<table class="col-12 table">
<thead>
<tr>
<th scope="col">Parameter</th>
</tr>
</thead>
<tbody>
<tr>
<td>Operates in SF6 and insulating liquids like transformer oil</td>
</tr>
<tr>
<td>Corona shield at top of Transformer termination provides shielding for terminal</td>
</tr>
<tr>
<td>Dry interfaces, no oil-filling</td>
</tr>
<tr>
<td>Pressure-tight resin housing</td>
</tr>
<tr>
<td>Prefabricated and factory-tested silicone-rubber stress cone</td>
</tr>
<tr>
<td>Torque-controlled or wedge-type multi-contact conductor bolt</td>
</tr>
<tr>
<td>Insulated cable gland for sectionalization</td>
</tr>
<tr>
<td>Type tested according to IEC 60840&nbsp;and&nbsp;IEC 62067 standards</td>
</tr>
</tbody>
</table>
<table class="col-12 table" data-table="" data-tablelook="1184">
<thead>
<tr>
<th colspan="4" data-celllook="0">
<p><strong> Design Data </strong> &nbsp;</p>
</th>
</tr>
</thead>
<tbody>
<tr>
<td data-celllook="0">
<p>Rated&nbsp;kV&nbsp;</p>
</td>
<td data-celllook="0">
<p>36/69 (72.5)&nbsp;</p>
</td>
<td data-celllook="0">
<p>76/132 (145)&nbsp;</p>
</td>
<td data-celllook="0">
<p>127/220 (245)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Diameter over insulation range&nbsp;</p>
</td>
<td data-celllook="0">
<p>38.40mm - 77.4 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>38.40 mm - 95.10 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>64.0 -123.1 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Diameter over sheath&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;120 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;140 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;160 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Cable screen type&nbsp;</p>
</td>
<td data-celllook="0">
<p>Corrugated Al. sheath, Copper wire, Copper tape, Lead sheath, etc.&nbsp;</p>
</td>
<td data-celllook="0">
<p>Corrugated Al. sheath, Copper wire, Copper tape, Lead sheath,&nbsp;etc.&nbsp;</p>
</td>
<td data-celllook="0">
<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Max. Cross section (Al/Cu)&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;1200 mm&sup2;&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;1600 mm&sup2;&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le;2500 mm&sup2;&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Conductor connection&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material of Housing&nbsp;</p>
</td>
<td data-celllook="0">
<p>Epoxy Resin&nbsp;</p>
</td>
<td data-celllook="0">
<p>Epoxy Resin&nbsp;</p>
</td>
<td data-celllook="0">
<p>Epoxy resin&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material of connection bolt&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum Alloy&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum Alloy&nbsp;</p>
</td>
<td data-celllook="0">
<p> Aluminum Alloy&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Method of Stress Control&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Type of Stress Cone&nbsp;</p>
</td>
<td data-celllook="0">
<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>
</td>
<td data-celllook="0">
<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>
</td>
<td data-celllook="0">
<p>Pre-moulded&nbsp;silicone rubber&nbsp;&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Corona Shield (only for Transformer Termination)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminium&nbsp;Alloy&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminium&nbsp;Alloy&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum Alloy&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Installation temperature [&deg;C]&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Operation temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>-55 &deg;C - +55 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p> -55 &deg;C - +55 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p> -55 &deg;C - +55 &deg;C&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Storage temperature [&deg;C]&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 to +40&nbsp;</p>
</td>
</tr>
</tbody>
</table>