INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(228, 'Cable to Earth Rod', 'asset-personnel-protection/earthing-and-lightning-protection-systems/exothermic-welding/cable-to-earth-rod', 'Copper Cable to Earth Rod Connection.Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. Exothermic connection provides permanent conductivity over the complete section due to molecular bonding between metal surfaces. Exothermic welded joint carries more tensile strength than mechanical connections.', 'vRalD5mjtKf3D83U5gdblXUDIgE16q.JPG', 2, NULL, NULL, '', NULL, 'cable-to-earth-rod-rcr1.pdf', 3, '', '<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCR1</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th scope=\"col\">C</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm</th>\r\n<th scope=\"col\">Inches</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>25</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-11125</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>35</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-11135</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>50</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-11150</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>70</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-11170</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>95</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-11195</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>120</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-111120</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>150</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-111150</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 045</td>\r\n<td>RCR1-R4-12716</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-12725</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-12730</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-12735</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-12750</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-1278SC</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-12770</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-12795</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-127150</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-127185</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-127240</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>300</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-127300</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>16*</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-14216</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-14225</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-14230</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-14235</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-14250</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-1428SC</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-14270</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-14295</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-142120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-142150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-142185</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-142240</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>300</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-142300</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-17216</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-17225</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-17230</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 065</td>\r\n<td>RCR1-R4-17235</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-17250</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-1728SC</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-17270</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-17295</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 090</td>\r\n<td>RCR1-R4-172120</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-172150</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 115</td>\r\n<td>RCR1-R4-172185</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-172240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>300</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-172300</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25425</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25430</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25435</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25450</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25470</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-25495</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCR1-R4-254120</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-254150</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-254185</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-254240</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>300</td>\r\n<td>RWP 200</td>\r\n<td>RCR1-R4-254300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCR2</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th scope=\"col\">C</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm</th>\r\n<th scope=\"col\">Inches &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>25</td>\r\n<td>RWP 90</td>\r\n<td>RCR2-R4-11125</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>30</td>\r\n<td>RWP 90</td>\r\n<td>RCR2-R4-11130</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>35</td>\r\n<td>RWP 90</td>\r\n<td>RCR2-R4-11135</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>50</td>\r\n<td>RWP 90</td>\r\n<td>RCR2-R4-11150</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>70</td>\r\n<td>RWP 90</td>\r\n<td>RCR2-R4-11170</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>95</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-11195</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-111120</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>150</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-111150</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12716</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12725</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12730</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12735</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12750</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 065</td>\r\n<td>RCR2-R4-1278SC</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-12770</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-12795</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-127150</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-127185</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-127240</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>300</td>\r\n<td>RWP 250</td>\r\n<td>RCR2-R4-127300</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 065</td>\r\n<td>RCR2-R4-14216</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-14225</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-14230</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-14235</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-14250</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-1428SC</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-14270</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-14295</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-142120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-142150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-142185</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCR2-R4-142240</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>300</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR2-R5-142300</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>16*</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-17216</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-17225</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-17230</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 090</td>\r\n<td>RCR2-R4-17235</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-17250</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-1728SC</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-17270</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 115</td>\r\n<td>RCR2-R4-17295</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-172120</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-172150</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-172185</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCR2-R4-172240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>300</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR2-R5-172300</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25425</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25430</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25435</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25450</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25470</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCR2-R4-25495</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-254120</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCR2-R4-254150</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP 250</td>\r\n<td>RCR2-R4-254185</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCR2-R4-254240</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>300</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR2-R4-254300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCR3</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th scope=\"col\">C</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm &Oslash;</th>\r\n<th scope=\"col\">Inches &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-12716</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-12725</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-12735</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-12750</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-1278SC</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-12770</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-127R95</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP150</td>\r\n<td>RCR3-R9-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>150</td>\r\n<td>-</td>\r\n<td>RCR3-R9-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>185</td>\r\n<td>-</td>\r\n<td>RCR3-R9-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>240</td>\r\n<td>-</td>\r\n<td>RCR3-R9-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>300</td>\r\n<td>-</td>\r\n<td>RCR3-R9-127120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>16*</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-14216</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-14225</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-14235</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-14250</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-1428SC</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-14270</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-142R95</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP150</td>\r\n<td>RCR3-R9-142120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP150</td>\r\n<td>RCR3-R9-142150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>185</td>\r\n<td>RWP200</td>\r\n<td>RCR3-R9-142185</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>240</td>\r\n<td>2 x RWP200</td>\r\n<td>RCR3-R10-142240</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>300</td>\r\n<td>-</td>\r\n<td>RCR3-R10-142300</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-17216</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-17225</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP090</td>\r\n<td>RCR3-R9-17235</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-17250</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCR3-R9-1728SC</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP150</td>\r\n<td>RCR3-R9-17270</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP150</td>\r\n<td>RCR3-R9-172R95</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP200</td>\r\n<td>RCR3-R9-172120</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>150</td>\r\n<td>RWP250</td>\r\n<td>RCR3-R9-172150</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>185</td>\r\n<td>2 x RWP200</td>\r\n<td>RCR3-R10-172185</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>240</td>\r\n<td>2 x RWP250</td>\r\n<td>RCR3-R10-172240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>300</td>\r\n<td>3 x RWP200</td>\r\n<td>RCR3-R10-172300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCR17</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th scope=\"col\">C</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm &Oslash;</th>\r\n<th scope=\"col\">Inches &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP090</td>\r\n<td>RCR17-R4-12716</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP090</td>\r\n<td>RCR17-R4-12725</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP090</td>\r\n<td>RCR17-R4-12730</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-12735</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-12750</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-1278SC</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-12770</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP200</td>\r\n<td>RCR17-R4-12795</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>120</td>\r\n<td>RWP250</td>\r\n<td>RCR17-R4-127120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP90</td>\r\n<td>RCR17-R4-14216</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP90</td>\r\n<td>RCR17-R4-14225</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-14230</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-14235</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-14250</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-1428SC</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP200</td>\r\n<td>RCR17-R4-14270</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP250</td>\r\n<td>RCR17-R4-14295</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>120</td>\r\n<td>2xRWP150</td>\r\n<td>RCR17-R5-142120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>150</td>\r\n<td>2xRWP200</td>\r\n<td>RCR17-R5-142150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>185</td>\r\n<td>2xRWP150</td>\r\n<td>RCR17-R5-142185</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>240</td>\r\n<td>3xRWP200</td>\r\n<td>RCR17-R5-142240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-17216</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-17225</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-17230</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-17235</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-17250</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-1728SC</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP200</td>\r\n<td>RCR17-R4-17270</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP250</td>\r\n<td>RCR17-R4-17295</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>120</td>\r\n<td>2xRWP150</td>\r\n<td>RCR17-R5-172120</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>150</td>\r\n<td>2xRWP200</td>\r\n<td>RCR17-R5-172150</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>185</td>\r\n<td>3xRWP150</td>\r\n<td>RCR17-R5-172185</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>240</td>\r\n<td>3xRWP200</td>\r\n<td>RCR17-R5-172240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>300</td>\r\n<td>2xRWP250</td>\r\n<td>RCR17-R4-172300</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP115</td>\r\n<td>RCR17-R4-25425</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-25430</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP150</td>\r\n<td>RCR17-R4-25435</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP200</td>\r\n<td>RCR17-R4-25450</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP250</td>\r\n<td>RCR17-R4-25470</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>95</td>\r\n<td>2xRWP150</td>\r\n<td>RCR17-R5-25495</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>120</td>\r\n<td>2xRWP200</td>\r\n<td>RCR17-R5-254120</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>150</td>\r\n<td>3xRWP150</td>\r\n<td>RCR17-R5-254150</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>185</td>\r\n<td>3xRWP200</td>\r\n<td>RCR17-R5-254185</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>240</td>\r\n<td>3xRWP250</td>\r\n<td>RCR17-R5-254240</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCR17</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th scope=\"col\">C</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm &Oslash;</th>\r\n<th scope=\"col\">Inches &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-11125</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>30</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-11130</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-11135</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-11150</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>70</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-11170</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>95</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-11195</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>120</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR24-R5-111120</td>\r\n</tr>\r\n<tr>\r\n<td>11.1</td>\r\n<td>-</td>\r\n<td>150</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCR24-R5-111150</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 090</td>\r\n<td>RCR24-R4-12716</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-12725</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-12730</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-12735</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-12750</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-1278SC</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-12770</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>95</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-12795</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>120</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR24-R4-127120</td>\r\n</tr>\r\n<tr>\r\n<td>12.7</td>\r\n<td>1&frasl;2&rdquo;</td>\r\n<td>150</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCR24-R4-127150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 090</td>\r\n<td>RCR24-R4-14216</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-14225</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-14230</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-14235</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-14250</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-1428SC</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-14270</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>95</td>\r\n<td>2 XRWP 150</td>\r\n<td>RCR24-R5-14295</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>120</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCR24-R5-142120</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>150</td>\r\n<td>3 X RWP 150</td>\r\n<td>RCR24-R5-142150</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>185</td>\r\n<td>2 X RWP 250</td>\r\n<td>RCR24-R5-142185</td>\r\n</tr>\r\n<tr>\r\n<td>14.2</td>\r\n<td>5&frasl;8&rdquo;</td>\r\n<td>240</td>\r\n<td>3 X RWP 250</td>\r\n<td>RCR24-R5-142240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>16</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-14216</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCR24-R4-17225</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-17230</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-17235</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-17250</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-1728SC</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>70</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-17270</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>95</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR24-R4-17295</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>120</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCR24-R5-172120</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>150</td>\r\n<td>3 X RWP 150</td>\r\n<td>RCR24-R5-172150</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>185</td>\r\n<td>3 X RWP 200</td>\r\n<td>RCR24-R5-172185</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>240</td>\r\n<td>3 X RWP 250</td>\r\n<td>RCR24-R5-172240</td>\r\n</tr>\r\n<tr>\r\n<td>17.2</td>\r\n<td>3&frasl;4&rdquo;</td>\r\n<td>300</td>\r\n<td>3 X RWP 250</td>\r\n<td>RCR24-R5-172300</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>25</td>\r\n<td>RWP 150</td>\r\n<td>RCR24-R4-25425</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>30</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-25430</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>35</td>\r\n<td>RWP 200</td>\r\n<td>RCR24-R4-25435</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>50</td>\r\n<td>RWP 250</td>\r\n<td>RCR24-R4-25450</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>70</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCR24-R5-25470</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>95</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCR24-R5-25495</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>120</td>\r\n<td>2 X RWP 250</td>\r\n<td>RCR24-R5-254120</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>150</td>\r\n<td>3 X RWP 200</td>\r\n<td>RCR24-R5-254150</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>185</td>\r\n<td>3 X RWP 250</td>\r\n<td>RCR24-R5-254185</td>\r\n</tr>\r\n<tr>\r\n<td>25.4</td>\r\n<td>1&rdquo;</td>\r\n<td>240</td>\r\n<td>4 X RWP 250</td>\r\n<td>RCR24-R5-254240</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" scope=\"col\">Joint Type</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>RCR1</td>\r\n</tr>\r\n<tr>\r\n<td>RCR2</td>\r\n</tr>\r\n<tr>\r\n<td>RCR3</td>\r\n</tr>\r\n<tr>\r\n<td>RCR17</td>\r\n</tr>\r\n<tr>\r\n<td>RCR24</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 5, 79, NULL, 0, NULL, 'Cable To Earth Rod Rcr1 | Exothermic Welding - Raychem RPG', 'Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. View more information online!', 1, 227, '2021-08-26 06:32:58', '2022-01-14 11:43:28'),
(233, 'Cable to Rebar', 'asset-personnel-protection/earthing-and-lightning-protection-systems/exothermic-welding/cable-to-rebar', 'Copper Cable to Reinforcing Bar Connection . Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. Exothermic connection provides permanent conductivity over the complete section due to molecular bonding between metal surfaces. Exothermic welded joint carries more tensile strength than mechanical connections.', 'QY3bQ2FTPNFZKI5evd11kqSdXrkC4S.JPG', 2, NULL, NULL, '', NULL, 'cable-to-rebar-rcre2.pdf', 3, '', '<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCRE2</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>12</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-2R240</td>\r\n</tr>\r\n<tr>\r\n<td>13</td>\r\n<td>25</td>\r\n<td>RWP 090</td>\r\n<td>RCRE2-R4-13R25</td>\r\n</tr>\r\n<tr>\r\n<td>13</td>\r\n<td>35</td>\r\n<td>RWP 090</td>\r\n<td>RCRE2-R4-13R35</td>\r\n</tr>\r\n<tr>\r\n<td>13</td>\r\n<td>50</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-13R50</td>\r\n</tr>\r\n<tr>\r\n<td>13</td>\r\n<td>70</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-13R70</td>\r\n</tr>\r\n<tr>\r\n<td>13</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-13R95</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>16</td>\r\n<td>RWP 090</td>\r\n<td>RCRE2-R4-16R16</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>25</td>\r\n<td>RWP 090</td>\r\n<td>RCRE2-R4-16R25</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>35</td>\r\n<td>RWP 090</td>\r\n<td>RCRE2-R4-16R35</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-16R8SC</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>50</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-16R50</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-16R10SC</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>70</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-16R70</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-16R95</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>120</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-16R120</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-16R150</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-16R185</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-16R240</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>300</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-16R300</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>16*</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-18R16</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-18R25</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-18R35</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-18R8SC</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>50</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-18R50</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-18R10SC</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>70</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-18R70</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-18R95</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>120</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-18R120</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-18R150</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>185</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-18R185</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>240</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-18R240</td>\r\n</tr>\r\n<tr>\r\n<td>18</td>\r\n<td>300</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-18R300</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>16*</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-20R16</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>25</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-20R25</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-20R35</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-20R8SC</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-20R50</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-20R10SC</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>70</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-20R70</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>95</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-20R95</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>120</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-20R120</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>150</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-20R150</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>185</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-20R185</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>240</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-20R240</td>\r\n</tr>\r\n<tr>\r\n<td>20</td>\r\n<td>300</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R5-20R300</td>\r\n</tr>\r\n<tr>\r\n<td>22</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-22R35</td>\r\n</tr>\r\n<tr>\r\n<td>22</td>\r\n<td>50</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-22R50</td>\r\n</tr>\r\n<tr>\r\n<td>22</td>\r\n<td>70</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-22R70</td>\r\n</tr>\r\n<tr>\r\n<td>22</td>\r\n<td>95</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-22R95</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>16</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-25R16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>25</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-25R25</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>35</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-25R35</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-25R8SC</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>50</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-25R50</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-25R10SC</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>70</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-25R70</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>95</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-25R95</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>120</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-25R120</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>150</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-25R150</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>185</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R5-25R185</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>240</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R5-25R240</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>300</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R5-25R300</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>16*</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-30R16</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>25</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-30R25</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>35</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R4-30R35</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>8 mm &Oslash;</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-30R8SC</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>50</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-30R50</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>10 mm &Oslash;</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-30R10SC</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>70</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R4-30R70</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>95</td>\r\n<td>2 X RWP 150</td>\r\n<td>RCRE2-R5-30R95</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>120</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R4530R120</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>150</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R5-30R150</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>185</td>\r\n<td>2 X RWP 250</td>\r\n<td>RCRE2-R5-30R185</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>240</td>\r\n<td>3 X RWP 200</td>\r\n<td>RCRE2-R5-30R240</td>\r\n</tr>\r\n<tr>\r\n<td>30</td>\r\n<td>300</td>\r\n<td>3 X RWP 200</td>\r\n<td>RCRE2-R5-30R300</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-32R35</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-32R50</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>70</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-32R70</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>95</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R5-32R95</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>120</td>\r\n<td>RWP 250</td>\r\n<td>RCRE2-R5-32R120</td>\r\n</tr>\r\n<tr>\r\n<td>32</td>\r\n<td>240</td>\r\n<td>2 X RWP 200</td>\r\n<td>RCRE2-R5-32R240</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>35</td>\r\n<td>RWP 115</td>\r\n<td>RCRE2-R4-36R35</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>50</td>\r\n<td>RWP 150</td>\r\n<td>RCRE2-R4-36R50</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>70</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R4-36R70</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>95</td>\r\n<td>RWP 200</td>\r\n<td>RCRE2-R5-36R95</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCRE3</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>10-40</td>\r\n<td>16</td>\r\n<td>RWP045</td>\r\n<td>RCRE3-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCRE3-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCRE3-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>10mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>70</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>95</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>120</td>\r\n<td>RWP090</td>\r\n<td>RCRE3-R4-120</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCRE6</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2; &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>10-40</td>\r\n<td>16*</td>\r\n<td>RWP045</td>\r\n<td>RCRE6-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCRE6-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCRE6-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP065</td>\r\n<td>RCRE6-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>50</td>\r\n<td>RWP065</td>\r\n<td>RCRE6-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>10mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCRE6-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>70</td>\r\n<td>RWP090</td>\r\n<td>RCRE6-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>95</td>\r\n<td>RWP090</td>\r\n<td>RCRE6-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>120</td>\r\n<td>RWP115</td>\r\n<td>RCRE6-R4-120</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCRE17</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">B</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2; &Oslash;</th>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>10-40</td>\r\n<td>16</td>\r\n<td>RWP045</td>\r\n<td>RCRE17-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCRE17-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCRE17-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>10mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>70</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>95</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>10-40</td>\r\n<td>120</td>\r\n<td>RWP090</td>\r\n<td>RCRE17-R4-120</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" scope=\"col\">Joint Type</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>RCRE2</td>\r\n</tr>\r\n<tr>\r\n<td>RCRE3</td>\r\n</tr>\r\n<tr>\r\n<td>RCRE6</td>\r\n</tr>\r\n<tr>\r\n<td>RCRE17</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 5, 80, NULL, 0, NULL, 'Cable To Rebar Rcre2 | Exothermic Welding - Raychem RPG', 'Copper Cable to Reinforcing Bar Connection Type RCRE2. Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. View more information online!', 1, 232, '2021-08-26 06:40:11', '2022-01-14 11:56:19');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(237, 'Cable to Steel Surface & Pipe', 'asset-personnel-protection/earthing-and-lightning-protection-systems/exothermic-welding/cable-to-steel-surface-pipe', 'Copper Cable to Steel Surface & Pipe Connection. Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. Exothermic connection provides permanent conductivity over the complete section due to molecular bonding between metal surfaces. Exothermic welded joint carries more tensile strength than mechanical connections.', 'W8kyfcyPKJqsjIkfEK3gGRtEzJfVVo.JPG', 2, NULL, NULL, '', NULL, 'cable-to-steel-surface-pipe-rcs1.pdf', 3, '', '<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS1</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>8mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS1-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCS1-R4-50-FU</td>\r\n</tr>\r\n<tr>\r\n<td>10mm&Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS1-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP090</td>\r\n<td>RCS1-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCS1-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP115</td>\r\n<td>RCS1-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP150</td>\r\n<td>RCS1-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP200</td>\r\n<td>RCS1-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP200</td>\r\n<td>RCS1-R4-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP250</td>\r\n<td>RCS1-R4-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS2</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS2-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCS2-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCS2-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP115</td>\r\n<td>RCS2-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP1t15</td>\r\n<td>RCS2-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP150</td>\r\n<td>RCS2-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP200</td>\r\n<td>RCS2-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP250</td>\r\n<td>RCS2-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP2 x 150</td>\r\n<td>RCS2-R5-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP2 x 200</td>\r\n<td>RCS2-R5-300</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"5\" width=\"414\">&nbsp;</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS3</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP045</td>\r\n<td>RCS3-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCS3-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCS3-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP065</td>\r\n<td>RCS3-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP065</td>\r\n<td>RCS3-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS3-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP090</td>\r\n<td>RCS3-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCS3-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP115</td>\r\n<td>RCS3-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP115</td>\r\n<td>RCS3-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP200</td>\r\n<td>RCS3-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP200</td>\r\n<td>RCS3-R4-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP250</td>\r\n<td>RCS3-R4-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS7</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP065</td>\r\n<td>RCS7-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP065</td>\r\n<td>RCS7-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP065</td>\r\n<td>RCS7-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS7-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCS7-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP150</td>\r\n<td>RCS7-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP150</td>\r\n<td>RCS7-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP200</td>\r\n<td>RCS7-R5-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP200</td>\r\n<td>RCS7-R5-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP250</td>\r\n<td>RCS7-R5-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP2 x 150</td>\r\n<td>RCS7-R9-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP2 x 150</td>\r\n<td>RCS7-R9-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP2 x 200</td>\r\n<td>RCS7-R10-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS8</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP045</td>\r\n<td>RCS8-R2-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCS8-R2-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCS8-R2-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP045</td>\r\n<td>RCS8-R2-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP045</td>\r\n<td>RCS8-R2-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP065</td>\r\n<td>RCS8-R2-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP065</td>\r\n<td>RCS8-R2-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP090</td>\r\n<td>RCS8-R2-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP115</td>\r\n<td>RCS8-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP150</td>\r\n<td>RCS8-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP200</td>\r\n<td>RCS8-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP200</td>\r\n<td>RCS8-R4-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP250</td>\r\n<td>RCS8-R4-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS9</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP045</td>\r\n<td>RCS9-R2-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCS9-R2-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCS9-R2-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP090</td>\r\n<td>RCS9-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP090</td>\r\n<td>RCS9-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCS9-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP115</td>\r\n<td>RCS9-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCS9-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP150</td>\r\n<td>RCS9-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP200</td>\r\n<td>RCS9-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP250</td>\r\n<td>RCS9-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP2 x 150</td>\r\n<td>RCS9-R5-240</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS25</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP45</td>\r\n<td>RCS25-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP45</td>\r\n<td>RCS25-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP45</td>\r\n<td>RCS25-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP65</td>\r\n<td>RCS25-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP65</td>\r\n<td>RCS25-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP90</td>\r\n<td>RCS25-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP90</td>\r\n<td>RCS25-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP115</td>\r\n<td>RCS25-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP115</td>\r\n<td>RCS25-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP150</td>\r\n<td>RCS25-R4-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP200</td>\r\n<td>RCS25-R4-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP200</td>\r\n<td>RCS25-R4-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP250</td>\r\n<td>RCS25-R4-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS27</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>16</td>\r\n<td>RWP45</td>\r\n<td>RCS27-R4-16</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>RWP045</td>\r\n<td>RCS27-R4-25</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>RWP045</td>\r\n<td>RCS27-R4-35</td>\r\n</tr>\r\n<tr>\r\n<td>8 mm &Oslash;</td>\r\n<td>RWP065</td>\r\n<td>RCS27-R4-8SC</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>RWP065</td>\r\n<td>RCS27-R4-50</td>\r\n</tr>\r\n<tr>\r\n<td>10 mm &Oslash;</td>\r\n<td>RWP115</td>\r\n<td>RCS27-R4-10SC</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>RWP115</td>\r\n<td>RCS27-R4-70</td>\r\n</tr>\r\n<tr>\r\n<td>95</td>\r\n<td>RWP150</td>\r\n<td>RCS27-R4-95</td>\r\n</tr>\r\n<tr>\r\n<td>120</td>\r\n<td>RWP150</td>\r\n<td>RCS27-R4-120</td>\r\n</tr>\r\n<tr>\r\n<td>150</td>\r\n<td>RWP200</td>\r\n<td>RCS27-R5-150</td>\r\n</tr>\r\n<tr>\r\n<td>185</td>\r\n<td>RWP250</td>\r\n<td>RCS27-R5-185</td>\r\n</tr>\r\n<tr>\r\n<td>240</td>\r\n<td>RWP2 x 150</td>\r\n<td>RCS27-R5-240</td>\r\n</tr>\r\n<tr>\r\n<td>300</td>\r\n<td>RWP2 x 200</td>\r\n<td>RCS27-R5-300</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS32</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n<th scope=\"col\">mm &Phi;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>2.5</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-2.5-A</td>\r\n</tr>\r\n<tr>\r\n<td>2.5</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-2.5-B</td>\r\n</tr>\r\n<tr>\r\n<td>4</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-4-A</td>\r\n</tr>\r\n<tr>\r\n<td>4</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-4-B</td>\r\n</tr>\r\n<tr>\r\n<td>6</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-6-A</td>\r\n</tr>\r\n<tr>\r\n<td>6</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS32-R4-6-B</td>\r\n</tr>\r\n<tr>\r\n<td>10</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 025</td>\r\n<td>RCS32-R4-10-A</td>\r\n</tr>\r\n<tr>\r\n<td>10</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 025</td>\r\n<td>RCS32-R4-10-B</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-16-A</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-16-B</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 025</td>\r\n<td>RCS32-R4-25-C</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>70-165</td>\r\n<td>RWP 025</td>\r\n<td>RCS32-R4-25-D</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>&gt; 165</td>\r\n<td>RWP 025</td>\r\n<td>RCS32-R4-25-E</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-35-C</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>70-165</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-35-D</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>165-250</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-35-F</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>&gt; 250</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-35-G</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-50-C</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>70-165</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-50-D</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>165-250</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-50-F</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>&gt; 250</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-50-G</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 045</td>\r\n<td>RCS32-R4-70-C</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>70-165</td>\r\n<td>RWP 065</td>\r\n<td>RCS32-R4-70-D</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>165-250</td>\r\n<td>RWP 065</td>\r\n<td>RCS32-R4-70-F</td>\r\n</tr>\r\n<tr>\r\n<td>70</td>\r\n<td>&gt; 250</td>\r\n<td>RWP 065</td>\r\n<td>RCS32-R4-70-G</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">RCS34</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">A</th>\r\n<th scope=\"col\">A</th>\r\n<th rowspan=\"2\" scope=\"col\">Weld &amp; Ignition Powder</th>\r\n<th rowspan=\"2\" scope=\"col\">Mould</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">mm&sup2;</th>\r\n<th scope=\"col\">mm &Phi;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>2.5</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-2.5-A</td>\r\n</tr>\r\n<tr>\r\n<td>2.5</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-2.5-B</td>\r\n</tr>\r\n<tr>\r\n<td>4</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-4-A</td>\r\n</tr>\r\n<tr>\r\n<td>4</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-4-B</td>\r\n</tr>\r\n<tr>\r\n<td>6</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-6-A</td>\r\n</tr>\r\n<tr>\r\n<td>6</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 015</td>\r\n<td>RCS34-R4-6-B</td>\r\n</tr>\r\n<tr>\r\n<td>10</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-10-A</td>\r\n</tr>\r\n<tr>\r\n<td>10</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-10-B</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>&lt; 125</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-16-A</td>\r\n</tr>\r\n<tr>\r\n<td>16</td>\r\n<td>&gt; 125</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-16-B</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-25-C</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>70-165</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-25-D</td>\r\n</tr>\r\n<tr>\r\n<td>25</td>\r\n<td>&gt; 165</td>\r\n<td>RWP 032</td>\r\n<td>RCS34-R4-25-E</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 045</td>\r\n<td>RCS34-R4-35-C</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>70-165</td>\r\n<td>RWP 045</td>\r\n<td>RCS34-R4-35-D</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>165-250</td>\r\n<td>RWP 045</td>\r\n<td>RCS34-R4-35-F</td>\r\n</tr>\r\n<tr>\r\n<td>35</td>\r\n<td>&gt; 250</td>\r\n<td>RWP 045</td>\r\n<td>RCS34-R4-35-G</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>&lt; 70</td>\r\n<td>RWP 065</td>\r\n<td>RCS34-R4-50-C</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>70-165</td>\r\n<td>RWP 065</td>\r\n<td>RCS34-R4-50-D</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>165-250</td>\r\n<td>RWP 065</td>\r\n<td>RCS34-R4-50-F</td>\r\n</tr>\r\n<tr>\r\n<td>50</td>\r\n<td>&gt; 250</td>\r\n<td>RWP 065</td>\r\n<td>RCS34-R4-50-G</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 120px;\" width=\"879\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 869.389px;\" colspan=\"2\" scope=\"col\">&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; Joint Type</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 389.972px;\">RCS1</td>\r\n<td style=\"width: 473.622px;\">RCS9</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 389.972px;\">RCS2</td>\r\n<td style=\"width: 473.622px;\">RCS25</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 389.972px;\">RCS3</td>\r\n<td style=\"width: 473.622px;\">RCS27</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 389.972px;\">RCS7</td>\r\n<td style=\"width: 473.622px;\">RCS32</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 389.972px;\">RCS8</td>\r\n<td style=\"width: 473.622px;\">RCS34</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 5, 81, NULL, 0, NULL, 'Cable To Steel Surface Pipe Rcs1 | Exothermic Welding - Raychem RPG', 'Copper Cable to Steel Surface & Pipe Connection Type RCS1. Exothermic welding process is a simple, efficient method of permanently bonding copper to copper or copper to steel. View more information online!', 1, 236, '2021-08-26 06:44:23', '2022-01-17 08:40:40'),
(247, 'Exothermic Welding Powder', 'asset-personnel-protection/earthing-and-lightning-protection-systems/exothermic-welding/exothermic-welding-powder/exothermic-welding-powder', 'Produce high quality electrical connections between different metals (copper to copper / copper to steel)', 'bDQ3uMyfeZhpuzJarefdgUjPjYYZwF.jpg', 2, NULL, NULL, '', NULL, 'exothermic-welding-powder.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong> Part No </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> Raychem RPG Item Description </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;045 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 45grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;065 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 65grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;090 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 90grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;115 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder&nbsp;115grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;150 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 150grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;200 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 200grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p><strong> RWP&nbsp;250 </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Exo-thermic&nbsp;Welding Powder 250grams.&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 112px;\" width=\"944\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 934.389px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 934.389px;\"><span class=\"TextRun  BCX0 SCXW160669293\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun  BCX0 SCXW160669293\">Weld Powder&nbsp;</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">produces&nbsp;</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">high quality electrical connection between different metals (Copper to Copper / Copper to Steel)</span></span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 934.389px;\"><span class=\"TextRun Highlight  BCX0 SCXW160669293\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"none\"><span class=\"NormalTextRun  BCX0 SCXW160669293\">It is a reaction of copper oxide and&nbsp;</span><span class=\"NormalTextRun SpellingErrorV2  BCX0 SCXW160669293 DefaultHighlightTransition\">aluminium</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">&nbsp;inside a&nbsp;</span><span class=\"NormalTextRun SpellingErrorV2  BCX0 SCXW160669293\">mould</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">&nbsp;that forms a permanent joint by igniting weld powder with flint gun</span></span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 934.389px;\"><span class=\"TextRun Highlight  BCX0 SCXW160669293\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"none\"><span class=\"NormalTextRun  BCX0 SCXW160669293\">Ignition Powder and steel disc are provided as&nbsp;</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">p</span><span class=\"NormalTextRun  BCX0 SCXW160669293\">art of Weld Powder</span></span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', 5, 82, NULL, 0, NULL, 'Exothermic Welding Powder | Exothermic Welding - Raychem RPG', 'Produce high quality electrical connections between different metals (copper to copper / copper to steel)', 1, 246, '2021-08-26 07:03:36', '2022-01-05 05:17:00'),
(249, 'Welding Accessories', 'asset-personnel-protection/earthing-and-lightning-protection-systems/exothermic-welding/welding-accessories', 'Used for igniting and initiating exothermic reaction. Welding accessories like Flint Gun, Handle Clamp, Mould Cleaning Brush, Weld Cavity Cleaning Brush, File Card Brush, Slag remover scrapper and Hand Gloves are used to securely make a joint.', 'QKE8fxG2PTWih7oK2IxwOsJJYuPloA.jpg', 2, NULL, NULL, '', NULL, 'flint-gun.pdf', 3, '', '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th width=\"112\">\r\n<p><strong> Part No </strong></p>\r\n</th>\r\n<th width=\"227\">\r\n<p><strong> Raychem RPG Item Description </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> RFG-01 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Flint Gun</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> HCRRL-4 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Handle Clamp (Small)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> HCRRL-5 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Handle Clamp (Big)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> RMCB-01 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Mould Cleaning Brush</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> R </strong> <strong> WCCB-01 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Weld Cavity cleaning brush</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> RFCB-01 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>File Card Brush</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> RSRS-01+D13 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Slag remover scrapper</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"112\">\r\n<p><strong> RHG-01 </strong></p>\r\n</td>\r\n<td width=\"227\">\r\n<p>Hand Gloves</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 219px; width: 962px;\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 203.48px;\" scope=\"col\">Parameter</th>\r\n<th style=\"width: 743.111px;\" scope=\"col\">Value</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Flint Gun</td>\r\n<td style=\"width: 743.111px;\">It is used to ignite &amp; initiate in exothermic Reaction</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Handle Clamp</td>\r\n<td style=\"width: 743.111px;\">To clamp the two/three partmould together (or) clamping the mould to the surface to which a connection is to be made</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Mould Cleaning Brush</td>\r\n<td style=\"width: 743.111px;\">Used for cleaning the scrap on mould after weld joints are completed</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Weld Cavity Cleaning Brush</td>\r\n<td style=\"width: 743.111px;\">Used for cleaning the scrap on mould Cavity after weld joints are completed</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">File Card Brush</td>\r\n<td style=\"width: 743.111px;\">It is used for Cleaning surface of tape</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Slag Remover Scrapper</td>\r\n<td style=\"width: 743.111px;\">It is used for removing Slag leftovers after weld joints are completed</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 203.48px;\">Hand Gloves</td>\r\n<td style=\"width: 743.111px;\">It is used to provide safety high temperature resistant gloves while working on the exothermic reaction.</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', 5, 83, NULL, 0, NULL, 'Handle Clamp | Exothermic Accessories - Raychem RPG', 'Clamping two/three part moulds together or clamping moulds to surface for making connection.  View more information online!', 1, 248, '2021-08-26 07:05:45', '2022-01-05 05:29:45'),
(255, 'Heat Shrink Insulation Tubing', 'asset-personnel-protection/insulation-enhancement-system/heat-shrink-insulation-tubing', 'Heat-shrinkable busbar insulation tubing. Busbar heat-shrinkable tubing are suitable for use on long runs of rectangular or round busbars. The tubing shrinks down to 40% of their original diameter and, due to excellent flexibility, conform tightly to a wide range of sizes. BBIT/BPTM tubing can be slid easily into place, even around several bends and awkward shapes. The wall thickness is controlled by heat-shrink process. Available for over fifteen sizes of busbars from 5 mm to over 250 mm, BPTM/RBPM is suitable for applications up to 24 kV. BBIT is suitable for applications up to and over 36 kV.', 'o2H3exmKtPl1NgfOrgrY4t0uwrsCkk.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-heat-shrink-insulation-tubing.pdf', 3, '', '<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">BBIT</h3>\r\n</header>\r\n<p>BBIT should normally be used on the following busbar sizes</p>\r\n<p>&nbsp;</p>\r\n<p><span data-ccp-props=\"{&quot;335559738&quot;:2}\"><img src=\"/assets/images/editor/1_hsit.png\" width=\"304\" height=\"131\" />&nbsp; &nbsp; &nbsp;&nbsp;<img src=\"/assets/images/editor/2_hsit1.png\" width=\"335\" height=\"90\" /></span></p>\r\n<p>&nbsp;</p>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">Product selection</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th rowspan=\"2\" scope=\"col\">Product size</th>\r\n<th colspan=\"2\" scope=\"col\">Rectangular bars L + T (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">Round bars D (mm)</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">min.</th>\r\n<th scope=\"col\">max.</th>\r\n<th scope=\"col\">min.</th>\r\n<th scope=\"col\">max.</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>BBIT 25/10</td>\r\n<td>17</td>\r\n<td>28</td>\r\n<td>11</td>\r\n<td>20</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT 40/16</td>\r\n<td>28</td>\r\n<td>45</td>\r\n<td>18</td>\r\n<td>32</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT 65/25</td>\r\n<td>44</td>\r\n<td>69</td>\r\n<td>28</td>\r\n<td>47</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT 100/40</td>\r\n<td>6</td>\r\n<td>102</td>\r\n<td>44</td>\r\n<td>72</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT 150/60</td>\r\n<td>102</td>\r\n<td>148</td>\r\n<td>65</td>\r\n<td>105</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT 175/80</td>\r\n<td>133</td>\r\n<td>196</td>\r\n<td>85</td>\r\n<td>125</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">Ordering information</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th rowspan=\"2\" scope=\"col\">Ordering description</th>\r\n<th colspan=\"2\" scope=\"col\">Inside diameter (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">Wall thickness (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">UOM: roll</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">H<br />min.</th>\r\n<th scope=\"col\">h<br />max.</th>\r\n<th scope=\"col\">W<br />nom.</th>\r\n<th scope=\"col\">w<br />min.</th>\r\n<th>length<br />(m)</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>BBIT-25/10-A/U-4 25</td>\r\n<td>10</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>25</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT-40/16-A/U-4 40</td>\r\n<td>16</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>20</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT-65/25-A/U-4 65</td>\r\n<td>25</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>15</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT-100/40-A/U-4</td>\r\n<td>100</td>\r\n<td>40</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>15</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT-150/60-A/U-4</td>\r\n<td>150</td>\r\n<td>60</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>15</td>\r\n</tr>\r\n<tr>\r\n<td>BBIT-175/80-A/U-4</td>\r\n<td>175</td>\r\n<td>80</td>\r\n<td>1.6</td>\r\n<td>3.6</td>\r\n<td>10</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\"></header><header class=\"col-12 p-0 tables__title mt-2 sticky\"></header><header class=\"col-12 p-0 tables__title mt-2 sticky\"></header><header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">BPTM / RBPM</h3>\r\n</header>\r\n<p><span style=\"font-size: 12pt;\"><strong><span class=\"EOP SCXW141800148 BCX0\" data-ccp-props=\"{&quot;201341983&quot;:1,&quot;335559685&quot;:110,&quot;335559738&quot;:33,&quot;335559740&quot;:189}\"><span data-ccp-props=\"{&quot;201341983&quot;:1,&quot;335559685&quot;:110,&quot;335559740&quot;:182}\">&nbsp;</span></span></strong></span><span style=\"font-size: 12pt;\">BPTM should normally be used on the following busbar sizes</span></p>\r\n<p>&nbsp;<img src=\"/assets/images/editor/1_hsit1.png\" width=\"271\" height=\"117\" />&nbsp; &nbsp; &nbsp;<img src=\"/assets/images/editor/2_hsit2.png\" width=\"284\" height=\"76\" /></p>\r\n<p>&nbsp;</p>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">Product selection</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th rowspan=\"2\" scope=\"col\">Product size</th>\r\n<th colspan=\"2\" scope=\"col\">Rectangular bars L + T (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">Round bars D (mm)</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">min.</th>\r\n<th scope=\"col\">max.</th>\r\n<th scope=\"col\">min.</th>\r\n<th scope=\"col\">max.</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>BPTM 15/6</td>\r\n<td>12</td>\r\n<td>18</td>\r\n<td>6.5</td>\r\n<td>12</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 30/12</td>\r\n<td>22</td>\r\n<td>38</td>\r\n<td>13.5</td>\r\n<td>25</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 50/20</td>\r\n<td>36</td>\r\n<td>65</td>\r\n<td>22</td>\r\n<td>43</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 75/30</td>\r\n<td>55</td>\r\n<td>95</td>\r\n<td>33</td>\r\n<td>63</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 100/40</td>\r\n<td>70</td>\r\n<td>130</td>\r\n<td>44</td>\r\n<td>86</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 120/50</td>\r\n<td>90</td>\r\n<td>165</td>\r\n<td>55</td>\r\n<td>105</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 175/70</td>\r\n<td>125</td>\r\n<td>235</td>\r\n<td>80</td>\r\n<td>150</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 205/110</td>\r\n<td>200</td>\r\n<td>276</td>\r\n<td>127</td>\r\n<td>190</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM 235/130</td>\r\n<td>235</td>\r\n<td>315</td>\r\n<td>150</td>\r\n<td>220</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-2 sticky\">\r\n<h3 class=\"secondary-heading\">Ordering information</h3>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th rowspan=\"2\" scope=\"col\">Ordering description</th>\r\n<th colspan=\"2\" scope=\"col\">Inside diameter (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">Wall thickness (mm)</th>\r\n<th colspan=\"2\" scope=\"col\">UOM: roll</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">H<br />min.</th>\r\n<th scope=\"col\">h<br />max.</th>\r\n<th scope=\"col\">W<br />nom.</th>\r\n<th scope=\"col\">w<br />min.</th>\r\n<th>length<br />(m)</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>BPTM-15/6-A/U-4</td>\r\n<td>15</td>\r\n<td>6</td>\r\n<td>1.1</td>\r\n<td>1.90</td>\r\n<td>30</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-30/12-A/U-4</td>\r\n<td>30</td>\r\n<td>12</td>\r\n<td>1.1</td>\r\n<td>2.20</td>\r\n<td>30</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-50/20-A/U-4</td>\r\n<td>50</td>\r\n<td>20</td>\r\n<td>1.1</td>\r\n<td>2.35</td>\r\n<td>30</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-75/30-A/U-4</td>\r\n<td>75</td>\r\n<td>30</td>\r\n<td>1.1</td>\r\n<td>2.35</td>\r\n<td>20</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-100/40-A/U-4</td>\r\n<td>100</td>\r\n<td>40</td>\r\n<td>1.1</td>\r\n<td>2.35</td>\r\n<td>25</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-120/50-A/U-4</td>\r\n<td>120</td>\r\n<td>50</td>\r\n<td>1.3</td>\r\n<td>2.80</td>\r\n<td>25</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-175/70-A/U-4</td>\r\n<td>175</td>\r\n<td>70</td>\r\n<td>1.3</td>\r\n<td>2.80</td>\r\n<td>15</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-205/110-A/U-4</td>\r\n<td>205</td>\r\n<td>110</td>\r\n<td>1.3</td>\r\n<td>2.80</td>\r\n<td>10</td>\r\n</tr>\r\n<tr>\r\n<td>BPTM-235/130-A/U-4</td>\r\n<td>235</td>\r\n<td>130</td>\r\n<td>1.5</td>\r\n<td>3.10</td>\r\n<td>20</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"257\">\r\n<p><strong> Key product specifications </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"257\">\r\n<p><strong> Test method </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"257\">\r\n<p><strong> Requirement </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Thermal endurance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC 216&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>105 &deg;C min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Accelerated ageing&nbsp;</p>\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Arial\" data-listid=\"1\" data-aria-posinset=\"0\" data-aria-level=\"1\">Tensile&nbsp;strength&nbsp;</li>\r\n<li data-leveltext=\"-\" data-font=\"Arial\" data-listid=\"1\" data-aria-posinset=\"0\" data-aria-level=\"1\">Ultimate&nbsp;elongation&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ISO 188, ASTM D2671&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>168&nbsp;hrs&nbsp;@ 120 &deg;C&nbsp;</p>\r\n<p>10 MPa min.&nbsp;</p>\r\n<p>300% min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Comparative tracking index&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC&nbsp;112,&nbsp;VDE&nbsp;0303/1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>KA 3c&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Dielectric strength&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D149, IEC 243&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>180&nbsp;kV/cm&nbsp;min.&nbsp;@&nbsp;2&nbsp;mm&nbsp;</p>\r\n<p>150 kV/cm min. @ 2.5 mm&nbsp;</p>\r\n<p>120 kV/cm min. @ 3 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Smoke index&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>NES 711&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>Less than 120&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Acid gas generation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>Raychem PPS 3010 4.23&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>Less than 1% by weight&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Low temperature flexibility&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D2671 Procedure C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>No cracking after 4&nbsp;hrs&nbsp;@ -40 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Flammability&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ANSI C37.20/IEEE-27&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>No flame conveyance, 60 sec. max.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Tracking and Erosion Resistance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D2303&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>No tracking, erosion to top surface or flame failure after&nbsp;1&nbsp;hr. at 2.5kV, after&nbsp;1&nbsp;hr. at 2.75kV,&nbsp;1%&nbsp;max.&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 61, NULL, 0, NULL, 'Heat Shrink Insulation Tubing | Insulation Enhancement System - Raychem RPG', 'Heat-shrinkable busbar insulation tubing. Busbar heat-shrinkable tubing are suitable for use on long runs of rectangular or round busbars.', 1, 254, '2021-08-27 11:45:43', '2022-01-17 06:51:09'),
