<table class="col-12 table" data-table="" data-tablelook="1184">
<thead>
<tr>
<th colspan="4" data-celllook="0">
<p><strong> Single Piece Joint 72/145 kV/245 kV </strong></p>
</th>
</tr>
</thead>
<tbody>
<tr>
<td data-celllook="0">
<p>Rated&nbsp;kV&nbsp;</p>
</td>
<td data-celllook="0">
<p>36/66 (72)&nbsp;</p>
</td>
<td data-celllook="0">
<p>76/132 (145)&nbsp;</p>
</td>
<td data-celllook="0">
<p>127/220 (245)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Diameter over insulation&nbsp;</p>
</td>
<td data-celllook="0">
<p>37.86 - 75.20 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>37.86-96.80 mm&nbsp;&nbsp;</p>
</td>
<td data-celllook="0">
<p>60.70-128.25 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Diameter over sheath&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le; 120 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le; 140 mm&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le; 160 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Cable screen types&nbsp;</p>
</td>
<td data-celllook="0">
<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Corrugated&nbsp;aluminium&nbsp;sheath/Lead sheath/Cu wire. etc.&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Max. Cross section (Cu / Al)&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le; 1200 mm&sup2;&nbsp;</p>
</td>
<td data-celllook="0">
<p>Approx. 1600 mm&sup2;&nbsp;</p>
</td>
<td data-celllook="0">
<p>&le; 2500 mm&sup2;&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Conductor connection&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear head bolts)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear head bolts)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear head bolts)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material of connection bolt&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum / Copper&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum / Copper&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminum / Copper&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Max. permissible dielectric stress&nbsp;</p>
</td>
<td data-celllook="0">
<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>
</td>
<td data-celllook="0">
<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>
</td>
<td data-celllook="0">
<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Outer protection&nbsp;</p>
</td>
<td data-celllook="0">
<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>
</td>
<td data-celllook="0">
<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>
</td>
<td data-celllook="0">
<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Method of stress control&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material main body&nbsp;</p>
</td>
<td data-celllook="0">
<p>Silicone rubber&nbsp;</p>
</td>
<td data-celllook="0">
<p>Silicone rubber&nbsp;</p>
</td>
<td data-celllook="0">
<p>Silicone rubber&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Installation temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Operation temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>-55 &deg;C - +50 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>-55 &deg;C - +50 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>-55 &deg;C - +50 &deg;C&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Storage temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
</tr>
</tbody>
</table>
<table class="col-12 table" data-table="" data-tablelook="1184">
<thead>
<tr>
<th colspan="2" data-celllook="0">
<p><strong> Three-Piece 145 kV Joint&nbsp; </strong> &nbsp;</p>
</th>
</tr>
</thead>
<tbody>
<tr>
<td data-celllook="0">
<p>Diameter over insulation&nbsp;</p>
</td>
<td data-celllook="0">
<p>43 &ndash; 84 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Diameter over sheath&nbsp;</p>
</td>
<td data-celllook="0">
<p>105 mm&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Cable screen types&nbsp;</p>
</td>
<td data-celllook="0">
<p>Cu-wires w/o laminated foil, lead sheath, corrugated metal sheath, Cu-tape (other types and combinations on request)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Max. Cross section (Cu / Al)&nbsp;</p>
</td>
<td data-celllook="0">
<p>Approx. 3000 mm&sup2;&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Conductor connection&nbsp;</p>
</td>
<td data-celllook="0">
<p>Mechanical (shear head bolts)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material of connection bolt&nbsp;</p>
</td>
<td data-celllook="0">
<p>Aluminium&nbsp;/ copper&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Max. permissible dielectric stress&nbsp;</p>
</td>
<td data-celllook="0">
<p>4 kV/mm (at insulation screen of cable)&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Outer protection&nbsp;</p>
</td>
<td data-celllook="0">
<p>Reinforced composite laminate wrap around with an integral moisture barrier/Copper Casing/FRP box with PU compound&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Method of stress control&nbsp;</p>
</td>
<td data-celllook="0">
<p>Geometric&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Material main body&nbsp;</p>
</td>
<td data-celllook="0">
<p>Silicone rubber&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Installation temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Operation temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>-55 &deg;C - +50 &deg;C&nbsp;</p>
</td>
</tr>
<tr>
<td data-celllook="0">
<p>Storage temperature&nbsp;</p>
</td>
<td data-celllook="0">
<p>0 &deg;C - +40 &deg;C&nbsp;</p>
</td>
</tr>
</tbody>
</table>