Transformer: 1250 kVA, Oil Filled Pad Mount Transformer
Primary: 11KV, 3 Phase, Delta Configuration
Secondary: 415Y/240 Volts, 50 Hz, 3 Phase, 4-Wire
HV BIL: 95 KV
LV BIL: 30 KV
Connection Configuration: DY11
Tap Changing: 5 No on H.V Side for off load tap changing +5%, +2.5%, 0%,-2.5%, -5%
Radial Feed
11Kv Terminations:- 3 No. Bushing Well / Inserts to be included
Protection:- HV Fuse under oil
Standard :- IEEE C57.12.34
The Transformer should have 11Kv Bushing wells and bushing inserts accepting 200 A load break elbows