(256, 'Insulating Tapes', 'asset-personnel-protection/insulation-enhancement-system/insulating-tapes', 'Medium Voltage Heat Shrink/ Fusion tapes.  HVBT heat-shrinkable tape is ideal for use on complex shapes and where busbars cannot be disconnected. HVBT tape shrinks 30% longitudinally and an adhesive layer flows and seals the layers of tape during installation.  As with the other components in the system, the adhesive does not bond to metalwork, allowing easy removal for inspection and maintenance. Available in four widths from 25 mm to 100 mm. A spiral formed tape is also available for ease of use on overhead conductors. MVFT is a self-amalgamating tape providing insulation enhancement and protection against accidentally induced discharge. Quick and easy to install, upon application the tape amalgamates the overlapped layers together, producing a complete seal.', 'fbNybeMgiriGZ9Fpn7RczaXzzSiG5T.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-insulating-tapes.pdf', 3, '', '<div class=\"table-responsive\">\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\">HVBT</th>\r\n</tr>\r\n<tr>\r\n<th>Rated Voltage (kV)</th>\r\n<th>Phase- Phase (mm)</th>\r\n<th>Phase- Ground (mm)</th>\r\n<th>IEC 71-2 Air Clearance (mm)</th>\r\n</tr>\r\n<tr>\r\n<th colspan=\"4\">Round Busbars</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>12</td>\r\n<td>55</td>\r\n<td>65</td>\r\n<td>120</td>\r\n</tr>\r\n<tr>\r\n<td>17.5</td>\r\n<td>70</td>\r\n<td>85</td>\r\n<td>160</td>\r\n</tr>\r\n<tr>\r\n<td>24</td>\r\n<td>95</td>\r\n<td>125</td>\r\n<td>220</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>150</td>\r\n<td>205</td>\r\n<td>320</td>\r\n</tr>\r\n</tbody>\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\">Rectangular Busbars</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>12</td>\r\n<td>65</td>\r\n<td>75</td>\r\n<td>120</td>\r\n</tr>\r\n<tr>\r\n<td>17.5</td>\r\n<td>85</td>\r\n<td>104</td>\r\n<td>160</td>\r\n</tr>\r\n<tr>\r\n<td>24</td>\r\n<td>115</td>\r\n<td>150</td>\r\n<td>220</td>\r\n</tr>\r\n<tr>\r\n<td>36</td>\r\n<td>200</td>\r\n<td>285</td>\r\n<td>320</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n</div>\r\n<div class=\"table-responsive\">\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"5\">MVFT Selection Information:</th>\r\n</tr>\r\n<tr>\r\n<th>Catalog Number</th>\r\n<th>Color</th>\r\n<th>Width UOM: Inches (mm)</th>\r\n<th>Supplied Length UOM: Yards (M)</th>\r\n<th>Std. Pack</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>MVFT-G-2-12(B4)</td>\r\n<td>Gray</td>\r\n<td>2 (50)</td>\r\n<td>12 (11)</td>\r\n<td>4 Rolls</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n</div>', NULL, '', NULL, '', NULL, '<div class=\"table-responsive\">\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"8\">HVBT</th>\r\n</tr>\r\n<tr>\r\n<th>Product Selection Rectangular Busbars Width</th>\r\n<th>IAC Application Recommended Product</th>\r\n<th>IEEE Applic ations</th>\r\n<th>HVBT Length Needed / meter of Busbar</th>\r\n<th>IEC Round Busbars Diameter</th>\r\n<th>Application Recom mended Product</th>\r\n<th>IEEE Applications</th>\r\n<th>HVBT Length Needed/ meter of Busbar</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>25 mm</td>\r\n<td>HVBT-12-A</td>\r\n<td>HVBT-1-R</td>\r\n<td>10.0</td>\r\n<td>12 mm</td>\r\n<td>HVBT-12-A</td>\r\n<td>HVBT-1-R</td>\r\n<td>5.0</td>\r\n</tr>\r\n<tr>\r\n<td>50 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>7.6</td>\r\n<td>25 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>5.0</td>\r\n</tr>\r\n<tr>\r\n<td>75 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>11.4</td>\r\n<td>50 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>10.0</td>\r\n</tr>\r\n<tr>\r\n<td>100 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>15.6</td>\r\n<td>75 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>16.7</td>\r\n</tr>\r\n<tr>\r\n<td>150 mm</td>\r\n<td>HVBT-14-A</td>\r\n<td>HVBT-2-R</td>\r\n<td>25.0</td>\r\n<td>100 mm</td>\r\n<td>HVBT-16-A</td>\r\n<td>HVBT-4-R</td>\r\n<td>10.0</td>\r\n</tr>\r\n<tr>\r\n<td>200 mm</td>\r\n<td>HVBT-16-A</td>\r\n<td>HVBT-4-R</td>\r\n<td>15.6</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n</div>\r\n<div class=\"table-responsive\">\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\">MVFT</th>\r\n</tr>\r\n<tr>\r\n<th>Product Testing Result</th>\r\n<th>Result</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>AC Dry Withstand/1 min.</td>\r\n<td>15 kV (One Insulation Layer) 35 kV (Two Insulation Layers)</td>\r\n</tr>\r\n<tr>\r\n<td>Loading Cycling 30 days @ 130˚C</td>\r\n<td>No Deformation or Splitting Low</td>\r\n</tr>\r\n<tr>\r\n<td>Temperature Install @ 0˚C</td>\r\n<td>Installable Without Difficulty</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n</div>\r\n<div class=\"table-responsive\">\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th>Test</th>\r\n<th>Specification</th>\r\n<th>Results</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Accelerated Aging 168 hours 150˚C Tensile Strength Ultimate Elongation</td>\r\n<td>ASTM D2671</td>\r\n<td>&gt; 1,000 psi &gt; 450%</td>\r\n</tr>\r\n<tr>\r\n<td>Low Temperature Flexibility 4 hours -40˚</td>\r\n<td>ASTM D2671</td>\r\n<td>No cracking</td>\r\n</tr>\r\n<tr>\r\n<td>Dielectric Strength 3.4 mm thickness</td>\r\n<td>ASTM D149</td>\r\n<td>&gt; 300V/mil</td>\r\n</tr>\r\n<tr>\r\n<td>Tracking and Erosion Resistance</td>\r\n<td>ASTM D2303</td>\r\n<td>No Tracking, erosion to top surface or flame failure after: 1 hour at 2.5 kV 1 hour at 2.75 kV 1 hour at 3.0 kV 20 min. at 3.25 kV</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n</div>', NULL, '', NULL, 61, NULL, 0, NULL, 'Insulating Tapes | Insulation Enhancement System - Raychem RPG', 'Medium Voltage Heat Shrink/ Fusion tapes. HVBT heat-shrinkable tape is ideal for use on complex shapes and where busbars cannot be disconnected.', 1, 255, '2021-08-27 11:47:53', '2022-01-20 07:42:09');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(257, 'Insulating Sheets', 'asset-personnel-protection/insulation-enhancement-system/insulating-sheets', 'Medium Voltage Insulating barriers.  BCIC preformed covers provide connections for insulators, bushings and busbars. Customized covers can be made simply and economically by vacuum forming non-shrinkable sheet material.  Installation is very simple often with no need to disconnect busbars. BCIC covers are held in place with UV-stabilized plastic nuts and bolts, rivets or tie-wraps, and can be easily removed for maintenance, or else sealed with Raychem sealing mastic. Suitable for applications up 36 kV.  Rigid Red Barrier Board (RRBB) is a non-structural, interphase barrier for switchgear applications. The RRBB board has excellent track resistance, especially following a power-arc. It can be easily fabricated into a shape; produces less nuisance dust and less tooling wear than other boards.', '4Qe6XzbTnHTdxup9f3YRAk7LMH6mu0.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-insulating-sheets.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"256\">\r\n<p><strong> RRBB </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"256\">\r\n<p><strong>Key Material Properties </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"256\">\r\n<p><strong> Test Method </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"256\">\r\n<p><strong> Requirement </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"257\">\r\n<p>Physical&nbsp;</p>\r\n&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Tensile Strength&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D638&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>17&nbsp;Mpa&nbsp;minimum (2450 psi min)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Ultimate Elongation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D638&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>25% minimum&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"257\">\r\n<p>Electrical&nbsp;</p>\r\n&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td rowspan=\"3\" data-celllook=\"257\">\r\n<p>Tracking and Erosion Resistance&nbsp;</p>\r\n&nbsp;&nbsp;\r\n<p>&nbsp;</p>\r\n<p>&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D2303&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>No tracking, or erosion to top&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"1\">\r\n<p>Step Voltage Method&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"1\">\r\n<p>surface or flame failure after:&nbsp;</p>\r\n<p>1&nbsp;hr&nbsp;@ 2.5 kV&nbsp;</p>\r\n<p>1&nbsp;hr&nbsp;@&nbsp;2.75 kV&nbsp;</p>\r\n<p>1&nbsp;hr&nbsp;@&nbsp;3.00 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"256\">\r\n<p>(initiate @ 2.5 kV)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"256\">\r\n<p>20 min @ 3.25 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"256\">\r\n<p><strong>*For BCIC, please&nbsp;contact Raychem&nbsp;RPG&nbsp;Representative</strong></p>\r\n<p>&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"width: 813px; height: 283px;\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 803px;\" colspan=\"4\" data-celllook=\"256\">\r\n<p><strong> RRBB </strong></p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th style=\"width: 449.562px;\" data-celllook=\"256\">\r\n<p><strong> Product Selection Information: </strong></p>\r\n</th>\r\n<th style=\"width: 347.438px;\" colspan=\"3\" data-celllook=\"256\">\r\n<p><strong> dimensions in&nbsp;mm </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 449.562px;\" data-celllook=\"256\">\r\n<p><strong> Catalog Number </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 80.0312px;\" data-celllook=\"256\">\r\n<p><strong> Width </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 108.484px;\" data-celllook=\"256\">\r\n<p><strong> Length </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 146.922px;\" data-celllook=\"256\">\r\n<p><strong> Thickness </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 449.562px;\" data-celllook=\"257\">\r\n<p>RRBB-2050/775-5-B&nbsp;</p>\r\n</td>\r\n<td style=\"width: 80.0312px;\" data-celllook=\"257\">\r\n<p>775&nbsp;</p>\r\n</td>\r\n<td style=\"width: 108.484px;\" data-celllook=\"257\">\r\n<p>2050&nbsp;</p>\r\n</td>\r\n<td style=\"width: 146.922px;\" data-celllook=\"257\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 803px;\" colspan=\"4\" data-celllook=\"257\">\r\n<p><strong>*For BCIC, please&nbsp;contact Raychem&nbsp;RPG&nbsp;Representative</strong></p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 61, NULL, 0, NULL, 'Insulating Tapes | Insulation Enhancement System - Raychem RPG', 'Medium Voltage Insulating barriers. BCIC preformed covers provide connections for insulators, bushings and busbars. Customized covers can be made simply and economically.', 1, 256, '2021-08-27 11:48:29', '2021-12-28 06:42:34'),
(258, 'Creepage Extender', 'asset-personnel-protection/insulation-enhancement-system/creepage-extender', 'High Voltage Creepage Extenders.  HVCE creepage extenders represent a long-term solution to pollution flashovers by making a permanent addition to the creepage distance. This increases flashover voltage, reduces leakage currents and surface electrical stresses. They are available to fit insulators and bushings up to 500 kV, with shed diameter 80 mm to over 390 mm.  Wrap-around HVCE-WA creepage extenders are cold applied and custom-made from semi-rigid polymer and bonded in place with a pressure sensitive track-resistant mastic. These are available to fit insulators and bushings up to 500 kV.', 'CFPduupWRr3ssWQX8PjjrSM1pWyg3m.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-creepage-extender.pdf', 3, '', '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\">Dimensions in mm (inches)</th>\r\n<th colspan=\"3\">Application range</th>\r\n</tr>\r\n<tr>\r\n<th>Size&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;</th>\r\n<th>Min. internal dia. of the extender (as supplied)</th>\r\n<th>Max. shed dia. of insulator (d)</th>\r\n<th>Min. shed dia. of insulator (d)</th>\r\n<th>Nominal creepage extension per extender</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>HVCE-100/80-01</td>\r\n<td>115 (4.5)</td>\r\n<td>100 (4.0)</td>\r\n<td>80 (3.2)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-120/100-01</td>\r\n<td>135 (5.3)</td>\r\n<td>120 (4.7)</td>\r\n<td>100 (4.0)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-140/120-01</td>\r\n<td>155 (6.1)</td>\r\n<td>140 (5.5)</td>\r\n<td>120 (4.7)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-160/140-01</td>\r\n<td>180 (7.1)</td>\r\n<td>160 (6.3)</td>\r\n<td>140 (5.5)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-183/161-01</td>\r\n<td>205 (8.1)</td>\r\n<td>183 (7.2)</td>\r\n<td>161 (6.3)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-205/184-01</td>\r\n<td>230 (9.0)</td>\r\n<td>205 (8.1)</td>\r\n<td>184 (7.2)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-226/206-11</td>\r\n<td>241 (9.5)</td>\r\n<td>226 (8.9)</td>\r\n<td>206 (8.1)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-247/227-11</td>\r\n<td>262 (10.3)</td>\r\n<td>247 (9.7)</td>\r\n<td>227 (8.9)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-268/248-11</td>\r\n<td>283 (11.1)</td>\r\n<td>268 (10.5)</td>\r\n<td>248 (9.8)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-289/269-11</td>\r\n<td>304 (12.0)</td>\r\n<td>289 (11.4)</td>\r\n<td>269 (10.6)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-310/290-11</td>\r\n<td>325 (12.8)</td>\r\n<td>310 (12.2)</td>\r\n<td>290 (11.4)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-331/311-11</td>\r\n<td>346 (13.6)</td>\r\n<td>331 (13.0)</td>\r\n<td>311 (12.2)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-352/332-11</td>\r\n<td>367 (14.4)</td>\r\n<td>352 (13.8)</td>\r\n<td>332 (13.1)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-373/353-11</td>\r\n<td>388 (15.3)</td>\r\n<td>373 (14.7)</td>\r\n<td>353 (13.9)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n<tr>\r\n<td>HVCE-394/374-11</td>\r\n<td>409 (16.1)</td>\r\n<td>394 (15.5)</td>\r\n<td>374 (14.7)</td>\r\n<td>100 (4.0)</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"256\">\r\n<p>General properties&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"256\">\r\n<p>Test method&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"256\">\r\n<p>Typical data*&nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Density&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ISO/R1183 Method A&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>1.2&nbsp;g/cm3&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Tensile strength&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ISO 37&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>10&nbsp;N/mm2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Ultimate elongation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ISO 37&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>400 %&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Low temperature flexibility&nbsp;</p>\r\n<p>4 hours at &ndash;40&deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>ASTM D2671 Procedure C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>no cracking&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Thermal endurance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC 216&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>120&deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Electric strength&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC 243&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>140 kV/cm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Dielectric constant&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC 250&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"257\">\r\n<p>Volume resistivity&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>IEC 93&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"257\">\r\n<p>1&nbsp;x&nbsp;1014 W&nbsp;cm&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>Additional&nbsp;properties Further details are given in our Specification PPS&nbsp;3011&nbsp;</p>', NULL, '', NULL, 61, NULL, 0, NULL, 'Creepage Extender | Insulation Enhancement System - Raychem RPG', 'High Voltage Creepage Extenders. HVCE creepage extenders represent a long-term solution to pollution flashovers by making a permanent addition to the creepage distance.', 1, 257, '2021-08-27 11:49:02', '2022-01-05 10:09:37'),
(259, 'Overhead Line Cover', 'asset-personnel-protection/insulation-enhancement-system/overhead-line-cover', 'Overhead line covers for bare conductors. MVLC provides state-of-the-art insulation to help prevent electrical outages. It is designed to insulate existing bare lines without costly conductor replacement expenditures or additional line hardware. MVCC provides high quality electrical insulation and made from non-tracking silicone material suitable for harsh medium voltage outdoor environments.  MVCC is suitable for applications up to 25 kV phase to ground. Covers protect energized conductors from flashovers due to contact from birds and animals.', 'mjsn8wgFLAbsrtcEeSkT8eVkp0vkMu.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-overhead-line-cover.pdf', 3, '', '<header class=\"col-12 p-0 tables__title mt-5 sticky\">\r\n<h2 class=\"secondary-heading\">Power Line Protector</h2>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">Product Reference</th>\r\n<th scope=\"col\">Voltage (kV)</th>\r\n<th scope=\"col\">Roll Length (in meter)</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>POLIPRO</td>\r\n<td>1.1</td>\r\n<td>20</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-5 sticky\">\r\n<h2 class=\"secondary-heading\">Medium Voltage Line Cover</h2>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">Product Reference</th>\r\n<th scope=\"col\">Voltage (kV)</th>\r\n<th scope=\"col\">Roll Length (in meter)</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>MVLC-14-A/241 (COATED)</td>\r\n<td>33</td>\r\n<td>100</td>\r\n</tr>\r\n<tr>\r\n<td>MVLC-18-A/U</td>\r\n<td>11</td>\r\n<td>75</td>\r\n</tr>\r\n<tr>\r\n<td>MVLC-18-A/241 (COATED)</td>\r\n<td>33</td>\r\n<td>50</td>\r\n</tr>\r\n<tr>\r\n<td>MVLC-38-A/241 (COATED)</td>\r\n<td>33</td>\r\n<td>165</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<header class=\"col-12 p-0 tables__title mt-5 sticky\">\r\n<h2 class=\"secondary-heading\">Medium Voltage Conductor Cover :</h2>\r\n</header>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\" scope=\"col\">Selection</th>\r\n</tr>\r\n<tr>\r\n<th scope=\"col\">Description</th>\r\n<th scope=\"col\">Use Range UOM: mm (Inches)</th>\r\n<th scope=\"col\">Color</th>\r\n<th scope=\"col\">Supplied Length UOM: M (Feet)</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>MVCC-10/.40 (S30)</td>\r\n<td>Up to 11 (0.45)</td>\r\n<td>Red</td>\r\n<td>2 pieces at 15 (50)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-G-10/.40 (S30)</td>\r\n<td>Up to 11 (0.45)</td>\r\n<td>Grey</td>\r\n<td>2 pieces at 15 (50)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-19/.75 (S15)</td>\r\n<td>11 (0.45) &ndash; 19 (0.75)</td>\r\n<td>Red</td>\r\n<td>2 pieces at 7.5 (25)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-G-19/.75 (S15)</td>\r\n<td>11 (0.45) &ndash; 19 (0.75)</td>\r\n<td>Grey</td>\r\n<td>2 pieces at 7.5 (25)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-25/1.0 (S7)</td>\r\n<td>19 (0.75) &ndash; 28 (1.125)</td>\r\n<td>Red</td>\r\n<td>1 piece at 7.0 (25)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-G-25/1.0 (S7)</td>\r\n<td>19 (0.75) &ndash; 28 (1.125)</td>\r\n<td>Grey</td>\r\n<td>1 piece at 7.0 (25)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-45/1.75 x 4 (S7)</td>\r\n<td>28 (1.125) &ndash; 44 (1.75)</td>\r\n<td>Red</td>\r\n<td>6 pieces at 1.2 (4)</td>\r\n</tr>\r\n<tr>\r\n<td>MVCC-G-45/1.75 x 4 (S7)</td>\r\n<td>28 (1.125) &ndash; 44 (1.75)</td>\r\n<td>Grey</td>\r\n<td>6 pieces at 1.2 (4)</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\">&nbsp; <strong> Power Line Protector (POLIPRO) </strong> &nbsp;</th>\r\n</tr>\r\n<tr>\r\n<th>Properties</th>\r\n<th>Performance Parameter</th>\r\n<th>Test Method</th>\r\n<th>Requirements</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Electrical</td>\r\n<td>\r\n<p>AC Withstand (Dry)-One Minute</p>\r\n<p>AC Withstand (Wet)-One Minute</p>\r\n<p>&nbsp;Di-electric strength</p>\r\n<p>Volume Resistivity @27&deg;C</p>\r\n</td>\r\n<td>\r\n<p>ASTM D149</p>\r\n<p>ASTM D257</p>\r\n</td>\r\n<td>\r\n<p>3 KV min</p>\r\n<p>3 kV min</p>\r\n<p>10 kV/mm min</p>\r\n<p>10&sup1;&sup2;ohm-cm min</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Physical</td>\r\n<td>\r\n<p>Tensile Strength</p>\r\n<p>Ultimate Elongation</p>\r\n<p>Low Temperature Impact</p>\r\n<p>Abrasion Resistance</p>\r\n</td>\r\n<td>\r\n<p>ASTM D638</p>\r\n<p>ASTM D638</p>\r\n<p>ASTM D746</p>\r\n<p>1000 Cycles, 2068 gms</p>\r\n</td>\r\n<td>\r\n<p>10 N/sq.mm min</p>\r\n<p>200% min</p>\r\n<p>No Cracking at-20&deg;C</p>\r\n<p>20% max Thickness loss.</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Thermal</td>\r\n<td>\r\n<p>Accelerated Ageing@168hrs at (150&plusmn;2) &deg;C</p>\r\n<p>-Tensile Strength</p>\r\n<p>-Ultimate Elongation</p>\r\n</td>\r\n<td>ASTM D2671</td>\r\n<td>\r\n<p>8.5 N/sq.mm min</p>\r\n<p>100% min</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Chemical</td>\r\n<td>\r\n<p>Water Absorption 336 hrs@ (23+2) &deg;C</p>\r\n<p>Resistance to Bird Excrement</p>\r\n<p>-Tensile Strength</p>\r\n<p>-Ultimate Elongation</p>\r\n<p>&nbsp;Resistance to Cable Grease</p>\r\n<p>-Tensile Strength</p>\r\n<p>-Ultimate Elongation</p>\r\n</td>\r\n<td>\r\n<p>ASTM D570</p>\r\n<p>Uric Acid for 168hrs@60 C</p>\r\n<p>168 brs@60 &deg;C</p>\r\n</td>\r\n<td>\r\n<p>1% max</p>\r\n<p>8.5 N/sq.mm min 100% min</p>\r\n<p>8.5 N/sq.mm min 100% min</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Crosslinking</td>\r\n<td>\r\n<p>Hot Elongation 200&deg;C&nbsp;</p>\r\n<p>permanent Set @ 200&deg;C</p>\r\n</td>\r\n<td>\r\n<p>IS:10810</p>\r\n<p>IS:10810</p>\r\n</td>\r\n<td>\r\n<p>&nbsp;170 % &plusmn;&nbsp;20 %</p>\r\n<p>&nbsp;15 %&nbsp;&plusmn;&nbsp;20 %</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\"><strong> Medium Voltage Line Cover </strong></th>\r\n</tr>\r\n<tr>\r\n<th colspan=\"2\">Product Performance&nbsp;&nbsp;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Test</td>\r\n<td>MVLC-A/U&nbsp;/&nbsp;MVLC-A/241&nbsp;(sealed)</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>AC withstand (dry) -&nbsp;1&nbsp;minute</p>\r\n<p>(wet) -&nbsp;1&nbsp;minute</p>\r\n</td>\r\n<td>\r\n<p>15 kV&nbsp;min.&nbsp;/&nbsp;25 kV&nbsp;min.&nbsp;AC withstand&nbsp;</p>\r\n<p>15 kV&nbsp;min.&nbsp;/&nbsp;25 kV&nbsp;min.</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>AC long term withstand&nbsp;</p>\r\n<p>(dry)&nbsp;-&nbsp;4&nbsp;hours&nbsp;loading</p>\r\n<p>(8&nbsp;hr&nbsp;@&nbsp;130&nbsp;&deg;C;&nbsp;16&nbsp;hr&nbsp;off)</p>\r\n</td>\r\n<td>\r\n<p>8.6&nbsp;kV&nbsp;min.&nbsp;/&nbsp;14.4&nbsp;kV&nbsp;min.&nbsp;30&nbsp;day&nbsp;thermal&nbsp;</p>\r\n<p>No&nbsp;MVLC&nbsp;deformation&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Conductor&nbsp;ampacity</p>\r\n</td>\r\n<td>\r\n<p>82-89%&nbsp;of&nbsp;bare conductor&nbsp;ampacity</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\">Material properties&nbsp;per&nbsp;pps&nbsp;3010/42&nbsp;</th>\r\n<th>Test&nbsp;method</th>\r\n<th>Requirement</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Physical&nbsp;</td>\r\n<td>\r\n<p>Tensile&nbsp;Strength</p>\r\n<p>Elongation</p>\r\n</td>\r\n<td>\r\n<p>ASTM&nbsp;D638</p>\r\n<p>ASTM&nbsp;D638</p>\r\n</td>\r\n<td>\r\n<p>8&nbsp;MPa&nbsp;min.&nbsp;Ultimate</p>\r\n<p>200%&nbsp;min.</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Abrasion&nbsp;Resistance</p>\r\n<p>Impact</p>\r\n</td>\r\n<td>\r\n<p>1000&nbsp;cycles,&nbsp;2068g</p>\r\n<p>ASTM&nbsp;D746</p>\r\n</td>\r\n<td>\r\n<p>20%&nbsp;max.thickness&nbsp;loss&nbsp;Low&nbsp;Temperature</p>\r\n<p>No&nbsp;cracking&nbsp;at -20&nbsp;&deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>Electrical &nbsp;</td>\r\n<td>\r\n<p>Dielectric&nbsp;Strength</p>\r\n</td>\r\n<td>\r\n<p>ASTM&nbsp;D149</p>\r\n</td>\r\n<td>\r\n<p>217&nbsp;kV/cm&nbsp;@&nbsp;1.27&nbsp;mm</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Tracking&nbsp;and&nbsp;Erosion</p>\r\n<p>Step&nbsp;Voltage&nbsp;Method</p>\r\n</td>\r\n<td>\r\n<p>ASTM&nbsp;D2303</p>\r\n<p>(Initiate&nbsp;@&nbsp;2.5&nbsp;kV)</p>\r\n</td>\r\n<td>\r\n<p>No&nbsp;tracking&nbsp;or&nbsp;erosion Resistance</p>\r\n<p>to top&nbsp;surface&nbsp;or&nbsp;flame</p>\r\n<p>failure&nbsp;after:&nbsp;200&nbsp;minutes</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"69905\">\r\n<p>&nbsp; <strong> Medium Voltage Conductor&nbsp;Cover : </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"69905\">\r\n<p>PRODUCT PERFORMANCE&nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong>Test&nbsp;</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>AC Dry Withstand/1 min.&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"4369\">\r\n<p>35&nbsp;kV&nbsp;Line&nbsp;Voltage&nbsp;(all&nbsp;three&nbsp;phase&nbsp;covered) 25&nbsp;kV&nbsp;Line&nbsp;Voltage&nbsp;(all&nbsp;three&nbsp;phases&nbsp;covered) 25 kV&nbsp;phase-to-ground&nbsp;</p>\r\n<p>15&nbsp;kV&nbsp;phase-to-ground&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Loading&nbsp;Cycleing&nbsp;30 days at 130&deg;C&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"69905\">\r\n<p>No Deformation or Splitting&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>Low Temperature Install at 0&deg;C&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"4369\">\r\n<p>Installable without Difficulty&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong>Physical&nbsp;</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>Key Material Properties&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Test Method&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Results&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Accelerated Aging 168 hrs. 150&deg;C Tensile Strength&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>ASTM D412&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>&gt; 1.3 MPa (psi)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>Accelerated Aging 168 hrs. 150&deg;C Ultimate Elongation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>ASTM D412&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>90% min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Low Temperature Flexibility 4 hrs.- 20&deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>ASTM D2671&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>No Cracking&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong>Electrical&nbsp;</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Dielectric Strength 1.91 mm thickness&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>ASTM D149&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>&gt; 120 kV/cm (300 V/mil)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>Tracking and Erosion Resistance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>ASTM D2303&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>No&nbsp;tracking&nbsp;or&nbsp;erosion&nbsp;to&nbsp;top&nbsp;surface&nbsp;or&nbsp;flame&nbsp;failure&nbsp;after:&nbsp;</p>\r\n<p>1&nbsp;hr.&nbsp;at&nbsp;2.5&nbsp;kV&nbsp;</p>\r\n<p>1&nbsp;hr.&nbsp;at&nbsp;2.75&nbsp;kV&nbsp;</p>\r\n<p>1&nbsp;hr.&nbsp;at&nbsp;3.0&nbsp;kV&nbsp;</p>\r\n<p>20 min at 3.25 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Volume Resistivity&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>ASTM D257&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;x 10₁₃&nbsp;Ohm cm min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 61, NULL, 0, NULL, 'Overhead Line Cover | Insulation Enhancement System - Raychem RPG', 'Overhead line covers for bare conductors. MVLC provides state-of-the-art insulation to help prevent electrical outages. It is designed to insulate existing bare lines.', 1, 258, '2021-08-27 11:49:37', '2022-01-18 10:44:24'),
(260, 'Insulating Boots', 'asset-personnel-protection/insulation-enhancement-system/insulating-boots', 'Medium Voltage Insulating Boots. Cold applied unscreened elastomeric insulating boots (in Silicon or EPDM) are moulded parts, fitted over the connection between a cable lug and inline or right-angled equipment bushing, to improve phase-to-phase and phase-to-ground insulation. They are used in switchgear and transformer cable boxes where the air clearances are insufficient for normal operation or protect against flashover due to rodents or high humidity. The non-tracking elastomeric housing has excellent erosion resistance, dielectric properties, and environmental resistance, giving superb performance in areas of high humidity and electrical stresses.', 'fEgVeF935nRrMXId5OrM6U3H3B8HFb.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-insulation-enhancement-system-insulating-boots.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 240px; width: 1095px;\">\r\n<thead>\r\n<tr style=\"height: 17px;\">\r\n<th style=\"width: 494.484px; height: 17px;\" scope=\"col\">Parameter</th>\r\n<th style=\"width: 584.516px; height: 17px;\" scope=\"col\">Value</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 1085px; height: 21px;\" colspan=\"2\"><span data-contrast=\"auto\">Suitable for&nbsp;indoor&nbsp;applications&nbsp;upto&nbsp;17.5 kV system</span></td>\r\n</tr>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 1085px; height: 21px;\" colspan=\"2\"><span data-contrast=\"auto\">Improves&nbsp;air clearances&nbsp;in confined boxes</span></td>\r\n</tr>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 1085px; height: 21px;\" colspan=\"2\"><span data-contrast=\"auto\">Mounted on single or three core applications</span></td>\r\n</tr>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 494.484px; height: 21px;\"><strong><span data-contrast=\"auto\">Kit No:&nbsp;</span></strong></td>\r\n<td style=\"width: 584.516px; height: 21px;\"><strong><span data-contrast=\"auto\">Kit Contents</span></strong><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559740&quot;:259}\">&nbsp;</span></td>\r\n</tr>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 494.484px; height: 21px;\"><span data-contrast=\"auto\">CAB-RRL-KIT</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559740&quot;:259}\">&nbsp;&nbsp;</span><span data-contrast=\"auto\">(for three core cable)</span></td>\r\n<td style=\"width: 584.516px; height: 21px;\"><span data-contrast=\"auto\">Elastomeric insulating boots,&nbsp;Silicon grease,&nbsp;Installation instruction</span></td>\r\n</tr>\r\n<tr style=\"height: 21px;\">\r\n<td style=\"width: 494.484px; height: 21px;\">\r\n<p><span data-contrast=\"auto\">E-CAB-KIT</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559740&quot;:259}\">&nbsp;&nbsp;</span><span data-contrast=\"auto\">(for three core cable)</span></p>\r\n</td>\r\n<td style=\"width: 584.516px; height: 21px;\">&nbsp;E<span data-contrast=\"auto\">lastomeric insulating boots,&nbsp;Silicon grease,&nbsp;Installation instruction</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 39px; width: 1026px;\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 369.844px;\" scope=\"col\">Parameter</th>\r\n<th style=\"width: 639.156px;\" scope=\"col\">Value</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">Maximum system voltage</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">17.5 kV</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">Basic impulse level</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">75 /&nbsp;95 kV</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">AC high Voltage</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">36kV for 1 minute</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">Bushing diameter</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">46 - 70 mm</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">Bushing types</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">DIN, CEN ELEC, ANSI&nbsp;400/630A</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 369.844px;\"><span data-contrast=\"none\">Cable cross section</span></td>\r\n<td style=\"width: 639.156px;\"><span data-contrast=\"none\">35 &ndash; 400 mm&sup2;</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;<span data-contrast=\"none\">&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;&nbsp;</span>&nbsp;</p>\r\n<p>&nbsp;<span data-contrast=\"none\">&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;</span>&nbsp;</p>\r\n<p>&nbsp;<span data-contrast=\"none\">&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>\r\n<p><span data-contrast=\"none\">&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;</span>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;<span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>\r\n<p><span data-contrast=\"none\">&nbsp;</span>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; <span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>\r\n<p><span data-contrast=\"none\">&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;</span>&nbsp; &nbsp; &nbsp; &nbsp;</p>\r\n<p><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:240}\">&nbsp;</span></p>', NULL, '', NULL, 61, NULL, 0, NULL, 'Insulating Boots | Insulation Enhancement System - Raychem RPG', 'Medium Voltage Insulating Boots. Cold applied unscreened elastomeric insulating boots (in Silicon or EPDM) are moulded parts, fitted over the connection between a cable lug and inline.', 1, 259, '2021-08-27 11:50:05', '2021-12-28 06:08:10'),
(261, 'Post Insulators', 'asset-personnel-protection/polymeric-insulators/post-insulators', 'Post Insulators up to 52kV. Polymeric insulators combine mechanical strength with excellent pollution performance. High tensile strength of glass fiber combined with HV shed profile makes the insulator rugged and light weight for Line Post and Station Post applications.', 'eU98xR2A9e0bUlWISv5mhkVEoUbUNm.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-insulators-post-insulators.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 115px;\" width=\"808\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 798.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Available up to 52kV rating</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Available from 5kN to 15kN mechanical rating</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Offered in both Silicone &amp; EVA as housing material</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Available up to 40 mm/kV creepage distance</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Product qualification as per IEC 62217, IEC 61952 &amp; IEC 62231 specifications</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Aerodynamic shed profile as per IEC815</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 798.395px;\">Have verity of end fitting options</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, NULL, NULL, '', NULL, 62, NULL, 0, NULL, 'Post Insulators | Polymeric Insulators - Raychem RPG', 'Post Insulators up to 52kV. Polymeric insulators combine mechanical strength with excellent pollution performance. High tensile strength of glass fiber combined with HV shed profile', 1, 260, '2021-08-27 11:50:51', '2022-01-05 05:48:32'),
(262, 'Suspension & Tension Insulators', 'asset-personnel-protection/polymeric-insulators/suspension-tension-insulators', 'Polymeric Insulators for suspension and tension application up to 110kV. Polymeric Insulators combine mechanical strength with excellent pollution performance. High tensile strength of glass fiber combined with HV shed profile makes the insulator rugged and light weight for tension and suspension application in distribution lines.', 'fMewr9tRdCcXbFnfWOjNyPA8ZR6m47.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-insulators-suspension-tension-insulators.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 171px;\" width=\"713\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 703.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Available up to 110kV rating</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Available from 45kN to 120kN mechanical rating</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Offered in both Silicone &amp; EVA as housing material</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Available up to 40 mm/ kV creepage distance</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Product qualification as per IEC 62217, IEC 61109 &amp; ANSI specification</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Aerodynamic shed profile as per IEC815</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 703.395px;\">Have variety of end fitting options as per IEC61466</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 358px; width: 894px; margin-left: auto; margin-right: auto;\">\r\n<thead>\r\n<tr>\r\n<th><strong> &nbsp;Parameter </strong></th>\r\n<th><strong> Value </strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Creepage Distance</td>\r\n<td>265-3010</td>\r\n</tr>\r\n<tr>\r\n<td>Arcing Distance</td>\r\n<td>125-885</td>\r\n</tr>\r\n<tr>\r\n<td>No of Sheds</td>\r\n<td>3-37</td>\r\n</tr>\r\n<tr>\r\n<td>SML (kN)</td>\r\n<td>45 - 120</td>\r\n</tr>\r\n<tr>\r\n<td>RTL (kN)</td>\r\n<td>22.5 - 60</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Dry AC flashover voltage (kV)</p>\r\n</td>\r\n<td>104-200</td>\r\n</tr>\r\n<tr>\r\n<td>Wet AC flashover voltage (kV)</td>\r\n<td>72-165</td>\r\n</tr>\r\n<tr>\r\n<td>Dry AC withstand voltage (kV)</td>\r\n<td>95-175</td>\r\n</tr>\r\n<tr>\r\n<td>Wet AC withstand voltage (kV)</td>\r\n<td>61-145</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Impulse withstand voltage (kV)</p>\r\n</td>\r\n<td>137-310</td>\r\n</tr>\r\n<tr>\r\n<td>End fittings configurations</td>\r\n<td>Ball, Socket, Tongue, Eye, Clevis &amp; Y clevis as per IEC 61466</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 62, NULL, 0, NULL, 'Suspension Tension Insulators | Polymeric Insulators - Raychem RPG', 'Polymeric Insulators for suspension and tension application up to 110kV. Polymeric Insulators combine mechanical strength with excellent pollution performance.', 1, 261, '2021-08-27 11:52:38', '2022-01-05 06:36:54'),
