Material Description	UOM	QTY
METAL OXIDE GAPLES LA 9KV,10KAP (METAL OXIDE GAPLESS LA, CGL MAKE, MODEL ZPL2, SYSTEM VOLTAGE 11KV, MOCV 7.5KV,NDC 10KA, STATION CLASS -III, POLYMER TYPE.                                        VENDOR SHOULD BE AUTHORISED SUPPLIER OF CGL MAKE LA AND TEST CERTIFICATES TO BE FURNISHED ALONG WITH MATERIAL.)	NO	4.00
METAL OXIDE GAPLES LA 9KV,10KAP (Metal oxide gapless, heavy duty, Gapless LA, MODEL : ASN03WO009
SHREEM MAKE.
Applicable Standard : IEC-60099-4
Rated Voltage KV (rms) : 9KV (rms)
Rated Frequency (Hz) : 50Hz
Nominal Discharge current (8X20 micro : 10KAP Second wave) (rms.
Maximum Continuous operating voltage : 7.65 KV rms)

Insulation withstand voltage
a) Dry power frequency : 28 KV
b) Wet power frequency : 28 KV
c) Impulse (1.2 X 50 micro second) : 95 KVP

Lightning Impulse residual voltage
(8/20 micro second wave)
a) 5000 A : 27 KVP
b) 10000 A : 30 KVP
c) 20000 A : 35 KVP

Steep current impulse Residual Voltage : 36 KVP at 10KA of 1 micro second front time.
Switching Impulse Residual Voltage : 24 KVP (50 X 100 microsecond)
Current withstand capability
a) Long duration discharge class : III
b) Minimum energy discharge capability : AS PER IEC 60099-4
Protective ratio : 2.1
High Current Impulse withstand value : 100 KA ( 4 X 10 microsecond)
As per attached GA and Technical Specifications with all test reports.


)	NO	6.00