DISTRIBUTION TRANSFORMERS: Supply, Installation, testing and commissioning of Cast Rasin Dry Type Transformer 1600 KVA 11/0.433 KV, 3 Phase, 50 Hz, Dyn 11 vector group, copper wound, class F insulation associated with On Load Tap Changer (OLTC) plus AVR and RTCC Panel for automatic sensing of incoming voltage, automatic operation of OLTC and facility for remote manual operation of On Load Tap Changer, winding temperature indicator/ controller actuated by means of resistance temperature detector embedded in LV windings, indoor type Transformer with  impedance as per latest ECBC norms, tapping for off load operation on HV side in steps of  +5% to - 15% in steps of 1.25% 17 steps to give a constant secondary voltage, having cable end boxes on HV side suitable for 3 x 300 sqmm XLPE cable of 11 KV grade and bus trunking as required  on LV side with neutral brought out separately including supplying and laying of copper conductor multicore control cables  for safety tripping, suitably mounted on M.S. Channel i/c supplying and grouting of suitable M.S. Channel with all accessories and conforming to IS 11171:1985, IEC 60726, ANSI, NEMA standards  & as per specification complete in all respects as required at site.
 
QUANTITY :- 1