(263, 'Railway Insulators', 'asset-personnel-protection/polymeric-insulators/railway-insulators', 'Polymeric Insulator for railway application up to 25kV. Polymeric Railway Insulators combine mechanical strength with excellent pollution performance. High tensile strength of glass fiber combined with HV shed profile makes the insulator rugged and light weight for traction application.', 'QiMnRArfY6J8g4Bak9zYkLRh2XYrcB.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-insulators-railway-insulators.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 52px;\" width=\"695\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 685.398px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 685.398px;\">Available in 25 &amp; 31 mm/kV creepage distance</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 685.398px;\">Product qualification as per IEC 62217 &amp; RDSO specifications</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 685.398px;\">Aerodynamic and double alternative shed profile as per IEC815</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 612px; width: 819.898px;\">\r\n<thead>\r\n<tr style=\"height: 30px;\">\r\n<th style=\"width: 251px; height: 30px; text-align: left;\"><span style=\"font-size: 12pt;\"><strong>General characteristics:</strong></span></th>\r\n<th style=\"width: 56px; height: 30px; text-align: center;\"><span style=\"font-size: 12pt;\"><strong>Unit</strong></span>&nbsp;</th>\r\n<th style=\"width: 205px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;9 Tonne</strong></span></th>\r\n<th style=\"width: 127px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>Bracket Tube</strong></span></th>\r\n<th style=\"width: 146.898px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>Stay Arm Tube</strong></span></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr style=\"height: 8.39062px;\">\r\n<td style=\"width: 251px; height: 8.39062px;\">Applicable standard</td>\r\n<td style=\"width: 56px; height: 8.39062px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 8.39062px; text-align: center;\" colspan=\"3\">\r\n<p>IEC 61109, IEC 62217 &amp; RDSO specification No T1/SPC/OHE/INSCOM/1071, Rev.1</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Material of FRP rod</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Boron free, ECR grade</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Material of housing</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Silicone, Grey</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\" colspan=\"5\"><span style=\"font-size: 12pt;\"><strong>Mechanical Characteristics:</strong></span>&nbsp;&nbsp;&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Type of shed profile</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Aerodynamic</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Applicable standard for shed profile</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;IEC 60815</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Creepage distance</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;mm</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;1600 &amp; 1050</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Specified tensile load</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kgf</td>\r\n<td style=\"width: 205px; height: 17px; text-align: center;\">&nbsp;11,000</td>\r\n<td style=\"width: 127px; height: 17px; text-align: center;\">&nbsp;7,000</td>\r\n<td style=\"width: 146.898px; height: 17px; text-align: center;\">&nbsp;7,000</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Specified cantilever load</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;Kgf.m</td>\r\n<td style=\"width: 205px; height: 17px; text-align: center;\">&nbsp;210</td>\r\n<td style=\"width: 127px; height: 17px; text-align: center;\">&nbsp;200</td>\r\n<td style=\"width: 146.898px; height: 17px; text-align: center;\">&nbsp;200</td>\r\n</tr>\r\n<tr style=\"height: 46px;\">\r\n<td style=\"width: 251px; height: 46px;\" colspan=\"5\"><span style=\"font-size: 12pt;\"><strong>Electrical Characteristics:</strong></span>&nbsp;&nbsp;&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Nominal system voltage</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;25</td>\r\n</tr>\r\n<tr style=\"height: 6px;\">\r\n<td style=\"width: 251px; height: 6px;\">\r\n<p>Wet power frequency withstands voltage (Horizontal Position)</p>\r\n</td>\r\n<td style=\"width: 56px; height: 6px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 6px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;125</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">(Vertical Position)</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;100</td>\r\n</tr>\r\n<tr style=\"height: 2px;\">\r\n<td style=\"width: 251px; height: 2px;\">\r\n<p>Dry lighting impulse withstand voltage.</p>\r\n<p style=\"text-align: right;\">(Positive Polarity)</p>\r\n</td>\r\n<td style=\"width: 56px; height: 2px; text-align: center;\">&nbsp;kVp</td>\r\n<td style=\"width: 478.898px; height: 2px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;240</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px; text-align: right;\">(Negative Polarity)</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kVp</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;260</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Visible discharge test voltage</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;35</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 62, NULL, 0, NULL, 'Railway Insulators | Polymeric Insulators - Raychem RPG', 'Polymeric Insulator for railway application up to 25kV. Polymeric Railway Insulators combine mechanical strength with excellent pollution performance.', 1, 262, '2021-08-27 11:53:03', '2022-01-06 10:16:20'),
(264, 'LV Surge Arresters upto 440 V', 'asset-personnel-protection/polymeric-surge-arresters/lv-surge-arresters-upto-440-v', 'LV Surge Arrester upto 440V for substation protection from lightening and switching overvoltages. LV Surge Arresters provide protection for low-voltage overhead lines, consumer in-house  supplies, distribution transformers and other systems. Numerous tests have confirmed durability of the housing, even when exposed to extreme temperature fluctuations and contamination', '9wzs8WEY91weD72f3QGMzQ6671vwHB.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-surge-arresters-lv-surge-arresters-upto-440-v.pdf', NULL, '', NULL, NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Type </strong></p>\r\n</th>\r\n<th data-celllook=\"0\">&nbsp;</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> LVA-280B </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> LVA-440B </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Continuous operating voltage&nbsp;(Uc)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>V&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>280&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>440&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Applicable standard /class&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">&nbsp;</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>IEC 61643-1 / Class II / Imax= 40 kA&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Nominal discharge current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>10&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>High current impulse 4/10&micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>100&nbsp;&nbsp;</p>\r\n<p>(test&nbsp;as per IEC 60099-4)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>48 &ndash; 62&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Ambient temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&deg;C&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>-40&nbsp;to&nbsp;+70&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Energy absorption during line discharge impulses (2shots):&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kJ/kV&middot;Uc&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>4.1&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Maximum Discharge current&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"0\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 63, NULL, 0, NULL, 'LV Surge Arresters upto 440 V | Polymeric Surge Arresters - Raychem RPG', 'LV Surge Arrester upto 440V for substation protection from lightening and switching overvoltages. LV Surge Arresters provide protection for low-voltage overhead lines.', 1, 263, '2021-08-27 11:55:03', '2022-01-05 09:25:22');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(265, 'MV Surge Arresters upto 36 kV', 'asset-personnel-protection/polymeric-surge-arresters/mv-surge-arresters-upto-36-kv', 'MV Surge Arrester upto 45kV for substation protection from lightening and switching over voltages. In past 15 years, almost all high-voltage networks used MO arresters.  However, in medium-voltage networks,   a   substantial number of conventional gapped arresters (SiC resistors and series spark gaps) were  installed until  a few years ago. Today MO (Metal-Oxide) arresters without spark gaps have gained popularity. Networks require improved protection level and better performance in polluted environments. The switch to polymeric housings made it possible to do without the previously necessary spark gaps. Polymeric housings   are reliable against ingress of moisture and provide minimal risk of failures (violent shattering of the housing). MVSA are manufactured using high quality MOV blocks which display excellent thermal and current handling characteristics due to guaranteed homogeneity of the varistor volume.  In the wrap design surge arresters, the MOV blocks are wrapped with fiberglass ribbons impregnated with epoxy resin to create stacks of MOV blocks.', 'qOAqRVh0KIVT3RR0lXxkKktz2ir32V.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-surge-arresters-mv-surge-arresters-upto-36-kv.pdf', 3, '', '<table class=\"col-12 table\" width=\"778\">\r\n<thead>\r\n<tr>\r\n<th>\r\n<p><strong> Distribution&nbsp;Medium&nbsp;Duty (DM) Class MV&nbsp;Surge&nbsp;Arrester (Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p><strong><span style=\"color: #ffffff;\">Bowthorpe&nbsp;EMP DA0 series surge arrester</span>&nbsp; </strong> &nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>\r\n<p>Tested in accordance with IEC60099-4 at independent accredited laboratories&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p><span data-contrast=\"auto\">Direct moulded housing&nbsp;prevents&nbsp;moisture ingress&nbsp;</span><span data-ccp-props=\"{&quot;134233279&quot;:true,&quot;201341983&quot;:0,&quot;335559739&quot;:160,&quot;335559740&quot;:240}\">&nbsp;</span></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Low residual voltages&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>High-energy handling&nbsp;safe non-shattering short circuit&nbsp;behavior&nbsp;at&nbsp;higher current levels&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Maintenance free Hydrophobic silicone housing, tracking and erosion resistant&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Excellent cantilever and tensile performance&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Quality design&nbsp;conforming to&nbsp;international standards&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Application&nbsp;- protection of MV networks and equipment from lightning and switching surge related over-voltages,&nbsp;optimized to protect distribution assets including transformers and cable-end terminations&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">\r\n<p><strong> Distribution Heavy Duty (DH) Class MV Surge Arrester (Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>\r\n<p>Safe non-shattering short circuit behaviour to higher current levels&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Cage design&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Type tested&nbsp;in accordance with IEC60099-4, Ed 3.0 (2014)&nbsp;at independent laboratories&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Alternating sheds for best pollution flashover resistance&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Hydrophobic silicone housing for outdoor use&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Excellent operating performance&nbsp;and&nbsp;long service life&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<p>Directly&nbsp;molded&nbsp;housing prevents moisture ingress&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp;</p>\r\n<p><strong> Distribution Medium&nbsp;Duty (DM) Class MV&nbsp;Surge&nbsp;Arrester (Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">&nbsp;</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> DA0 </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Application&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp; &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated voltage Ur&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3-12&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Line discharge class as per IEC60099-4 &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Arrester class designation &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>DM&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated discharge current 8/20 &micro;s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current impulse 4/10&micro;s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p>TOV (kV) &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>1s&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.18xUr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>100s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.12xUr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current short circuit Pre failing method &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p>Mechanical data&nbsp; &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Cantilever&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Nm &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>150&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Tension&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> N&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1000&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Torque&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> Nm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>30&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp; <strong> Distribution&nbsp;Heavy&nbsp;Duty (DH) Class MV&nbsp;Surge&nbsp;Arrester &ndash;(Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> DA1 </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> HDA </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> HDA-M </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> OCP-1 </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Application&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated voltage Ur&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>4-45</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> 3.7-30&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>32.5-51.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> 4-51.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Line discharge class as per IEC60099-4 &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Arrester class designation &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated discharge current 8/20 &micro;s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current impulse 4/10&micro;s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Energy (according to IEC 99-4, 8.5) Line discharge &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>5.6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>5.3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>5.3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>5.1&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current short circuit Pre failing method &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>21&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"6\" data-celllook=\"69905\">\r\n<p>Mechanical data&nbsp; &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Cantilever&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Nm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Tension&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>N&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2000&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2000&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2000&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2000&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Torque&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Nm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp; <strong> Distribution&nbsp;Heavy&nbsp;Duty (DH) Class MV&nbsp;Surge&nbsp;Arrester (Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> DOV&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Application&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp; &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated voltage Ur&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3- 36&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Arrester class designation </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated discharge current 8/20 &micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current impulse 4/10&micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Repetitive Charge transfer rating (Qrs) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>C</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>0.4&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Thermal Charge transfer rating (Qth) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>C</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.1&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong> &nbsp;TOV (kV) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1s&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.12xUr</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.08xUr</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp;</p>\r\n<p><strong> Distribution&nbsp;Heavy&nbsp;Duty (DH) Class MV&nbsp;Surge&nbsp;Arrester&nbsp;(Indoor) </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">&nbsp;</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> RDA </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> SPA&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> CPA&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Application&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Indoor</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Indoor</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Indoor</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated voltage Ur&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.5-30&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.5-40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>4-51.5 &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Arrester class designation </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>DH&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated discharge current 8/20 &micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current impulse 4/10&micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Energy (according to IEC 99-4, 8.5) Line discharge </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3.3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3.3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3.3&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.25&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current short circuit Pre failing method </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"5\" data-celllook=\"69905\">\r\n<p><strong> Mechanical data&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Cantilever&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Nm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>200&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>200&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>200&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Tension&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>N&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1000&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1000&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1000&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Torque&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Nm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>58&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>58&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>58&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp; <strong> Station&nbsp;Low&nbsp;Duty (SL) Class MV&nbsp;Surge Arrester (Indoor) </strong></p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> PCA-I </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Application&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Indoor &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated voltage Ur&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>6- 72.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Arrester class designation </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SL&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated discharge current 8/20 &micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current impulse 4/10&micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Energy (according to IEC 99-4, 8.5) Line discharge </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.8&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Repetitive Charge transfer rating&nbsp;Qrs) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>C</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2.2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong> TOV (kV) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1s&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.15x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.10x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current short circuit Pre failing method </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>63&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"69905\">\r\n<p><strong> Mechanical strength&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Safe Long -term load (SLL)&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kNm</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Safe Long -term load (SSL)&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kNm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>   </strong> &nbsp; <strong> Station&nbsp;Low&nbsp;Duty (SL) Class MV&nbsp;Surge&nbsp;Arrester (Outdoor) </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> OCP-2 </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> PAA1 </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> PCA-I </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Application&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp; &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated voltage Ur&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>6- 72.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>6- 72.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>6-42&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Arrester class designation </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SL</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SL</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SL</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Rated discharge current 8/20 &micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current impulse 4/10&micro;s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Energy (according to IEC 99-4, 8.5) Line discharge </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>4.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.8&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"5\" data-celllook=\"69905\">\r\n<p><strong> &nbsp;TOV (kV) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1s&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.14 x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.08x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.15x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10s </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.12x Ur</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.04x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.10x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> High current short circuit&nbsp;(Pre failing method) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>65&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 63, NULL, 0, NULL, 'MV Surge Arresters upto 36 kV | Polymeric Surge Arresters - Raychem RPG', 'MV Surge Arrester upto 45kV for substation protection from lightening and switching over voltages. In past 15 years, almost all high-voltage networks used MO arresters.', 1, 264, '2021-08-27 11:55:26', '2022-01-18 09:50:46'),
(266, 'HV Surge Arresters upto 245 kV', 'asset-personnel-protection/polymeric-surge-arresters/hv-surge-arresters-upto-245-kv', 'HV Surge Arrester upto 216kV for substation protection from lightening and switching overvoltages. Bowthorpe EMP pioneered the development of polymeric composite housed surge arresters in early 1980’s and since 1986, has a proven service experience across the globe, operating in world’s toughest environments. Bowthorpe surge arresters provide active over-voltage protection, reducing system outages and protecting expensive terminal equipment.', 'kLUFZ6aypCAfDbzvSGt6JPHbiTsupe.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-surge-arresters-hv-surge-arresters-upto-245-kv.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 161px;\" width=\"788\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 778.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Tested in accordance with IEC60099-4 at independent accredited laboratories</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Direct moulded housing to prevent&nbsp;ingress of&nbsp;moisture</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Low residual voltages</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Safe non-shattering short circuit behaviour to higher current levels</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Maintenance free</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Hydrophobic silicone housing (tracking and erosion resistant)</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"auto\">Excellent cantilever and tensile performance</span></td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong>Type  </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> PCA-I </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"69905\">\r\n<p><strong> PAA4 </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated voltage Ur&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>66-245&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>66-245&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Line discharge class as per IEC60099-4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Arrester class designation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SM&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>SL&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated discharge current 8/20 &micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current impulse 4/10&micro;s &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Energy (according to IEC 99-4, 8.5) Line discharge &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>7.8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>4.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Repetitive Charge transfer rating (Qrs)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>C&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>TOV&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Calibri\" data-listid=\"7\" data-aria-posinset=\"2\" data-aria-level=\"1\">1s&nbsp;&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.15x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.08x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Calibri\" data-listid=\"7\" data-aria-posinset=\"2\" data-aria-level=\"1\">10s&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.10x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.04x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current short&nbsp;circuit Pre&nbsp;failing method&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>63&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Mechanical&nbsp;Strength&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Outdoor&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Calibri\" data-listid=\"7\" data-aria-posinset=\"2\" data-aria-level=\"1\">High current short circuit Pre-failing method&nbsp;&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>65&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Calibri\" data-listid=\"7\" data-aria-posinset=\"2\" data-aria-level=\"1\">Safe Long -term load (SLL)&nbsp;&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kNm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>0.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<ul>\r\n<li data-leveltext=\"-\" data-font=\"Calibri\" data-listid=\"7\" data-aria-posinset=\"2\" data-aria-level=\"1\">Safe Long -term load (SSL)&nbsp;&nbsp;</li>\r\n</ul>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kNm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>2.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>0.6&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 63, NULL, 0, NULL, 'HV Surge Arresters upto 245 kV | Polymeric Surge Arresters - Raychem RPG', 'HV Surge Arrester upto 216kV for substation protection from lightening and switching overvoltages.', 1, 265, '2021-08-27 11:55:54', '2022-01-05 09:26:24'),
(267, 'Transmission Line Surge Arresters upto 400kV', 'asset-personnel-protection/polymeric-surge-arresters/transmission-line-surge-arresters-upto-400kv', 'Transmission Line Surge Arrester (NGLA) upto 400kV, Power supply utilities have verified load losses due to voltage snags on their systems from transitory outages caused by lightning activity and causing permanent damages.  The effect of these transitory disturbances on transmission lines are more critical in areas with high ground resistivity when associated with high lightning activity.  Most non-scheduled outages are transitory in nature, with a fault time shorter than 1 minute, yet deemed to be unacceptable by power supply utilities.  The loss of supply is critical for all modern industries reliant on sophisticated electronic equipment and production processes sensitive to momentary disturbances to the system.  Raychem RPG’s Transmission Line Surge Arresters (TLA) provides reliability to the power system by reducing non-schedule outages caused by lightening.', 'CR6FHJ4S77DmrxTofTjHcfenAItlD6.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-asset-personnel-protection-polymeric-surge-arresters-transmission-line-surge-arresters-upto-400kv.pdf', NULL, '', NULL, NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"69905\">\r\n<p><strong> &nbsp;Type </strong></p>\r\n</th>\r\n<th data-celllook=\"69905\">&nbsp;</th>\r\n<th colspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> MVSA&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> HVSA </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n<p>Application</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp; &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>TL-PCA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>TL-PAA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>TL-PCA</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>TL-PAA&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated voltage Ur</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>6-42&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>6-42&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>66-400</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>66-400&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Line discharge class as per IEC60099-4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Arrester class designation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>SM&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>SL&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>SM&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>SL&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rated discharge&nbsp;current 8/20 &micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Safe short term load(SSL) 4/10&micro;s</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>100&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Energy (according to IEC 99-4, 8.5) Line&nbsp;discharge</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kJ / kV Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Repetitive Charge transfer rating (Qrs)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>C&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"6\" data-celllook=\"69905\">\r\n<p>&nbsp;TOV (kV)&nbsp;</p>\r\n<p> &nbsp;</p>\r\n<p> &nbsp;</p>\r\n<p> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>1s</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.15x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.08x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.15x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.08x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>10s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.09&nbsp;xUr&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.04x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.09&nbsp;x Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.04x Ur&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>High current short circuit&nbsp;(Pre failing method)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>63&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>63&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>40&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, 63, NULL, 0, NULL, 'Transmission Line Surge Arresters upto 400kV | Polymeric Surge Arresters - Raychem RPG', 'Transmission Line Surge Arrester (NGLA) upto 400kV, Power supply utilities have verified load losses due to voltage snags on their systems from transitory outages.', 1, 266, '2021-08-27 11:56:19', '2022-01-05 09:24:18');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(268, 'Heat Shrink Low Voltage Joints', 'reliable-connections/power-cable-accessories/low-voltage-joints-terminations/heat-shrink-low-voltage-joints/heat-shrink-low-voltage-joints', '1.1kV Heat Shrink Joint -conventional and next generation. Raychem products offer excellent insulating and sealing performance with heat shrinkable\r\nmaterials. These proven materials form the basis of straight and branch joints for voltages up to 1.1 kV and designed for solid dielectric cables (PVC/Rubber/XLPE).', 'e3nxrF4YuFkJQGsehjajOClOCVi1tc.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-power-cable-accessories-low-voltage-joints-terminations-heat-shrink-low-voltage-joints-heat-shrink-low-voltage-joints.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 108px;\" width=\"707\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 697.386px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"auto\">High&nbsp;reliability&nbsp;and low skilled features with unlimited shelf life for heat shrink materials</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"auto\">Suitable for wide range of crimp and&nbsp;mechanical connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"auto\">Suitable for&nbsp;single&nbsp;/&nbsp;multi-core, armoured&nbsp;/&nbsp;unarmoured&nbsp;cables</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"auto\">Type tested as per National and International standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 1.1 KV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Rated Voltage of Cable accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.1 kV&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>IS: 13573- Part 1, 2011&nbsp;/ EN50393&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Air&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Water&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Immersed)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">6.</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7.</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impact Test for Straight Joints&nbsp;(armoured cables)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>No damage&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand (Water)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>9.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10.</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Thermal Short Circuit&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>As per&nbsp;cable cross section and material of conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11.&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing Material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>12.</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10 kV/mm min&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 89, NULL, 0, NULL, 'Heat Shrink Low Voltage Joints | Low Voltage Joints & Terminations - Raychem RPG', '1.1kV Heat Shrink Joint -conventional and next gen. Raychem products offer excellent insulating and sealing performance with heat shrinkable\r\nmaterials View more information online!', 1, 267, '2021-08-27 12:33:08', '2022-02-21 16:05:00'),
(269, 'Cold Applied Low Voltage Joints', 'reliable-connections/power-cable-accessories/low-voltage-joints-terminations/cold-applied-low-voltage-joints/cold-applied-low-voltage-joints', '1.1kV Cold Applied Rayvolve Roll-on Joint. Rayvolve RVS jointing is the “roll-on” way to insulate and seal cable connections up to 1.1kV. The gripping force, of a specially formulated EPDM elastomer, combined with high-performance sealant forms a reliable and water-resistant insulating sleeve. The product is UL listed and CSA certified for direct burial applications.', 'tIGb6tcdWkUIrYxfwgpEMUTqAV8VLv.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-power-cable-accessories-low-voltage-joints-terminations-cold-applied-low-voltage-joints-cold-applied-low-voltage-joints.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 121px;\" width=\"707\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 697.386px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"none\">Tool Free installation</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"none\">UV and Fungi resistant</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"none\">Suitable for single and&nbsp;multi-core&nbsp;applications</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\"><span data-contrast=\"none\">Immediate energisation of joint after installation</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 697.386px;\">Unlimited shelf life</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 1.1 KV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Rated Voltage of Cable accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.1 kV&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>IS: 13573- Part 1, 2011&nbsp;/ EN50393&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Air&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Water&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Water)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impact Test for Straight&nbsp;Joints (armoured cables)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>No damage&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand&nbsp;(water)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>9.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Thermal Short Circuit&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>As per&nbsp;cable cross section and material of conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing Material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Cold Applied (Roll-On Sleeve) Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10 kV/mm min&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', 6, 89, NULL, 0, NULL, 'Cold Applied Low Voltage Joints | Low Voltage Joints & Terminations - Raychem RPG', '1.1kV Cold Applied Roll-on Joint. Rayvolve RVS jointing is the “roll-on” way to insulate and seal cable connections up to 1.1kV. View more information online!', 1, 268, '2021-08-27 12:33:52', '2022-01-05 09:38:33'),
(270, 'Heat Shrink Low Voltage Terminations', 'reliable-connections/power-cable-accessories/low-voltage-joints-terminations/heat-shrink-low-voltage-terminations/heat-shrink-low-voltage-terminations', '1.1kV Heat Shrink Termination. Low voltage cable crutch is sealed by an adhesive lined heat-shrinkable breakout installed over cores and end of over sheath. The heat-shrinkable tubing seals between the cable lug and end of core insulation. All materials are resistant to UV-light and weathering', 'Excy2CWRT6gsqHA2ydU4PUPsL6pcc9.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-power-cable-accessories-low-voltage-joints-terminations-heat-shrink-low-voltage-terminations-heat-shrink-low-voltage-terminations.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 101px;\" width=\"739\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 729.389px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 729.389px;\"><span data-contrast=\"auto\">High&nbsp;reliability and low skilled features&nbsp;with unlimited shelf life for heat shrink materials</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 729.389px;\"><span data-contrast=\"auto\">Suitable for wide range of crimp and&nbsp;mechanical connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 729.389px;\"><span data-contrast=\"auto\">Suitable for&nbsp;single / multi core, armoured / unarmoured&nbsp;cables</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 729.389px;\"><span data-contrast=\"auto\">Suitable for indoor and&nbsp;outdoor&nbsp;applications</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 729.389px;\"><span data-contrast=\"auto\">Type tested as per National and International standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 1.1 KV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Rated Voltage of Cable accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>1.1 kV&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>IS: 13573- Part 1, 2011&nbsp;/&nbsp;EN50393&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Air&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"4369\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Test&nbsp;in Water&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Total cycle = 63 nos.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a. Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>5 hours (maintain 2 hrs min as steady state)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b. Temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>PVC - 75&deg;C, XLPE - 95&deg;C.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c. Cooling Duration&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Water)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n<td data-celllook=\"4369\">\r\n<p>Insulation Resistance&nbsp;Test (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 M&Omega; (Min)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impact Test for Straight Joints&nbsp;(armoured cables)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>No damage&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand (Water)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>A.C. Voltage Withstand (Air)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4 KV for&nbsp;1&nbsp;minute&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>9.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Thermal Short Circuit&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>As per&nbsp;cable cross section and material of conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing Material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10 kV/mm min&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 89, NULL, 0, NULL, 'Heat Shrink Low Voltage Terminations | Low Voltage Joints & Terminations - Raychem RPG', '1.1kV Heat Shrink Termination. Low voltage cable crutch is sealed by an adhesive lined heat-shrinkable breakout installed over cores and end of over sheath. View more information online!', 1, 269, '2021-08-27 12:34:41', '2022-01-05 09:48:41'),
(271, 'Heat Shrink Medium Voltage Joints', 'reliable-connections/power-cable-accessories/medium-voltage-joints-terminations/heat-shrink-medium-voltage-joints/heat-shrink-medium-voltage-joints', 'Medium Voltage Heat Shrink Joints-Conventional and next generation. Raychem developed highly specialized polymers for heat shrink joints suitable for plastic and paper cables upto 36 kV. For transition joints, a special oil barrier tubing is used to transform draining oil (MI) and non-draining oil (MIND) paper insulated cable into quasi-polymeric insulated cable with a radial field.   \r\n\r\nThe conventional design developed in 1980 was based on multiple layer tubing concept providing insulation and stress functions. The latest developed heat shrink joint is a single tubing (triple layer co-extruded) of adequate thickness which provides insulation for a particular voltage range.', '0wT5zOyB3ezhXRQRE2DFCrZ8pvjehu.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-medium-voltage-joints-terminations-heat-shrink-medium-voltage-joints-heat-shrink-medium-voltage-joints.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 118px;\" width=\"644\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 634.389px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 634.389px;\"><span data-contrast=\"none\">Unlimited&nbsp;shelf life&nbsp;for&nbsp;heat&nbsp;shrink&nbsp;components</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 634.389px;\"><span data-contrast=\"none\">Suitable for wide range of connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 634.389px;\"><span data-contrast=\"none\">Immediate energization</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 634.389px;\"><span data-contrast=\"none\">Pre-Engineered Kit</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 634.389px;\"><span data-contrast=\"none\">Tested as per National &amp; International Standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 7.2 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 12 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 24 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 36 KV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>IEC 60502-4, CENELEC HD 629.1, IS 13573-2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Rated Voltage of&nbsp;cable accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3.8/6.6 (7.2)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>6.35/11 (12)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>12.7/22 (24)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>19/33 (36)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Brand&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem- RPG&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Accessories&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Heat Shrink type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>AC Voltage test&nbsp;&nbsp;</p>\r\n<p>Dry for 5 minutes&nbsp;</p>\r\n<p>Wet for 1 minute&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>17.1 kV&nbsp;</p>\r\n<p>15.2 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>28.5 kV&nbsp;</p>\r\n<p>25.4 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>57.1 kV&nbsp;</p>\r\n<p>50.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>85.5 kV&nbsp;</p>\r\n<p>76 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>DC Voltage test for 15 min&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.2 kV&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>25.4 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>76 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge at 1.73U0&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impulse Voltage at ambient &amp; elevated temp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>60&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>75&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>125&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>170&nbsp;kVp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>9.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Load Cycle test&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>60 cycles in air &amp; water&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>5 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Temperature&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>95 - 100&deg; C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Cooling Duration&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>d.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Voltage&nbsp;withstand&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>&nbsp;9.5 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>31.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>47.5 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Humidity Test for 300 hrs.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.93 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>23.7 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Salt fog test for 1000 hrs.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.93 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>23.7 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>12.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Method of Stress Control&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Resistive based&nbsp;</p>\r\n<p>(ZnO&nbsp;based available in termination on req.)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>13.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing &amp; Molded parts&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>14.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Non-tracking material&nbsp;&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>As per ASTM D-2303&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>15.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>10 kV/mm minimum&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 97, NULL, 0, NULL, 'Heat Shrink Medium Voltage Joints | Medium Voltage Joints & Terminations - Raychem RPG', 'Medium Voltage Heat Shrink Joints-Conventional and next gen. Raychem developed highly specialized polymers for heat shrink joints suitable for plastic and paper cables upto 36 kV. View more information online!', 1, 270, '2021-08-27 12:35:04', '2022-01-05 09:55:20'),
(272, 'Heat Shrink Medium Voltage Terminations', 'reliable-connections/power-cable-accessories/medium-voltage-joints-terminations/heat-shrink-medium-voltage-terminations/heat-shrink-medium-voltage-terminations', 'Medium Voltage Heat Shrink Terminations-Conventional and next generation.', 'DhX1fMQ5UVdRi64nhYOYkhgPDDA037.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-medium-voltage-joints-terminations-heat-shrink-medium-voltage-terminations-heat-shrink-medium-voltage-terminations.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 123px;\" width=\"788\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 778.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"none\">Unlimited&nbsp;shelf&nbsp;life for&nbsp;heat&nbsp;shrink components</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"none\">Suitable for wide range of connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"none\">Immediate energization</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"none\">Pre-Engineered Kit</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 778.395px;\"><span data-contrast=\"none\">Tested as per National &amp; International Standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 7.2 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 12 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 24 KV </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> 36 KV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>IEC 60502-4, CENELEC HD 629.1, IS 13573-2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Rated Voltage of&nbsp;cable accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>3.8/6.6 (7.2)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>6.35/11 (12)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>12.7/22 (24)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>19/33 (36)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Brand&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem-RPG&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Raychem- RPG&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Accessories&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Heat Shrink type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>AC Voltage test&nbsp;&nbsp;</p>\r\n<p>Dry for 5 minutes&nbsp;</p>\r\n<p>Wet for 1 minute&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>17.1 kV&nbsp;</p>\r\n<p>15.2 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>28.5 kV&nbsp;</p>\r\n<p>25.4 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>57.1 kV&nbsp;</p>\r\n<p>50.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>85.5 kV&nbsp;</p>\r\n<p>76 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>DC Voltage test for 15 min&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.2 kV&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>25.4 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>76 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge at 1.73U0&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impulse Voltage at ambient &amp; elevated temp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>60&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>75&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>125&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>170&nbsp;kVp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>9.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Load Cycle test&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>60 cycles in air &amp; water&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>a.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Each cycle heating duration&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>5 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>b.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Temperature&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>95 - 100&deg; C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>c.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Cooling Duration&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>3 hours&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>d.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Voltage withstand&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>&nbsp;9.5 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>31.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>47.5 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Humidity Test for 300 hrs.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.93 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>23.7 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Salt fog test for 1000 hrs.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>4.7 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>7.93 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>15.8 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>23.7 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>12.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Method of Stress Control&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Resistive based&nbsp;</p>\r\n<p>(ZnO&nbsp;based available in termination on req.)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>13.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing&rsquo;s &amp; Molded parts&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>14.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Non-Tracking material&nbsp;&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>As per ASTM D-2303&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>15.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"4369\">\r\n<p>10 kV/mm minimum&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 98, NULL, 0, NULL, 'Heat Shrink Medium Voltage Terminations | Medium Voltage Joints & Terminations - Raychem RPG', 'Conventional Terminations - Universal termination based on impedance (resistant) based stress control system upto 36 kV View more information online!', 1, 271, '2021-08-27 12:35:23', '2022-01-05 10:03:52'),
(273, 'Medium Voltage Switchgear Terminations', 'reliable-connections/power-cable-accessories/medium-voltage-joints-terminations/medium-voltage-switchgear-terminations/medium-voltage-switchgear-terminations', 'Medium Voltage screened separable connectors for switchgears. Raychem developed screened separable connectors for switchgears which are compact and space saving, having high degree of reliability and safety. These terminations are designed, developed, and tested upto 36 kV for almost all sizes of cables. Switchgear terminations are either OUTER CONE type (suitable for bushings as per EN 50181 for Type A (250 Amps), B (400 Amps), C (630/800 & 1250 Amps)) or INNER CONE type Size 2 (800 Amps) and Size 3 (1250 Amps).  Screened separable connectors conform to IEEE bushings and terminations to CENELEC HD 629.1 and IS 13573-2 standards.', 'MCP1VHyM00npSpLxcU6HMjGqwMVNZS.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-medium-voltage-joints-terminations-medium-voltage-switchgear-terminations-medium-voltage-switchgear-terminations.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 94px;\" width=\"842\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 832.386px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 832.386px;\"><span data-contrast=\"none\">Pre-engineered&nbsp;kit</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 832.386px;\"><span data-contrast=\"none\">Suitable for crimp&nbsp;and&nbsp;mechanical type connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 832.386px;\"><span data-contrast=\"none\">Available in LSR and EPDM variants</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 832.386px;\"><span data-contrast=\"none\">Tested as per National&nbsp;and&nbsp;International Standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p>Test Particulars&nbsp;</p>\r\n</th>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p>Inner Cone (RPIT)&nbsp;</p>\r\n</th>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p>Outer Cone (RSTI/ELBC)&nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"0\">&nbsp;</th>\r\n<th data-celllook=\"0\">\r\n<p>Size 2&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>Size 3&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>24 kV&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>36 kV&nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Voltage (U0/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>19/33 (36) kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>19/33 (36) kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>12.7/22 (24) kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>19/33 (36) kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Stress Control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric / Refractive&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric / Refractive&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Continuous&nbsp;Current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>800 Amps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1250 Amps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>800 /1250 Amps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>800 / 1250 Amps&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Basic Impulse Level&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>170&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>170&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>125&nbsp;kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>170&nbsp;kVp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable Cross section&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Upto&nbsp;300&nbsp;sqmm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Upto&nbsp;800&nbsp;sum&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Upto&nbsp;800&nbsp;sqmm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Upto&nbsp;800&nbsp;sqmm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Partial&nbsp;Discharge at 1.73 U0&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Less than 10&nbsp;pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Test Point&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Optional&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Optional&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Integrated with plug&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Integrated with plug&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>AC HV test for 5 minutes&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>85 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>85 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>57 kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>85 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Connection Technology&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Wedge Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Wedge Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical / Crimp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical / Crimp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"5\" data-celllook=\"0\">\r\n<p><strong> Plug&nbsp;In&nbsp;Termination (Inner &amp; Outer Cones) System 36kV for GIS Switchgear </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 99, NULL, 0, NULL, 'Medium Voltage Switchgear Terminations | Medium Voltage Joints & Terminations - Raychem RPG', 'Medium Voltage screened separable connectors for switchgears. Raychem developed screened separable connectors for switchgears which are compact and space saving, having high degree of reliability and safety.  View more information online!', 1, 272, '2021-08-27 12:35:42', '2022-01-05 13:13:00');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(274, 'Heat Shrink High Voltage Terminations', 'reliable-connections/power-cable-accessories/high-voltage-joints-terminations/heat-shrink-high-voltage-terminations/heat-shrink-high-voltage-terminations', 'HV Heat Shrink Termination. Heat shrink high voltage terminations upto 72 kV are in service for over 40 years. They are suitable for installation in all climates, environments and polluted areas. Heat shrink high voltage termination comply to IEC 60840.', 'otO5tMlMimBtpotjlvm8VOq21ZaBgX.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-high-voltage-joints-terminations-heat-shrink-high-voltage-terminations-heat-shrink-high-voltage-terminations.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 200px;\" width=\"719\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 709.389px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Heat-shrinkable stress control sleeves</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Non-tracking, heat-shrinkable outer insulation</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Water&nbsp;and corrosion-resistant</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Different creepage distances available</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Suitable for compression and mechanical lugs</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Suitable for wide range of connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">No oil or compound filling</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 709.389px;\"><span data-contrast=\"auto\">Tested under International standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Specifications </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>IEC 60840&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Nominal System Voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>66kV Phase to Phase&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Highest System Voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>72.5kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impulse Voltage&nbsp;at 95 to 1000C temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>325kV (Peak)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 Hz.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>AC High Voltage&nbsp;withstand test&nbsp;15&nbsp;min dry&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>95 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge Test at Ambient&nbsp;</p>\r\n<p>Pre-Stressed at 1.75U0&nbsp;(67kV) 10sec&nbsp;</p>\r\n<p>Measured at 1.5U0&nbsp;(57kV)&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Less than 5pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge Test at Elevated (95-1000C)&nbsp;&nbsp;</p>\r\n<p>Pre-Stressed at 1.75U0&nbsp;(67kV) 10sec&nbsp;</p>\r\n<p>Measured at 1.5U0&nbsp;(57kV)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Less than 5pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"7\" data-celllook=\"4369\">\r\n<p>9&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Voltage Test&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"1\" data-aria-level=\"1\">Total Duration of one cycle&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>24hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"2\" data-aria-level=\"1\">Duration of Heating period&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>8hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"3\" data-aria-level=\"1\">Duration of natural cooling period&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>16hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"4\" data-aria-level=\"1\">Temp. of conductor during heating&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>95 to 1000C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"5\" data-aria-level=\"1\">AC voltage applied during test&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>76kV&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"6\" data-aria-level=\"1\">No. of cycles&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>20&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Short Circuit Current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Same as Cable size subject to max. Conductor temperature of 250oC.&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Creepage (outdoor)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2300mm min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>12&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Mechanical connectors (if ordered separately for terminations)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>13&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Method of Stress Control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>14&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing&rsquo;s &amp; Molded parts&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>15&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Non-Tracking material&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Confirming as per ASTM D-2303&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10 kV/mm min&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Heat Shrink type Indoor/Outdoor Termination and Straight Through Joint for 66kV&nbsp;(E) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 100, NULL, 0, NULL, 'Heat Shrink High Voltage Terminations | High Voltage Joints & Terminations - Raychem RPG', 'HV Heat Shrink Termination. Heat shrink high voltage terminations upto 72 kV are in service for over 40 years. They are suitable for installation in all climates, environments and polluted areas. View more information online!', 1, 273, '2021-08-27 12:36:08', '2022-01-05 13:40:36'),
(275, 'Heat Shrink High Voltage Joints', 'reliable-connections/power-cable-accessories/high-voltage-joints-terminations/heat-shrink-high-voltage-joints/heat-shrink-high-voltage-joints', 'HV Heat Shrink Joint. Polymeric insulated cables of various designs can be adapted with respect to shielding and metal sheath. Raychem heat shrink accessories have been used by utilities and industrial companies around the world for over 40 years. The ongoing ﬁeld experience makes Raychem a leader in materials science and technology for high voltage applications. The materials used in TE Connectivity Raychem cable accessories are extensively optimized with respect to product design, function, manufacturing and expected service environment.', '40My8hyH6pRH7aFykVPmkAJ4wlTXkU.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-high-voltage-joints-terminations-heat-shrink-high-voltage-joints-heat-shrink-high-voltage-joints.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 200px;\" width=\"824\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 814.389px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Heat-shrinkable stress control sleeves</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Torque-controlled connector</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Water and corrosion-resistant</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Joint ﬁts on all polymeric cable constructions</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Proven shield continuity concept</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Short cut-back dimension</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Cable size transition possible</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Unlimited shelf life under normal storage conditions</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Suitable for wide range of mechanical connectors</span></td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 814.389px;\"><span data-contrast=\"auto\">Tested under International standards</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Sr. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Particulars </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Specifications </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Applicable Standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>IEC 60840&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Nominal System Voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>66kV Phase to Phase&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Highest System Voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>72.5kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Impulse Voltage&nbsp;at 95 to 1000C temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>325kV (Peak)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>50 Hz.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>AC High Voltage&nbsp;withstand test&nbsp;15&nbsp;min dry&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>95 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>7&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge Test at Ambient&nbsp;</p>\r\n<p>Pre-Stressed at 1.75U0&nbsp;(67kV) 10sec&nbsp;</p>\r\n<p>Measured at 1.5U0&nbsp;(57kV)&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Less than 5pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Partial Discharge Test at Elevated (95-1000C)&nbsp;&nbsp;</p>\r\n<p>Pre-Stressed at 1.75U0&nbsp;(67kV) 10sec&nbsp;</p>\r\n<p>Measured at 1.5U0&nbsp;(57kV)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Less than 5pC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"7\" data-celllook=\"4369\">\r\n<p>9&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heating Cycle Voltage Test&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"1\" data-aria-level=\"1\">Total Duration of one cycle&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>24hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"2\" data-aria-level=\"1\">Duration of Heating period&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>8hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"3\" data-aria-level=\"1\">Duration of natural cooling period&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>16hr&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"4\" data-aria-level=\"1\">Temp. of conductor during heating&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>95 to 1000C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"5\" data-aria-level=\"1\">AC voltage applied during test&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>76kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<ol>\r\n<li data-leveltext=\"%1)\" data-font=\"Verdana\" data-listid=\"3\" data-aria-posinset=\"6\" data-aria-level=\"1\">No. of cycles&nbsp;</li>\r\n</ol>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>20&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>10&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Short Circuit Current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Same as&nbsp;cable size subject to max. Conductor temperature of 250oC&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>11&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Creepage (outdoor)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>2300mm min.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>12&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Accessories&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Mechanical connectors (if ordered separately for terminations)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>13&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Method of Stress Control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>14&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Tubing&rsquo;s &amp; Molded parts&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Heat Shrinkable type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>15&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Non-Tracking material&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>As per ASTM D-2303&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"4369\">\r\n<p>16&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Di-electric strength of insulating material&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10 kV/mm min&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Heat Shrink Type&nbsp;Indoor/Outdoor Termination and Straight Through Joint for 66kV (E)&nbsp; </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 101, NULL, 0, NULL, 'Heat Shrink High Voltage Joints | High Voltage Joints & Terminations - Raychem RPG', 'HV Heat Shrink Joint. Polymeric insulated cables of various designs can be adapted with respect to shielding and metal sheath. View more information online!', 1, 274, '2021-08-27 12:36:28', '2022-01-05 13:32:08'),
(276, 'Pre Moulded EHV Joints', 'reliable-connections/power-cable-accessories/extra-high-voltage-joints-terminations-66kv-245kv/pre-moulded-ehv-joints/pre-moulded-ehv-joints', 'Pre moulded design of Joints for voltages upto 245 kV. Available in Single/One piece design upto 245 kV and Three piece design for 145 kV. The silicone rubber joint body with integrated geometrical stress control, provides proven electrical functions. Joint components combine electrical performance, stress control and moisture sealing to provide important functions required for high voltage equipment.', '6e6QBzcooqY7v8SjSlvF8ZmmnnovqG.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-extra-high-voltage-joints-terminations-66kv-245kv-pre-moulded-ehv-joints-pre-moulded-ehv-joints.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\" data-celllook=\"0\">\r\n<p><strong> Single Piece Joint 72/145 kV/245 kV </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/66 (72)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over insulation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>37.86 - 75.20 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>37.86-96.80 mm&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>60.70-128.25 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over sheath&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 120 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 140 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 160 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable screen types&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. Cross section (Cu / Al)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 1200 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Approx. 1600 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 2500 mm&sup2;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Conductor connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of connection bolt&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum / Copper&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum / Copper&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum / Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. permissible dielectric stress&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Outer protection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of stress control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material main body&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Installation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Operation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +50 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +50 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +50 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Storage temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Three-Piece 145 kV Joint&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over insulation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>43 &ndash; 84 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over sheath&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>105 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable screen types&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. Cross section (Cu / Al)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Approx. 3000 mm&sup2;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Conductor connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of connection bolt&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium&nbsp;/ copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. permissible dielectric stress&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Outer protection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of stress control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material main body&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Installation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Operation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +50 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Storage temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"5\" data-celllook=\"0\">\r\n<p><strong> &nbsp;Single Piece&nbsp;Joint&nbsp;72/145 kV/245 kV </strong></p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Relevant standard </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong>   </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> IEC 60840 </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> IEC 60840 </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> IEC 62067 </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated voltage U0/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/66 (72)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage 1,2/50&mu;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1050&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>AC&nbsp;Voltage withstand test (15/30 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>90&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>190&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>254/318&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Partial discharge 1.5&nbsp;Uo&nbsp;kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>A&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short-circuit current (conductor) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short circuit current (sheath) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>As per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>As per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>As per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>DC&nbsp;Voltage test between metallic sheath/screen and earthed exterior&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Three-Piece 145 kV Joint&nbsp; </strong></p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Relevant standard </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong>   </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> IEC 60840 </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;Voltage&nbsp;Uo/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage 1,2/50&micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>AC&nbsp;Voltage withstand test (30 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>190&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>DC&nbsp;Voltage withstand (15 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>315&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short-circuit current (conductor)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short-circuit current (sheath) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>DC&nbsp;Voltage test between metallic sheath/screen and earthed exterior&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>25&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 102, NULL, 0, NULL, 'Pre Moulded EHV Joints - Raychem RPG', 'Pre Moulded EHV Joints.  View more information online!', 1, 275, '2021-08-27 12:37:00', '2022-01-06 04:55:10');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(277, 'EHV Outdoor Terminations', 'reliable-connections/power-cable-accessories/extra-high-voltage-joints-terminations-66kv-245kv/ehv-outdoor-termination/ehv-outdoor-termination', 'High Voltage Outdoor Terminations upto 245 kV - Dry type and Fluid filled type with Composite insulator including link boxes. Composite terminations for voltage classes up to 245 kV operate under severe environmental conditions. Composite housings with creepage lengths up to 31 mm/kV are available for the most common and extremely pollution levels, according to IEC 60815 standard.', '0He7SIwtZFqZmlH9vn4knEuMWP53BT.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-extra-high-voltage-joints-terminations-66kv-245kv-ehv-outdoor-termination-ehv-outdoor-termination.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\" data-celllook=\"0\">\r\n<p><strong> Oil filled 72/145/245 kV&nbsp; </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated Voltage&nbsp;kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/66 (72.5)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over insulation&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>38.87 to 96.80&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>38.87 - 96.80 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>62.33 - 128.25 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over sheath&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;120mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;140 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;160 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable screen type&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated Al. sheath, Copper wire, Copper tape, Lead sheath.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable Cross section (Al/Cu)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;1200 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;1600 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;2500 mm&sup2;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Conductor connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of connection bolt&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium/Copper&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium/Copper&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium/Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of insulator - outer surface&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Colour&nbsp;of insulator&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Grey&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Grey&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Grey&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of stress control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Stress cone&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulating liquid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Oil/Ester oil/Polyisobutlyene oil</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Oil/Ester oil/Polyisobutlyene oil</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone Oil/Ester oil/Polyisobutlyene oil</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Installation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Operation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> -55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> -55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Storage temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 &deg;C - +40 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Dry&nbsp;145kV </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over insulation&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>34 &ndash; 74 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over sheath&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;99 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable screen types&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. Cross section (Al/Cu)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1200 mm&sup2;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Conductor connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear head bolts)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of connection bolt&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of insulator - outer surface&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Profile of insulator&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Alternating sheds&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Colour&nbsp;of insulator&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Grey&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of stress control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Stress cone&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Prefabricated silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. permissible dielectric stress at core screen&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4&nbsp;kV/mm (at core screen of cable)&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulating liquid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>none&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of fittings&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>,</p>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p>&nbsp; <strong> Dry Flexible 145kV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. Cross section (Al/Cu)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1200 mm&sup2;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. XLPE Insulation diameter&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le; 78 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Connector style&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Crimping (with Aerial Lug)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Creepage distance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4590 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of body&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Silicone rubber&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Comply with&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC60840&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of stress control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Stress cone&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable Screen type&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Cu Wire/Lead sheath/CAS/Copper tape&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Grounding style&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical connection without solder&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Colour&nbsp;of insulator&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Grey&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"5\" data-celllook=\"0\">\r\n<p><strong> Oil filled 72/145/245 kV&nbsp; </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Relevant&nbsp;Standard&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 60840&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 60840&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 62067&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated voltage&nbsp;Uo/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/66 (72.5)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage 1.2/50&micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1050&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Power frequency voltage withstand dry (15/30&nbsp;min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>90&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>190&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>254/318&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Partial Discharge 1.5Uo (kV)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;Current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;Short&nbsp;Circuit&nbsp;Current (conductor) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;Short&nbsp;Circuit&nbsp;Current (sheath) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Creepage distance (min.)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>2250&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4500&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>7595&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Flash-over distance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>740&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1340&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> 2320&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Pollution level (IEC 60137; 1995, VDE 0674 Teil5)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> IV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Withstand voltage of support insulators (AC/DC)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10/20&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10/20&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10/20&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Dry 145 kV </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Relevant standard&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">&nbsp;</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 60840 / IEEE 48&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated voltage&nbsp;Uo/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage 1.2/50&micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Power frequency voltage withstand dry (1 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>310&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Power frequency voltage withstand wet (10 s)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>275&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>DC&nbsp;voltage&nbsp;withstand (15 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>355&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short-circuit current (conductor)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short-circuit current (sheath) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Total creepage distance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>4680&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Protected creepage distance (90&deg; shadow)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1820&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Flash-over distance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1320&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Withstand voltage of support insulators (AC/DC)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10/20&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Dry Flexible 145 kV: </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Relevant standard&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 60840&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated voltage&nbsp;Uo/U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Highest voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kVp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Power frequency voltage withstand dry (30 min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>190&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Current capacity&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> A&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Permissible short-circuit current 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 103, NULL, 1, NULL, 'EHV Outdoor Termination - Raychem RPG', 'High Voltage Outdoor termination upto 245 Kv-Dry and Composite Type including link boxes. Composite terminations for voltage classes up to 245 kV operate under severe environmental conditions. View more information online!', 1, 276, '2021-08-27 12:37:20', '2022-01-05 14:48:56'),
(278, 'GIS/Equipment Terminations', 'reliable-connections/power-cable-accessories/extra-high-voltage-joints-terminations-66kv-245kv/gisequipment-termination/gisequipment-termination', 'The dry compact GIS/Transformer termination for voltage classes up to 245 kV is designed to be installed in cable entry housings of gas-insulated switchgear (GIS)/Transformer.', 'BvG1a9fV2VuEMxBcs2pozKPTVAmAae.jpg', 2, NULL, NULL, '', NULL, 'product-catalog-reliable-connections-power-cable-accessories-extra-high-voltage-joints-terminations-66kv-245kv-gisequipment-termination-gisequipment-termination.pdf', 3, '', '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Operates in SF6 and insulating liquids like transformer oil</td>\r\n</tr>\r\n<tr>\r\n<td>Corona shield at top of Transformer termination provides shielding for terminal</td>\r\n</tr>\r\n<tr>\r\n<td>Dry interfaces, no oil-filling</td>\r\n</tr>\r\n<tr>\r\n<td>Pressure-tight resin housing</td>\r\n</tr>\r\n<tr>\r\n<td>Prefabricated and factory-tested silicone-rubber stress cone</td>\r\n</tr>\r\n<tr>\r\n<td>Torque-controlled or wedge-type multi-contact conductor bolt</td>\r\n</tr>\r\n<tr>\r\n<td>Insulated cable gland for sectionalization</td>\r\n</tr>\r\n<tr>\r\n<td>Type tested according to IEC 60840&nbsp;and&nbsp;IEC 62067 standards</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"4\" data-celllook=\"0\">\r\n<p><strong> Design Data </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated&nbsp;kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/69 (72.5)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over insulation range&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>38.40mm - 77.4 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>38.40 mm - 95.10 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>64.0 -123.1 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Diameter over sheath&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;120 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;140 mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;160 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cable screen type&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated Al. sheath, Copper wire, Copper tape, Lead sheath, etc.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated Al. sheath, Copper wire, Copper tape, Lead sheath,&nbsp;etc.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Max. Cross section (Al/Cu)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;1200 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;1600 mm&sup2;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;2500 mm&sup2;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Conductor connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical (shear off bolts)/Wedge connector&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of Housing&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Epoxy Resin&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Epoxy Resin&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Epoxy resin&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Material of connection bolt&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum Alloy&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum Alloy&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> Aluminum Alloy&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Method of Stress Control&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Geometric&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Type of Stress Cone&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-moulded&nbsp;silicone rubber&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Corona Shield (only for Transformer Termination)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium&nbsp;Alloy&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminium&nbsp;Alloy&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Aluminum Alloy&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Installation temperature [&deg;C]&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Operation temperature&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>-55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> -55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> -55 &deg;C - +55 &deg;C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Storage temperature [&deg;C]&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>0 to +40&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p>Relevant standard&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>IEC 60840&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>IEC 60840&nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p>IEC 62067&nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated voltage U0 /U (Um)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36/69 (72.5)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>76/132 (145)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>127/220 (245)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated frequency&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Hz&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>50&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Lightening impulse voltage 1.2/50&micro;s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>350&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>650&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1050&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>AC Voltage withstand test (15/30&nbsp;min)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>90&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>90&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> 254/318&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Partial discharge 1.5Uo (kV)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>pC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> &le;5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&le;5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p> as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short circuit current&nbsp;conductor) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated short circuit current (sheath) 1s&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>kA&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>as per cable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Creepage distance&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>254&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>410&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>475&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"5\" data-celllook=\"0\">\r\n<p><strong> Electrical Data for&nbsp;72/145/245 kV&nbsp;GIS / Equipment Extra High Voltage Termination </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 104, NULL, 0, NULL, 'Gisequipment Termination - Raychem RPG', 'The dry compact switchgear termination for voltage classes up to 245 kV is designed to be installed in cable entry housings of gas-insulated switchgear (GIS).  View more information online!', 1, 277, '2021-08-27 12:37:41', '2022-01-05 15:15:08'),
(279, 'Accessories', 'reliable-connections/power-cable-accessories/accessories/accessories', 'Add ons for Installation and Repairs', 'mSaaY3QSukNDOgOgJ1V34yJVoL4mJm.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-power-cable-accessories-accessories-accessories.pdf', 3, '', '<table class=\"col-12 table\" width=\"875\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\"><strong> Mechanical Connector </strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Raychem&rsquo;s mechanical connectors and lugs are designed for use in low and medium voltage applications up to 42 kV. Customized connectors&nbsp;suitable for HV and EHV are available and&nbsp;form&nbsp;part of supplied accessories. All products consist of high tensile&nbsp;aluminium&nbsp;tin-plated body and shear-head bolts. Made of special&nbsp;aluminium&nbsp;alloy, new patented shear off bolts&nbsp;is&nbsp;irremovable once their heads have been sheared off. The internal surface of conductor holes&nbsp;is&nbsp;grooved. Lugs are suitable for outdoor and indoor applications and available with different palm hole sizes. These connectors comply to IEC 61238-1 Class A standard.</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" width=\"876\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">&nbsp; <strong> Cable Repair Sleeves </strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Heat-shrinkable wraparound sleeves are a fast, versatile and permanent method of repair for damaged cable outer sheaths. Upon application of heat, the sleeve shrinks and adhesive melts and bonds to the cable sheath, creating a permanent seal against moisture entry into the cable. Wraparound sleeves are useful for repairs to cable outer sheath where it is not possible to use tubular sleeves.&nbsp;</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" width=\"841\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\"><strong> HV Installation Toolbox </strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>\r\n<p>High Voltage Installation Toolbox includes all necessary tools for installing Raychem HV cable accessories up to&nbsp;245kV.&nbsp;With this comprehensive range of tools,&nbsp;you will always find the right tool for the job. From simple standard tools to special high voltage tools, the installation toolbox offers outstanding quality for fast and reliable installation. All tools are field tested and chosen by skilled installers.</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" width=\"876\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\"><strong> Cable End Caps </strong> &nbsp;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>On the inside walls coated with hot-melt adhesive, heat-shrinkable end caps are used to seal and protect the ends of plastic, paper and rubber insulated cables during storage, transport and cable laying.</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" width=\"893\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\"><strong> Zero Halogen &amp; Flame Retardant Tubing </strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>\r\n<p>The new&nbsp;low fire hazard material&nbsp;is&nbsp;developed using latest polymer technology to provide low smoke, low toxicity and low acid gas generation while being highly flame retardant and having low calorific value.&nbsp;</p>\r\n<ul>\r\n<li data-leveltext=\"\" data-font=\"Symbol\" data-listid=\"1\" data-aria-posinset=\"1\" data-aria-level=\"1\">ZCSM tubing is halogen-free and flame-retardant. A range of established tests, such as flame propagation tests, limiting oxygen index and temperature index&nbsp;are&nbsp;carried out to assess flame retardation properties of this material.&nbsp;</li>\r\n<li>&nbsp;Corrosion damage depends on the amount of acid gases generated when material is burned and levels&nbsp;of halogen and other acidic components in the insulation material. Pyrolytic analyses show only trace quantities of these substances in the ZCSM tubing. The low toxicity index rating derived from measurement of&nbsp;these&nbsp;and further&nbsp;combustion products provide additional evidence of material&rsquo;s suitability for meeting special requirements of this kind.&nbsp;</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, NULL, NULL, '', 6, 93, NULL, 0, NULL, 'Accessories | Power Cable Accessories - Raychem RPG', 'Add ons for Installation and Repairs. View more information online!', 1, 279, '2021-08-27 12:38:17', '2022-01-06 05:17:18'),
(280, 'Clamps & Connectors', 'reliable-connections/high-voltage-connection-system-hvcs/clamps-connectors', 'Terminal Connectors - Rigid type,  Expansion type, T-Connectors, P G Clamps, Inter Connector, Corona Bell, Welding Sleeve, Rigid Spacers, Flexible Spacers, Elbow Connector, Junction Connector, Support Connector. Terminal Connectors used in sub-stations can be mounted on different equipment like Isolator (Disconnector), Transformer, CT, CVT, BPI, LA, etc.. for different IPS Alu. Tube sizes and conductor  configrations (Single/Twin/Triple/Quad/Hexa/Octa). The connectors are tested as per IS: 5561 and Spacers as per IS: 10162 Standards.  Clamps and Connectors are made of Aluminium Casting (LM6/LM25 as per BS 1490 or Gr 4600 as per IS: 617) suitable for different voltage ratings upto 1200kV for conductor configuration in Single/Twin/Triple/Quad/Hexa of all conductor / IPS tube sizes and sub-conductor spacings.', 'XJi9z0l4tIGBfimiZnNGXWz6FVQGtR.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-high-voltage-connection-system-hvcs-clamps-connectors.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"1\" rowspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Si. No. </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"1\" rowspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Clamps &amp; Connectors </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"1\" rowspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Type </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Application </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Main Side </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Tap Side </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Terminal Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid / Expansion&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Equipment Pad /&nbsp;Equipment Stud /&nbsp;&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor / IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>T Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor / IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor / IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Inter Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor / IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor / IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>P G Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Spacer&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid / Flexible&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Elbow Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Adjustable&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>7&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Corona Bell&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Welding Sleeve&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Rigid&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IPS Alu. Tube&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> SL. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Description </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Unit </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Value Guaranteed by the Bidder </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Voltage Class&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>33 / 66 / 110 / 132 / 220 / 400 / 765 / 800&nbsp;/ 1200&nbsp;kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> 2. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">\r\n<p>Reference standards&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Connectors: IS 5561&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Spacers: IS 10162&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> 3. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">\r\n<p>Type of&nbsp;Clamps &amp; Connectors&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Bolted Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>Rigid / Flexible&nbsp;/ Expansion / Adjustable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 4. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of&nbsp;Spacers&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Alu. Alloy: Gr.4600 as per IS: 617&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 5. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Fasteners&nbsp;</p>\r\n</td>\r\n<td colspan=\"2\" data-celllook=\"69905\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Bolts, Nuts &amp; Plain Washers&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Hot Dip Galvanized Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> b) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Spring Washers&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Electro Galvanized Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 6. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Method of casting&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Gravity&nbsp;die&nbsp;casting &amp; Gravity sand casting&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 7. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Bi-metallic connection&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>2 mm&nbsp;Thk.&nbsp;Cu-Alu. Bi-metallic Sleeves&nbsp;will be provided&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 8. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Short time current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>50 kA for 1 Sec&nbsp;(upto&nbsp;400kV)&nbsp;</p>\r\n<p>63kA for 1 Sec (765kV)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 9. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Temperature rise limit when carrying Normal current&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>45&ordm;C rise over&nbsp;40&deg;C ambient when carrying rated current for Equipment Connectors.&nbsp;</p>\r\n<p>Temperature rise on&nbsp;connector equal&nbsp;to or less than that of conductor or bus bar tube when carrying rated current at specified ambient temperature.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Corona Extinction voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>765/800 kV - 508 kV (rms)&nbsp;</p>\r\n<p>400 kV &ndash; 320 kV (rms)&nbsp;</p>\r\n<p>220 kV &ndash; 156 kV (rms)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 11. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Radio Interference Voltage&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>765/800 kV - Less than 2500 &micro;V at 508 kV (rms)&nbsp;</p>\r\n<p>400 kV - Less than 1000 &micro;V at 320 kV (rms)&nbsp;</p>\r\n<p>220 kV - Less than 1000 &micro;V at 156 kV (rms)&nbsp;</p>\r\n<p>132 kV - Less than 500 &micro;V at 92 kV (rms)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 12. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Packing details&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Standard&nbsp;Wooden&nbsp;Box&nbsp;Packing&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 87, NULL, 0, NULL, 'Clamps Connectors | High Voltage Connection System (HVCS) - Raychem RPG', 'Clamps and Connectors are made of Aluminium Casting (LM6/LM25 as per BS 1490 or Gr 4600 as per IS: 617) suitable for different voltage ratings', 1, 280, '2021-08-27 12:38:54', '2022-01-06 05:25:44');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(281, 'String Hardware', 'reliable-connections/high-voltage-connection-system-hvcs/string-hardware', 'Single Suspension, Double Suspension, Single Tension, Double Tension, Earthwire Tension Clamp Assembly, PG Clamp, T-Connector, Pad Clamp, Cleat Clamp. Suspension/Tension String Hardware used in sub-stations can be mounted on towers or structures available in sub-stations as per conductor  configrations (Single/Twin/Triple/Quad/Hexa/Octa). String Hardware components conform to IS: 2486 Standard.  \r\n\r\nString Hardware and Earth Wire Accessories for sub-stations are manufactured as per IS: 2486 and suitable for different voltage ratings and conductor configurations (Single/Twin/Triple/Quad/Hexa). String hardware products are approved by different utilities all over India.', 'vDiBwSeyVwpHbjY5w71Hov17noz0U5.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-high-voltage-connection-system-hvcs-string-hardware.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Si. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> String Hardware </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Anchoring </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Conductor Configuration </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Type of Clamp </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad&nbsp;/&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Through&nbsp;/ Drop Type Suspension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Double Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Double Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Through / Drop Type Suspension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single&nbsp;V Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Double Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Through / Drop Type Suspension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Double V Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Double Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Through / Drop Type Suspension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single&nbsp;Tension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bolted&nbsp;Type&nbsp;Tension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Double&nbsp;Tension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Double Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bolted Type Tension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>7&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Triple&nbsp;Tension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single /&nbsp;Triple Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Single / Twin / Triple / Quad /&nbsp;Hexa&nbsp;/ Octa&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bolted Type Tension Clamp&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> SL. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Description </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Unit </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"4\" data-celllook=\"4369\">\r\n<p><strong> Value Guaranteed by the Bidder </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Bolted type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 2. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Reference standards&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>IS 2486&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 3. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Voltage Class&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>33 / 110 /&nbsp;132 / 220 / 400 / 765 kV&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 4. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Variants&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Single Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Double Suspension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Single Tension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Double&nbsp;Tension&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 5. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Single Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Double Anchoring (Spacing&nbsp;&ndash;&nbsp;450&nbsp;/ 330&nbsp;mm)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Single Anchoring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Double Anchoring (Spacing&nbsp;&ndash;&nbsp;450&nbsp;/ 330&nbsp;mm)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 6. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Insulator Coupling&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>24/20/16&nbsp;mm Ball &amp; Socket - IS: 2486 (Part-II)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 7. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p><strong> Material: </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"5\" data-celllook=\"69905\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Ferrous Parts&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Mild Steel / Forged Steel (Hot Dip Galvanized)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> b) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Bolts, Nuts &amp; Plain Washers&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Hot Dip Galvanized Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> c) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Spring Washers&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Electro Galvanized Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> d) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>Split Pin / R-clip&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Stainless Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> e) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Suspension (Through/Drop) Clamps/&nbsp;Bolted Type Tension Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Alu. Alloy: Gr.4600 as per IS: 617&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 8. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p><strong> Ultimate Strength: </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"5\" data-celllook=\"69905\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Complete Assembly&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> b) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Anchor Shackle&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> c) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>H. H. Ball Link/Ball Link&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> d) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Socket Clevis&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> e) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Clevis&nbsp;Clevis&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> f) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Strap&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> g) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Clevis Eye&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> h) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Twisted Eye Link/Eye Link&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> i) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Yoke Plate&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>120 / 210&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> j) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Turn Buckle (Clevis Eye Type) / Turn Buckle (Clevis&nbsp;Clevis&nbsp;Type)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> k) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Arcing Horn / Grading Ring / Corona Control Ring&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>1.5&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> l) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Drop/Through Type Susp. Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> m) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Bolted Type Tension Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>KN&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>70&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 9. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Sub-conductor Spacing&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>mm&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>250 / 450&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> 10. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"4369\">\r\n<p>Suitable for Conductor&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"2\" data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Twin / Quad&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>ACSR Moose / ACSR&nbsp;Bersimis&nbsp;/ AAC Bull&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 11. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"6\" data-celllook=\"4369\">\r\n<p><strong> Earth&nbsp;Wire Accessories: </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Bolted type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> b) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>MCI / Mild Steel (HDG)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 12. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Min. No. of dips in standard test ferrous parts can withstand&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Spring Washer: 3 dips&nbsp;</p>\r\n<p>Fasteners: 4 dips&nbsp;</p>\r\n<p>All other ferrous parts: 6 dips&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 13. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Packing details&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td colspan=\"4\" data-celllook=\"69905\">\r\n<p>Standard&nbsp;Wooden Box Packing&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 87, NULL, 0, NULL, 'String Hardware | High Voltage Connection System (HVCS) - Raychem RPG', 'String Hardware and Earth Wire Accessories for sub-stations are manufactured as per IS: 2486 and suitable for different voltage ratings and conductor configurations', 1, 281, '2021-08-27 12:39:14', '2022-01-06 05:41:23'),
(282, 'MCS (Modular Cantilever System)', 'reliable-connections/railway-catenary-ohe-system/mcs-modular-cantilever-system', 'MCS for 25 KV high speed requirements - 20 KN and 24 KN. Raychem Indigenous Modular Cantilever System is designed to support the assembly of overhead power transmission wires — i.e., catenary (1000/1200 kgf tension), contact (1000/1200 kgf tension), and droppers — to transfer the overall bending, transverse, and vertical loads to the mast via insulators. The quintessential cantilever is lightweight and robust enough to support the current-carrying assembly for semi-high speed and high-speed trains up to 250 km/h. In addition to these functional requirements, ease of maintenance, transportation, handling, and aesthetics have been considered.', 'KseP4tztIbZS7h1BsxvpnC9xJcAuHq.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-mcs-modular-cantilever-system.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 17px;\" width=\"813\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 803.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 803.395px;\"><span class=\"TextRun SCXW31918454 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW31918454 BCX0\">Comply with l</span><span class=\"NormalTextRun SCXW31918454 BCX0\">atest&nbsp;</span></span><span class=\"TextRun SCXW31918454 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW31918454 BCX0\">RDSO Specification&nbsp;</span><span class=\"NormalTextRun SCXW31918454 BCX0\">N</span><span class=\"NormalTextRun SCXW31918454 BCX0\">o</span><span class=\"NormalTextRun SCXW31918454 BCX0\">.</span><span class=\"NormalTextRun SCXW31918454 BCX0\">&nbsp;</span></span><span class=\"TextRun SCXW31918454 BCX0\" lang=\"IT-IT\" xml:lang=\"IT-IT\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW31918454 BCX0\">TI/SPC/OHE/MCS/0150(08/2015)</span></span><span class=\"EOP SCXW31918454 BCX0\" data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:6,&quot;335551620&quot;:6,&quot;335559731&quot;:720,&quot;335559739&quot;:160,&quot;335559740&quot;:240}\">&nbsp;</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th width=\"66\">\r\n<p><strong> Sr No </strong></p>\r\n</th>\r\n<th width=\"210\">\r\n<p><strong> Parameter </strong></p>\r\n</th>\r\n<th width=\"108\">\r\n<p><strong> Value </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td width=\"66\">\r\n<p>1.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Line Tension</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>20/24/30 kN</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"66\">\r\n<p>2.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Train Speed</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>200 Kmph</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"66\">\r\n<p>3.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Span Length</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>&le; 72 m</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"66\">\r\n<p>4.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Stagger</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>Upto 0.3m</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"66\">\r\n<p>5.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Encumbrance</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>Max. 1.4 m</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"66\">\r\n<p>6.</p>\r\n</td>\r\n<td width=\"210\">\r\n<p>Implantation/Setting Distance</p>\r\n</td>\r\n<td width=\"108\">\r\n<p>2.36 &ndash; 3.6 m</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'MCS Modular Cantilever System | Railway Catenary (OHE) System - Raychem RPG', 'MCS for 25KV high speed requirements - 20KN and 24 KN. Indigenous MCS are designed to support assembly of overhead power transmission wires — i.e., catenary (1000/1200 kgf tension), contact (1000/1200 kgf tension) and droppers to transfer the overall bending, transverse, and vertical loads to the mast via insulators.', 1, 282, '2021-08-27 12:39:44', '2022-01-24 10:41:03'),
(283, 'ATD (Auto Tensioning Device)', 'reliable-connections/railway-catenary-ohe-system/atd-auto-tensioning-device', 'Light weight spring ATD for 25 KV line - 20KN and 24 KN. In an electric rail system, power is supplied by overhead lines that run along the entire length of the railway tracks. This power is transferred to the train by means of the pantograph which is a current collector mounted on top of the locomotive.  ATD  provides a mechanism for automatic tensioning of  OHE lines to ensure smooth collection of current by moving pantograph. Tensioning is needed on the contact lines due to variation in their lengths. Contact lines are primarily made from copper-based alloys prone to expansion and contraction due to variations in atmospheric temperatures. The absence of tensioning causes overhead lines to sag or tighten, leading to pantograph entanglement or snapping of overhead equipment (OHE) lines. We have introduced an indigenous spring ATD which is very light in weight and can cater to the load requirement upto 30 KN.', 'Pnk6Zu7IgmPRuvCS6oNsDFIKavDUce.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-atd-auto-tensioning-device.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 29px;\" width=\"642\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 632.386px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 632.386px;\"><span class=\"TextRun SCXW211110103 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW211110103 BCX0\">Compl</span><span class=\"NormalTextRun SCXW211110103 BCX0\">ies</span><span class=\"NormalTextRun SCXW211110103 BCX0\">&nbsp;</span><span class=\"NormalTextRun SCXW211110103 BCX0\">with</span><span class=\"NormalTextRun SCXW211110103 BCX0\">&nbsp;</span></span><span class=\"TextRun SCXW211110103 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW211110103 BCX0\">RDSO Specification</span><span class=\"NormalTextRun SCXW211110103 BCX0\">&nbsp;No.</span><span class=\"NormalTextRun SCXW211110103 BCX0\">&nbsp;</span></span><span class=\"TextRun SCXW211110103 BCX0\" lang=\"EN-IN\" xml:lang=\"EN-IN\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW211110103 BCX0\">TI/SPC/OHE/SPRATD/0110(03/2012)</span></span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p><span class=\"EOP SCXW211110103 BCX0\" data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:6,&quot;335551620&quot;:6,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Sr No </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Parameter </strong></p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Value </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Line Tension&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1000/1200/1500&nbsp;kgf&nbsp;in each overhead line (overall 2000/2400/3000&nbsp;kgf)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>2.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Max Tensioning Length&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Upto&nbsp;1500 m&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Working&nbsp;temperature difference (&Delta;T)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>65&nbsp;⁰C&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>4.&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Weight&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>&lt; 300 Kg</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'ATD Auto Tensioning Device | Railway Catenary (OHE) System - Raychem RPG', 'Light weight spring ATD for 25 KV line - 20KN and 24 KN. In an electric rail system, power is supplied by overhead lines that run along the entire length of the railway tracks.', 1, 283, '2021-08-27 12:40:09', '2022-01-06 05:46:33'),
(284, 'SNS (Short Neutral Section)', 'reliable-connections/railway-catenary-ohe-system/sns-short-neutral-section', 'Short Neutral Section (PTFE) for 25 KV line, The utility power supply system expects equal loading on all phases. Traction power system works on single phase 25kV traction system. It now becomes important to use all the three phases equally and convert them into one phase traction supply.  This is achieved by feeding single phase supply to the adjacent traction substation which is separated by a neutral section. Each feed covers a distance of about 30-40Km feeding all the trains in that zone.\r\nShort Neutral sections are dead zones in the overhead line, used for isolating or separating different sections of the overhead electricity transmission line &also to provide smooth transition of pantograph from one section to another. To ensure strong Electrification drive, wear and tear nature of existing PTFE SNS needs a complete relook and design. Raychem RPG has introduced indigenous Short Neutral section for 25 KV line which is a moving roller-based technology and also, an alternative retrofit system for easy replacement of linings. A system which can eliminate the periodic maintenance and servicing issues.', '1Ei7YHJ3NnfF2YluhVZqAvFOczWSqw.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-sns-short-neutral-section.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 46px;\" width=\"681\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 671.392px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 671.392px;\"><span class=\"TextRun SCXW171123026 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW171123026 BCX0\">Compl</span><span class=\"NormalTextRun SCXW171123026 BCX0\">ies t</span><span class=\"NormalTextRun SCXW171123026 BCX0\">o&nbsp;</span></span><span class=\"TextRun SCXW171123026 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW171123026 BCX0\">RDSO Specification</span><span class=\"NormalTextRun SCXW171123026 BCX0\">&nbsp;No.</span></span><span class=\"TextRun SCXW171123026 BCX0\" lang=\"EN-US\" xml:lang=\"EN-US\" data-contrast=\"auto\"><span class=\"NormalTextRun SCXW171123026 BCX0\">&nbsp;TI/SPC/OHE/SNS/0000(Rev.1)</span></span><span class=\"EOP SCXW171123026 BCX0\" data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:6,&quot;335551620&quot;:6,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" width=\"552\">\r\n<thead>\r\n<tr>\r\n<th width=\"67\">\r\n<p><strong> Sr No </strong></p>\r\n</th>\r\n<th width=\"341\">\r\n<p><strong> Catenary Wire </strong></p>\r\n</th>\r\n<th width=\"144\">\r\n<p><strong> Contact Wire </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td width=\"67\">\r\n<p>1</p>\r\n</td>\r\n<td width=\"341\">\r\n<p>19/2.10 mm, 65 mm <sup> 2 </sup> cadmium copper</p>\r\n</td>\r\n<td width=\"144\">\r\n<p>107 mm <sup> 2 </sup></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"67\">\r\n<p>2</p>\r\n</td>\r\n<td width=\"341\">\r\n<p>19/2.10 mm, 65 mm <sup> 2 </sup> cadmium copper</p>\r\n</td>\r\n<td width=\"144\">\r\n<p>150 mm <sup> 2 </sup></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"67\">\r\n<p>3</p>\r\n</td>\r\n<td width=\"341\">\r\n<p>19/2.79 mm, 65 mm <sup> 2 </sup> aluminum alloy</p>\r\n</td>\r\n<td width=\"144\">\r\n<p>107 mm <sup> 2 </sup></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"67\">\r\n<p>4</p>\r\n</td>\r\n<td width=\"341\">\r\n<p>37/2.10 mm, 125 mm <sup> 2 </sup> cadmium copper</p>\r\n</td>\r\n<td width=\"144\">\r\n<p>150 mm <sup> 2 </sup></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"67\">\r\n<p>5</p>\r\n</td>\r\n<td width=\"341\">\r\n<p>37/2.92 mm, 242 mm <sup> 2 </sup> cadmium copper</p>\r\n</td>\r\n<td width=\"144\">\r\n<p>193 mm <sup> 2 </sup></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"3\" width=\"67\">\r\n<p>Suitable for different sizes of contact and catenary wires as given in table</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"3\" width=\"72\">\r\n<p><strong> Design Parameters </strong></p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th width=\"72\">\r\n<p><strong> Sr No </strong></p>\r\n</th>\r\n<th width=\"336\">\r\n<p><strong> Parameters </strong></p>\r\n</th>\r\n<th width=\"127\">\r\n<p><strong> Value </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td width=\"72\">\r\n<p>1.</p>\r\n</td>\r\n<td width=\"336\">\r\n<p>Locomotive Speed</p>\r\n</td>\r\n<td width=\"127\">\r\n<p>200 Kmph</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"72\">\r\n<p>2.</p>\r\n</td>\r\n<td width=\"336\">\r\n<p>Power Frequency Voltage of Contact wire Insulator</p>\r\n</td>\r\n<td width=\"127\">\r\n<p>250 kV</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"72\">\r\n<p>3.</p>\r\n</td>\r\n<td width=\"336\">\r\n<p>Impulse Voltage of Contact wire Insulator</p>\r\n</td>\r\n<td width=\"127\">\r\n<p>500 kV</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"72\">\r\n<p>4.</p>\r\n</td>\r\n<td width=\"336\">\r\n<p>Creepage Distance of contact wire insulator</p>\r\n</td>\r\n<td width=\"127\">\r\n<p>Approx. 3200 mm</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td width=\"72\">\r\n<p>5.</p>\r\n</td>\r\n<td width=\"336\">\r\n<p>Clearance</p>\r\n</td>\r\n<td width=\"127\">\r\n<p>Approx. 1000 mm</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'SNS Short Neutral Section | Railway Catenary (OHE) System - Raychem RPG', 'Short Neutral Section (PTFE) for 25 KV line, Utility power supply system expects equal loading on all phases. Traction power system works on single phase 25kV traction system, and it is imperative to use all the three phases equally and convert them into one phase traction supply.', 1, 284, '2021-08-27 12:40:36', '2022-01-06 10:24:22'),
(285, 'Railway Insulators', 'reliable-connections/railway-catenary-ohe-system/railway-insulators', 'Composite Insulators for 25 KV line Stay, Bracket and 9Tonnes. Polymeric Insulator combines mechanical strength with excellent pollution-free performance. High tensile strength of glass fibre combined with  HV shedded profile produces rugged, lightweight tension insulators for overhead line applications. Railway Polymeric Insulator combines mechanical strength with excellent pollution performance. High tensile strength of the glass fibre combined with HV shedded profile, makes it a rugged and lightweight tension insulator for overhead line applications.', 'rqBL7amFN3jpZoX7DdL9HNt4ywuaCk.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-railway-insulators.pdf', 3, '', '<table class=\"col-12 table\" style=\"height: 122px;\" width=\"618\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 608.395px;\" scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 608.395px;\">Lightweight, ease of installation and reduced transport costs</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 608.395px;\">Vandal and break resistant</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 608.395px;\">High tracking and erosion resistance</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 608.395px;\">Excellent performance under polluted conditions</td>\r\n</tr>\r\n<tr>\r\n<td>Reduced maintenance costs</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 608.395px;\">Maximum mechanical strength without damaging fibre glass rod</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p>&nbsp;</p>\r\n<p>&nbsp;</p>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 612px; width: 819.898px;\">\r\n<thead>\r\n<tr style=\"height: 30px;\">\r\n<th style=\"width: 251px; height: 30px; text-align: left;\"><span style=\"font-size: 12pt;\"><strong>General characteristics:</strong></span></th>\r\n<th style=\"width: 56px; height: 30px; text-align: center;\"><span style=\"font-size: 12pt;\"><strong>Unit&nbsp;</strong></span></th>\r\n<th style=\"width: 205px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;9 Tonne</strong></span></th>\r\n<th style=\"width: 127px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>Bracket Tube</strong></span></th>\r\n<th style=\"width: 146.898px; height: 30px;\"><span style=\"font-size: 12pt;\"><strong>Stay Arm Tube</strong></span></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr style=\"height: 8.39062px;\">\r\n<td style=\"width: 251px; height: 8.39062px;\">Applicable standard</td>\r\n<td style=\"width: 56px; height: 8.39062px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 8.39062px; text-align: center;\" colspan=\"3\">\r\n<p>IEC 61109, IEC 62217 &amp; RDSO specification No T1/SPC/OHE/INSCOM/1071, Rev.1</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Material of FRP rod</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Boron free, ECR grade</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Material of housing</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Silicone, Grey</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\" colspan=\"5\"><span style=\"font-size: 12pt;\"><strong>Mechanical Characteristics:</strong></span>&nbsp;&nbsp;&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Type of shed profile</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;Aerodynamic</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Applicable standard for shed profile</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;IEC 60815</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Creepage distance</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;mm</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;1600 &amp; 1050</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Specified tensile load</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kgf</td>\r\n<td style=\"width: 205px; height: 17px; text-align: center;\">&nbsp;11,000</td>\r\n<td style=\"width: 127px; height: 17px; text-align: center;\">&nbsp;7,000</td>\r\n<td style=\"width: 146.898px; height: 17px; text-align: center;\">&nbsp;7,000</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Specified cantilever load</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;Kgf.m</td>\r\n<td style=\"width: 205px; height: 17px; text-align: center;\">&nbsp;210</td>\r\n<td style=\"width: 127px; height: 17px; text-align: center;\">&nbsp;200</td>\r\n<td style=\"width: 146.898px; height: 17px; text-align: center;\">&nbsp;200</td>\r\n</tr>\r\n<tr style=\"height: 46px;\">\r\n<td style=\"width: 251px; height: 46px;\" colspan=\"5\"><span style=\"font-size: 12pt;\"><strong>Electrical Characteristics:</strong></span>&nbsp;&nbsp;&nbsp;&nbsp;</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Nominal system voltage</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;25</td>\r\n</tr>\r\n<tr style=\"height: 6px;\">\r\n<td style=\"width: 251px; height: 6px;\">\r\n<p>Wet power frequency withstands voltage (Horizontal Position)</p>\r\n</td>\r\n<td style=\"width: 56px; height: 6px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 6px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;125</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">(Vertical Position)</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;100</td>\r\n</tr>\r\n<tr style=\"height: 2px;\">\r\n<td style=\"width: 251px; height: 2px;\">\r\n<p>Dry lighting impulse withstand voltage.</p>\r\n<p style=\"text-align: right;\">(Positive Polarity)</p>\r\n</td>\r\n<td style=\"width: 56px; height: 2px; text-align: center;\">&nbsp;kVp</td>\r\n<td style=\"width: 478.898px; height: 2px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;240</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px; text-align: right;\">(Negative Polarity)</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kVp</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;260</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 251px; height: 17px;\">Visible discharge test voltage</td>\r\n<td style=\"width: 56px; height: 17px; text-align: center;\">&nbsp;kV rms</td>\r\n<td style=\"width: 478.898px; height: 17px; text-align: center;\" colspan=\"3\">&nbsp;&nbsp;&nbsp;35</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'Railway Insulators | Railway Catenary (OHE) System - Raychem RPG', 'Railway Polymeric Insulator combines mechanical strength with excellent pollution performance. High tensile strength of the glass fibre combined with HV shedded profile, makes it a rugged and lightweight tension insulator for overhead line applications.', 1, 285, '2021-08-27 12:42:28', '2022-01-24 10:03:16'),
(286, 'Polymeric Surge Arrester & Disconnector', 'reliable-connections/railway-catenary-ohe-system/polymeric-surge-arrester-disconnector', 'PCA Polymeric surge arresters provides active over-voltage protection that contributes directly to improved reliability of the system, reduces outages and protects expensive terminal equipment. \r\n\r\nPCA silicone surge arresters are designed and tested to meet customer demands with reliability in offering optimum operational performance. \r\n\r\nProven moisture sealing technology \r\n\r\nNon-tracking insulating silicone materials \r\n\r\nFully integrated single piece and void free design \r\n\r\nSafe mode of failure \r\n\r\nThe PCA series of arresters are designed to perform in the toughest environmental conditions to meet and exceed the requirements of IEC60099-4. Our gapless zinc oxide polymeric arresters have been in service since 1986 and the PCA range builds on that experience.', 'XymraG12QPpJtR5t15HjDDetSM1Ddl.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-polymeric-surge-arrester-disconnector.pdf', 3, '', '<table class=\"col-12 table\" width=\"845\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\"><strong> Qualification&nbsp;Testing </strong> &nbsp;</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>Decades&nbsp;of&nbsp;experience in&nbsp;the field&nbsp;combined with expertise in&nbsp;design&nbsp;and&nbsp;development&nbsp;lead to&nbsp;creating PCA Series of&nbsp;surge arresters.&nbsp;The basic construction comprises&nbsp;of&nbsp;high energy&nbsp;ZnO&nbsp;varistor&nbsp;assembled&nbsp;within&nbsp;an&nbsp;open&nbsp;cage&nbsp;design. The&nbsp;series has been type tested as per&nbsp;IEC60099-4&nbsp;Standard.</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Insulation withstand&nbsp;test&nbsp;on arrester housing</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Residual voltage test</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Long duration current impulse withstand test</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Operating duty tests</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Short-circuit tests</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Internal partial discharge test</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Bending moment test (Cantilever)</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Moisture ingress test</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Weather Ageing&nbsp;test</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Power frequency voltage versus time characteristics on the arrester</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<table class=\"col-12 table\" width=\"669\">\r\n<thead>\r\n<tr>\r\n<th scope=\"col\">Parameter</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td>&nbsp;The silicone insulating material&nbsp;is&nbsp;optimized&nbsp;for arrester application&nbsp;and&nbsp;following additional testing&nbsp;performed&nbsp;for&nbsp;qualification of silicone.</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Tracking and&nbsp;erosion</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>UV testing</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Thermal endurance</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Dielectric testing</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Flammability testing</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td>\r\n<ul>\r\n<li>Long term water immersion testing</li>\r\n</ul>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table data-table=\"\" data-tablelook=\"480\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Generic technical data </strong></p>\r\n</th>\r\n<th data-celllook=\"0\">&nbsp;Unit</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>PCA Series Ur&nbsp;Rating&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>18 - 240 kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Rated discharge current (8/20)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10 kA&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Line discharge class 3 according to</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>IEC 60099-4&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Operating&nbsp;duty&nbsp;impulse&nbsp;withstand&nbsp;current&nbsp;(4/10&nbsp;&micro;s)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>100 kA&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Long duration current impulse (2400 &micro;s)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>640 A&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1&nbsp;second TOV (Uw/Ur)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1.15&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>High current short circuit: (pre-failing method) (Safe non-shattering failure mode)</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>65 kA&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Energy based on Ur&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>7.8 kJ/kV&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p><strong> Mechanical data:</strong></p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Cantilever (Nm)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>2500 Nm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Tension (N)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>75&nbsp;kN&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Torque (Nm)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>75 Nm&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'Polymeric Surge Arrester Disconnector | Railway Catenary (OHE) System - Raychem RPG', 'PCA Polymeric surge arresters provides active over-voltage protection that contributes directly to improved reliability of the system, reduces outages and protects expensive terminal equipment.', 1, 286, '2021-08-27 12:43:13', '2022-01-06 06:34:04');
INSERT INTO `products` (`id`, `product_name`, `product_url_slug`, `product_description`, `product_thumbnail`, `product_block_label_id`, `product_code`, `product_3d_gallery`, `product_3d_gallery_image`, `product_support_email_id`, `product_catalog`, `product_specification_template_id`, `product_specification_template_two_image`, `product_specification_template_three_content`, `product_specification_template_four_button_one_name`, `product_specification_template_four_button_one_attachment`, `product_specification_template_four_button_two_name`, `product_specification_template_four_button_two_attachment`, `product_specification_template_five_content`, `product_technical_info`, `product_technical_button_name`, `product_technical_button_attachment`, `product_brand_id`, `product_category_id`, `product_related_service_id`, `product_featured_homepage`, `product_view_count`, `meta_title`, `meta_description`, `display_status`, `sorting_order`, `created_at`, `updated_at`) VALUES
(287, 'Railway Connectors (OHE fittings)', 'reliable-connections/railway-catenary-ohe-system/railway-connectors-ohe-fittings', 'Offer overhead connectors like Branch Connectors, T-Connectors, Bi-metallic Lugs, Bimetallic Sleeves, PG Clamps and Droppers as per NFC Standard. Different types of Compression/Bolted type Connectors and Droppers. They are extensively used by SNCF (French Railway) in France, DMRC and other countries.', 'PoXJRsNsbf81y2tfnm1XBgNe0r2GvY.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-reliable-connections-railway-catenary-ohe-system-railway-connectors-ohe-fittings.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Si. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Railway Catenary Products </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Reference Standard </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Application </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Branch Connector&nbsp;(DPH&nbsp;7)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Crimped connector to make mechanical and electrical&nbsp;branch between one end of bare copper conductor to&nbsp;intermediate point on a main bare copper conductor&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Branch Tee &amp; Half Clamp&nbsp;(FC tee / FC half clamp)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Branch&nbsp;(mechanical &amp;&nbsp;electrical)&nbsp;connection between copper conductor and&nbsp;contact wire.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Suspension Assembly&nbsp;for anti-swinging arm&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Mechanical&nbsp;connection between cantilever and&nbsp;anti-swinging arm&nbsp;to keep fixed distance&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Branch Tee&nbsp;(RAC T7)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Connection&nbsp;between copper catenary conductor&nbsp;and bare&nbsp;copper rod&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>P G Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC/IS&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Connection between two parallel conductors&nbsp;</p>\r\n<p>Aluminium Clamps / Copper Clamps / Bimetallic Clamps&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Crimped Sleeve&nbsp;(J&hellip; U-P / N)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Sleeve to join two copper conductors of equal section&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>7&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Crimped Bimetallic Sleeve&nbsp;(XGX)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Sleeve to join copper conductor&nbsp;to aluminium conductors&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>8&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bimetallic Lug&nbsp;(XDX)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Connection between aluminium conductor to copper palm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>9&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Current&nbsp;carrying catenary Dropper&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Dropper provides mechanical connection between messenger and contact wires. It distributes&nbsp;current along the catenary to avoid additional connection to supply power&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"4369\">\r\n<p><strong> SL. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Description </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Unit </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"4369\">\r\n<p><strong> Value Guaranteed by the Bidder </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 1. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p><strong>Voltage Class&nbsp;</strong></p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>kV&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>1.5&nbsp;kV&nbsp;DC / 25 kV AC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 2. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p><strong>Reference standards&nbsp;</strong></p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>NFC&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 3. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p><strong> Branch Connector (DPH 7) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 4. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Branch Tee &amp; Half Clamp (FC tee / FC half clamp) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Bolted &amp; Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 5. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Suspension Assy. for anti-swinging arm </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Cable Length&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Any cable length between 200 to 1700 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>End Lugs: Stainless Steel&nbsp;</p>\r\n<p>Binding cable: Stainless Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>c) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Breaking load&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>N</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>10000 (Min.)</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 6. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p><strong> Branch Tee (RAC T7) </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">&nbsp;</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Bolted &amp; Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 7. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> P G Clamp </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Bolted Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Aluminium / Copper / Bimetallic (Al/Cu)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 8. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Crimped Sleeve (J&hellip; U-P / N) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Aluminium / Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 9. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Crimped Bimetallic Sleeve (XGX) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Aluminium and Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 10. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Bimetallic Lug (XDX) </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Type of Clamps&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Crimp Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Aluminium and Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 11. </strong> &nbsp;</p>\r\n</td>\r\n<td colspan=\"3\" data-celllook=\"4369\">\r\n<p><strong> Current&nbsp;carrying&nbsp;Catenary Dropper </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>a) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Cable&nbsp;length&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Any cable length between 277 to 2077 mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>b) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Material of Clamp&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Dropper Clamps: Cupro-aluminium&nbsp;</p>\r\n<p>Wire: Copper&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>c)</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Patent&nbsp;reference</p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>WO 96/01747</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p>d) &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p>Breaking load&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>N&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"69905\">\r\n<p>6000 (Min.)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"69905\">\r\n<p><strong> 12. </strong> &nbsp;</p>\r\n</td>\r\n<td data-celllook=\"4369\">\r\n<p><strong>Packing details&nbsp;</strong></p>\r\n</td>\r\n<td data-celllook=\"69905\">&nbsp;</td>\r\n<td data-celllook=\"69905\">\r\n<p>Standard&nbsp;Wooden Box Packing&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', 6, 88, NULL, 0, NULL, 'Railway Connectors Ohe Fittings | Railway Catenary (OHE) System - Raychem RPG', 'Offer overhead connectors like Branch Connectors, T-Connectors, Bi-metallic Lugs, Bimetallic Sleeves, PG Clamps and Droppers as per NFC Standard.', 1, 287, '2021-08-27 12:43:36', '2022-01-06 09:49:43'),
(288, 'Low Voltage Aerial Bunched Cable (LV ABC) Accessories', 'theft-loss-reduction/low-voltage-aerial-bunched-cable-abc-accessories', 'Accessories include Suspension Clamp, Anchoring/Tension Clamp, Eye Hooks, Insulation Piercing Connector (IPC), Mounting Brackets, Mid Span Joint (MJPT), Bi-metallic Lug (CPTAU), End Caps, and SS Straps and Buckles.  Low Voltage ABC Accessories for bare and insulated applications for different cable sizes as per REC and NFC Standards.  \r\nThe different LV ABC Accessories are suitable for all three types of technologies - Bundled Cables with Bare Neutral Messenger, Insulated Neutral Messenger and Self-supporting Conductors and confirming to REC specifications and NFC standards. They are type tested as per NFC Standard and approved by Utilities all over India.', 'p9yClsY6JCcOvDZthQwwvx7hJgKbs6.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-theft-loss-reduction-low-voltage-aerial-bunched-cable-abc-accessories.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> S. No. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> LV ABC Accessories </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Reference Standard </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Application </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>Anchoring / Tension Clamp&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>REC / NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bare Neutral Messenger: &nbsp;</p>\r\n<p>Bolted Type, Clamp/Keeper made of&nbsp;aluminium,&nbsp;&nbsp;</p>\r\n<p>U-Bolts, Nuts &amp; Washers&nbsp;are galvanized.&nbsp;&nbsp;</p>\r\n<p>Range: 16 to 210 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulated Neutral Messenger: &nbsp;</p>\r\n<p>Clamp body made of corrosion resistant&nbsp;al. alloy&nbsp;Wedges made of&nbsp;polymer&nbsp;&nbsp;</p>\r\n<p>Bail&nbsp;made&nbsp;of&nbsp;stainless&nbsp;steel&nbsp;</p>\r\n<p>Range:&nbsp;25 to 120 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Self-Supporting Conductor:&nbsp;</p>\r\n<p>Accommodates&nbsp;2 to 4&nbsp;insulated cables of self-supporting system&nbsp;</p>\r\n<p>Clamp&nbsp;made with&nbsp;Galvanized Steel&nbsp;&nbsp;</p>\r\n<p>Arms/bail and Wedges made of&nbsp;polymer&nbsp;&nbsp;</p>\r\n<p>Ranges: 2 cores: 4 to 95 sq. mm&nbsp;</p>\r\n<p>4 cores:&nbsp;25 to 95 sq.mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Service&nbsp;Clamp&nbsp;with&nbsp;Bracket&nbsp;</p>\r\n<p>Accommodates&nbsp;2 to 4&nbsp;insulated&nbsp;service lines&nbsp;</p>\r\n<p>Ranges: 2 cores:&nbsp;16&nbsp;to&nbsp;25 sq. mm&nbsp;</p>\r\n<p>4 cores:&nbsp;16&nbsp;to&nbsp;25 sq.mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>Suspension Clamp&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>REC / NFC&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Bare Neutral Messenger: &nbsp;</p>\r\n<p>Bolted Type, Clamp/keeper made of&nbsp;aluminium&nbsp;&nbsp;</p>\r\n<p>U-Bolts, Nuts &amp; Washers&nbsp;are&nbsp;galvanized&nbsp;</p>\r\n<p>Range:&nbsp;16 to 210 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulated Neutral Messenger: &nbsp;</p>\r\n<p>Clamp/Link made of&nbsp;polymer&nbsp;&nbsp;</p>\r\n<p>Range:&nbsp;25&nbsp;to 120 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Self-Supporting Conductor: &nbsp;</p>\r\n<p>Accommodates&nbsp;2 to 4&nbsp;insulated cables of self-supporting system&nbsp;</p>\r\n<p>Clamp&nbsp;made with galvanized&nbsp;steel&nbsp;support&nbsp;and&nbsp;anti UV black resistant thermoplastic insert to grip&nbsp;2 or 4 conductors&nbsp;</p>\r\n<p>Ranges:&nbsp;2 cores:&nbsp;50&nbsp;to 95 sq. mm&nbsp;</p>\r\n<p>4 cores:&nbsp;35 to&nbsp;120&nbsp;sq.mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-Insulated Sleeves/Joints (MJPT)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;33-021&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Joining&nbsp;(Pre-insulated)&nbsp;of&nbsp;two&nbsp;LV ABC&nbsp;Cables&nbsp;</p>\r\n<p>Range:&nbsp;16 to 150 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Pre-Insulated Lugs (CPTAU)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC&nbsp;33-021&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Connection&nbsp;(Pre-insulated)&nbsp;between&nbsp;LV ABC&nbsp;Cable&nbsp;and&nbsp;Transformer&nbsp;or End Connection&nbsp;</p>\r\n<p>Range:&nbsp;16 to 150 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>Insulation Piercing Connector (IPC)&nbsp;for LV ABC&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"4\" data-celllook=\"0\">\r\n<p>NFC&nbsp;/ EN&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Insulated&nbsp;Main to&nbsp;Insulated&nbsp;Main&nbsp;(Upto&nbsp;150Sq.mm) &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulated&nbsp;Main&nbsp;to&nbsp;Insulated&nbsp;Tap&nbsp;(Upto&nbsp;120Sq.mm)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Insulated&nbsp;Tap to&nbsp;Insulated&nbsp;Service&nbsp;Connection&nbsp;(Upto&nbsp;16Sq.mm)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Bare to&nbsp;Insulated&nbsp;Main/Tap&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Insulation Piercing Connector (IPC) for Covered Conductor&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>NFC /&nbsp;EN&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Insulated Main to Insulated Main&nbsp;</p>\r\n<p>Upto&nbsp;33kV,&nbsp;240Sq.mm&nbsp;&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>7</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>End Cap&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">&nbsp;</td>\r\n<td data-celllook=\"0\">\r\n<p>Thermoplastic End Cap suitable for 16 to 150 sq. mm.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>8</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>Eye Hooks, Pole Clamps &amp; Brackets&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">&nbsp;</td>\r\n<td data-celllook=\"0\">\r\n<p>Eye Hook: Flat Type and Bolted Type (HDG)&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Pole Clamp: Galvanized Steel Circular &amp; Rectangular Pole Clamps</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>Bracket: Universal fixing Brackets&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>9</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Stainless Steel Strap&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">&nbsp;</td>\r\n<td data-celllook=\"0\">\r\n<p>Stainless Steel Strap, Buckles SS Straps &amp; Buckles used to fixing Brackets</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr style=\"height: 44px;\">\r\n<th style=\"height: 44px;\" data-celllook=\"4369\">\r\n<p><strong> SL. No. </strong></p>\r\n</th>\r\n<th style=\"height: 44px;\" data-celllook=\"4369\">\r\n<p><strong> Description </strong></p>\r\n</th>\r\n<th style=\"height: 44px;\" data-celllook=\"4369\">\r\n<p><strong> Value Guaranteed by the Bidder </strong></p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr style=\"height: 61px;\">\r\n<td style=\"height: 61px;\" data-celllook=\"69905\">\r\n<p><strong> 1. </strong></p>\r\n</td>\r\n<td style=\"height: 61px;\" data-celllook=\"4369\">\r\n<p>Suitability (Type of LV ABC)</p>\r\n</td>\r\n<td style=\"height: 61px;\" data-celllook=\"69905\">\r\n<p>Bundled Cable with a Bare Neutral Messenger /Bundled Cable with an Insulated Neutral Messenger / Bundled Cable with 4 Self-supporting Conductors</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 44px;\">\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p><strong> 2. </strong></p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Reference standards</p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>REC Specification / NFC Standard</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 44px;\">\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p><strong> 3. </strong></p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Products offered</p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Anchoring/Tension Clamp</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 44px;\">\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p><strong> 4. </strong></p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Reference standards</p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Suspension Clamp</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 44px;\">\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p><strong> 5. </strong></p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Products offered</p>\r\n</td>\r\n<td style=\"height: 44px;\" data-celllook=\"69905\">\r\n<p>Pre-Insulated Sleeves/Joints (MJPT)</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 30.375px;\">\r\n<td style=\"height: 30.375px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 30.375px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 30.375px;\" data-celllook=\"69905\">\r\n<p>Pre-Insulated Lugs (CPTAU)</p>\r\n</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">Insulation Piercing Connector (IPC)</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">End Cap</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">Eye Hooks, Pole Clamps &amp; Brackets</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">&nbsp;</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">Stainless Strap</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"height: 17px;\" data-celllook=\"69905\"><strong> 6. </strong></td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">Packing details</td>\r\n<td style=\"height: 17px;\" data-celllook=\"69905\">StandardWooden Box Packing</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 105, NULL, 0, NULL, 'Low Voltage Aerial Bunched Cable (ABC) Accessories - Raychem RPG', 'Low Voltage ABC Accessories for bare and insulated applications for different cable sizes as per REC and NFC Standards.', 1, 288, '2021-08-27 12:51:19', '2021-12-26 16:21:42'),
(289, 'Low Loss Boltless C-Wedge Connectors', 'theft-loss-reduction/low-loss-boltless-c-wedge-connectors', 'Boltless low power loss C-Wedge Type Connectors used in Distribution and High Voltage Networks. AMPACT C-Wedge type Boltless Connectors used for same or different conductor combination or on solid rod equipment terminal connections. Consisting of 2 parts, C-Body and Wedge, it prevents degradation and achieves significantly lower resistance. Thermal cycling causes conductors to expand and contract, but the Connector C-Body spring effect maintains constant contact pressure.  It is light in weight and easy to install with power-actuated tools.', 'wQrfdJP4aYwh8gUDvdIlKIsaLBELOC.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-theft-loss-reduction-low-loss-c-wedge-connectors.pdf', 3, '', '<table class=\"col-12 table\" data-table=\"\" data-tablelook=\"1184\">\r\n<thead>\r\n<tr>\r\n<th colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Sr.No. </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Co</strong><strong>nnector </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p><strong> Network </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"4\" data-celllook=\"0\">\r\n<p><strong> Conductor Range&nbsp;(mm) </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Main Conductor </strong> &nbsp;</p>\r\n</th>\r\n<th colspan=\"2\" data-celllook=\"0\">\r\n<p><strong> Tap Conductor </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n<tr>\r\n<th data-celllook=\"0\">\r\n<p><strong> Min. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Max. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Min. </strong> &nbsp;</p>\r\n</th>\r\n<th data-celllook=\"0\">\r\n<p><strong> Max. </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>1&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>AMPACT Universal Distribution Connector (UDC)&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Distribution&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>3.17&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>14.6&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>1.74&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>10.11&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>AMPACT Mini Wedge Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Distribution / Sub-station&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>9.25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>19.05&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>6.53&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>18.69&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>3&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>AMPACT Wedge Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Distribution / Sub-station / Transmission&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>9.25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>38.2&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>9.25&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>36.2&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>4&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>AMPACT Paddle&nbsp;</p>\r\n</td>\r\n<td colspan=\"1\" rowspan=\"3\" data-celllook=\"0\">\r\n<p>Sub-station&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"0\">\r\n<p>2/4&nbsp;Hole Paddle&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"4\" data-celllook=\"0\">\r\n<p>610/895/1400&nbsp;Amp&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td colspan=\"4\" data-celllook=\"0\">\r\n<p>Shank&nbsp;Dia&nbsp;&ndash;&nbsp;12/18/28&nbsp;mm&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td data-celllook=\"0\">\r\n<p>5&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Palm Connector&nbsp;</p>\r\n</td>\r\n<td data-celllook=\"0\">\r\n<p>Sub-station&nbsp;</p>\r\n</td>\r\n<td colspan=\"4\" data-celllook=\"0\">\r\n<p>Palm Connector D50/D40/D38/D30/D22&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"width: 918px;\" data-table=\"\" data-tablelook=\"0\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 64px;\" data-celllook=\"4369\">\r\n<p><strong> SL. No. </strong> &nbsp;</p>\r\n</th>\r\n<th style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p><strong> Description </strong> &nbsp;</p>\r\n</th>\r\n<th style=\"width: 421.25px;\" data-celllook=\"4369\">\r\n<p><strong> Value Guaranteed by the Bidder </strong> &nbsp;</p>\r\n</th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 1. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"69905\">\r\n<p>Reference standards&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>IS 5561 and ANSI 119.4&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 2. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 831px;\" colspan=\"2\" data-celllook=\"69905\">\r\n<p><strong> AMPACT&nbsp;Universal Distribution Connector (UDC): </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of&nbsp;C-Body&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Tin plated Copper Alloy&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> b)&nbsp; </strong></p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of wedge&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Tin plated Copper Alloy</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> c) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Hardware&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Not Applicable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> d) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Installation Tool&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Parallel Jaw&nbsp;Piller&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> e) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Corrosion Resistance&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Pre coated with Corrosion Inhibitor Compound&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 3. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 831px;\" colspan=\"2\" data-celllook=\"4369\">\r\n<p><strong> AMPACT&nbsp;Mini Wedge Connector/Wedge Connector: </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of C-Body&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Alu. Alloy&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> b)&nbsp; </strong></p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of Wedge</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Alu. Alloy</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> c) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Hardware&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Not Applicable&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> d) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Installation &amp; Application Tooling&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Light weight power actuated tool&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> e) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Non-Metallic Material of Connector&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Anti-Corrosion Inhibitor (Pre applied by the factory) contain metallic abrasive grit.&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 4. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 831px;\" colspan=\"2\" data-celllook=\"4369\">\r\n<p><strong> Palm Connector: </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Type of Palm Connector&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Bolted Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> b) </strong></p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of Palm Connector</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Brass 60/40</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> c) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Hardware&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Hot Dip Galvanized Steel&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 5. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 831px;\" colspan=\"2\" data-celllook=\"4369\">\r\n<p><strong> Paddle: </strong> &nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> a) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Type of Paddle&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Bolted Type&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> b) </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Material of Paddle&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Alu. Alloy&nbsp;</p>\r\n</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 64px;\" data-celllook=\"69905\">\r\n<p><strong> 6. </strong> &nbsp;</p>\r\n</td>\r\n<td style=\"width: 409.75px;\" data-celllook=\"4369\">\r\n<p>Packing details&nbsp;</p>\r\n</td>\r\n<td style=\"width: 421.25px;\" data-celllook=\"69905\">\r\n<p>Standard&nbsp;Wooden Box Packing&nbsp;</p>\r\n</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, 105, NULL, 0, NULL, 'Low Loss C Wedge Connectors | Theft Loss Reduction - Raychem RPG', 'Thermal cycling causes conductors to expand and contract, but the Connector C-Body spring effect maintains constant contact pressure. It is light in weight and easy to install with power-actuated tools.', 1, 289, '2021-08-27 12:51:58', '2021-12-27 06:29:33'),
(290, 'Covered Conductors', 'theft-loss-reduction/covered-conductors', 'Improves reliability of power distribution & transmission lines and loss reduction in power utilities. Covered conductors are longitudinally water blocked and covered with special grade material that provides insulation and ultra violet protection. They provide safety against accidental contacts and reduce outages significantly.', 'vaDPUXYShVmIvVxtjtIFD1hCuG5GyE.jpg', 2, NULL, NULL, '', 'epd@raychemrpg.com', 'product-catalog-theft-loss-reduction-covered-conductors.pdf', 3, '', '<p><img src=\"/assets/images/editor/covered-connectors-image-2.jpg\" width=\"558\" height=\"430\" /></p>\r\n<table class=\"col-12 table\" style=\"height: 132px;\" width=\"878\">\r\n<thead>\r\n<tr>\r\n<th style=\"width: 868px;\" scope=\"col\"><strong>BENEFITS WITH COVERED CONDUCTORS</strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr>\r\n<td style=\"width: 868px;\">Protects the aluminum conductor from corrosion</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Reducing faults caused by tree contacts and enhance the reliability</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Reducing animal foults</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Upgrade the voltage/current without changing the phase distance</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Preventing bush fires</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Lower life cycle cost compared with bare conductor</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Reducing maintenance cost of tree trimming</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Reducing clearance between phases, can cope with direct contact between phases</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Less risk of sabotage</td>\r\n</tr>\r\n<tr>\r\n<td style=\"width: 868px;\">Environmental advantages</td>\r\n</tr>\r\n</tbody>\r\n</table>', NULL, '', NULL, '', NULL, '<table class=\"col-12 table\" style=\"height: 206px; width: 1014px;\">\r\n<thead>\r\n<tr style=\"height: 20px;\">\r\n<th style=\"width: 98px; height: 20px;\" scope=\"col\"><strong><span data-contrast=\"none\">Sr.&nbsp;No</span></strong></th>\r\n<th style=\"width: 213px; height: 20px;\" scope=\"col\"><strong><span data-contrast=\"none\">Description/Designation</span></strong></th>\r\n<th style=\"width: 354px; height: 20px;\" colspan=\"5\" scope=\"col\"><strong><span data-contrast=\"none\">&nbsp; &nbsp; &nbsp; &nbsp;Rating Available</span></strong></th>\r\n<th style=\"width: 152px; height: 20px;\" colspan=\"2\" scope=\"col\"><strong><span data-contrast=\"none\">&nbsp; &nbsp; &nbsp;Type</span></strong><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:2,&quot;335551620&quot;:2,&quot;335559740&quot;:240}\">&nbsp;</span></th>\r\n<th style=\"width: 125px; height: 20px;\" scope=\"col\"><strong><span data-contrast=\"none\">Area in&nbsp;Sq&nbsp;mm</span></strong></th>\r\n</tr>\r\n</thead>\r\n<tbody>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">11kV</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">33kV</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">66kV</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">110kV</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">132kV</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">AAAC</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">ACSR</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">&nbsp;</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">1</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\"><span data-contrast=\"none\">CCSX 50</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:2,&quot;335551620&quot;:2,&quot;335559740&quot;:240}\">&nbsp;</span></td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\"><span data-contrast=\"none\">50</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:2,&quot;335551620&quot;:2,&quot;335559740&quot;:240}\">&nbsp;</span></td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">2</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\"><span data-contrast=\"none\">CCSX 70</span><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335551550&quot;:2,&quot;335551620&quot;:2,&quot;335559740&quot;:240}\">&nbsp;</span></td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">&nbsp;</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">70</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">3</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\">CCSX 99</td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">99</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">4</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\">CCSX 120</td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">120</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">5</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\">CCSX 157</td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">157</td>\r\n</tr>\r\n<tr style=\"height: 17px;\">\r\n<td style=\"width: 98px; height: 17px; text-align: center;\">6</td>\r\n<td style=\"width: 213px; height: 17px; text-align: center;\">CCSX 241</td>\r\n<td style=\"width: 102.156px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 70.8438px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 57px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 62px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 87px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 65px; height: 17px; text-align: center;\">Yes</td>\r\n<td style=\"width: 125px; height: 17px; text-align: center;\">241</td>\r\n</tr>\r\n</tbody>\r\n</table>\r\n<p><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559737&quot;:662,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>\r\n<p><span data-ccp-props=\"{&quot;201341983&quot;:0,&quot;335559737&quot;:662,&quot;335559739&quot;:160,&quot;335559740&quot;:259}\">&nbsp;</span></p>', NULL, '', 6, 105, NULL, 0, NULL, 'Covered Conductors | Theft Loss Reduction - Raychem RPG', 'Improves reliability of power transmission lines and loss reduction in power utilities. Covered conductors are longitudinal and covered with special grade material that provides insulation and ultra violet protection.', 1, 290, '2021-08-27 12:52:33', '2021-12-24 12:42:38');
